2021 PCSA a/c maintenance renewal Everything was clean and checked out well. System is operating normally at this time.
Complaint not cooling Cause of the issue was bad capacitor. Replaced capacitor and system is operating normally at this time.
REplaced condenser motor & contactor ck warrantys
Lobby furnace 3/4 hp blower mtr. 15 my cap. Attic.
No heat gas valve was not working, replaced gas valve. Upon firing up system found board not operating correctly, replaced board. Tested unit system is heating
Complaint: Server Room Freezing up No cool found blower not coming on, found bad relay, wired motor hot, checked charge RSP installed a head pressure control with no tee so canâ€™t check high pressure. Need to come back to change relay, head pressure control and a tee. Wired around head pressure control, charged to 15 degrees superheat. Returned and replaced high pressure switch with fan cycle control with a tee, replaced blower relay. Tested unit operating as it should
2019 Fall PCSA Check Up Renewed & Done 1/8/20 2020 Spring Check Up Pre Paid & Scheduled