System was 1 lb low on R-410A. Capacitor on outdoor coil was also very weak and needed replaced. Customer will be cleaning the outdoor coil in the near future. System is operating normally at this time.
Cause of the issue was dead compressor. System will not start. Recommend system replacement.
2022 Spring Check Up PCSA Renew 5/20/22 Cause of the issue was dead fan motor. Installed temporary motor until replacement motor arrives. 6/8/22 Replaced motor and performed check up. Everything else was clean and checked out well. System is operating normally at this time.
1x a/c check up. Found condenser fan motor was locked up. Replaced motor and verified operation. Unit is operating at this time. System is running without filters. I highly recommend adding filters to system. Blower motor on indoor unit is not running efficiently due to dust build up, caused by lack of filters. I recommend we take blower out and clean it. Cost will be 150$.
PCSA 2021 heating maintenance prepaid Everything was clean and checked out well. System is operating normally at this time.
2021 PCSA a/c maintenance renewal Everything was clean and checked out well. System is operating normally at this time.
Complaint not cooling Cause of the issue was bad capacitor. Replaced capacitor and system is operating normally at this time.
REplaced condenser motor & contactor ck warrantys
Lobby furnace 3/4 hp blower mtr. 15 my cap. Attic.
No heat gas valve was not working, replaced gas valve. Upon firing up system found board not operating correctly, replaced board. Tested unit system is heating
Complaint: Server Room Freezing up No cool found blower not coming on, found bad relay, wired motor hot, checked charge RSP installed a head pressure control with no tee so canâ€™t check high pressure. Need to come back to change relay, head pressure control and a tee. Wired around head pressure control, charged to 15 degrees superheat. Returned and replaced high pressure switch with fan cycle control with a tee, replaced blower relay. Tested unit operating as it should
2019 Fall PCSA Check Up Renewed & Done 1/8/20 2020 Spring Check Up Pre Paid & Scheduled