This company will have my business and recommendations because they truly care about their customers and do a great job! Thank you
Tested both heating and cooling system. Checked filter. Recorded voltages and temperatures. Tested motors. Tested ignitor. Cleaned flame sensor. Tested thermostat. Verified refrigerant charge. Replaced outdoor discharge thermistor. Tested capacitor and contactor.
Diagnosed defective discharge line temperature sensor. Bypassed switch to test system and recorded refrigerant pressures. Systems is operating properly. Amp draws recorded, tested run capacitor. Need to replaced switch under parts warranty.
Arrived on site to perform fall tune up on a 2013 Lennox system. Furnace and evaporator coil located in attic. Client stated no issues and was good cycled heating mode on and good. Filter was due for replacement but client stated itâ€™s okay and will leave it in. Recommend replacing to reduce dirt entering system and airflow restriction to creat stress wear on motor. Found new flex ducting used and good condition. Blower assembly good dust accumulating. Motor is good and amp drawls are in range. inducer motor is good and amp draws are in range. Coil is good. Heat exchanger is good. All safety switches are operational. Drain lines good slight debris accumulating Indicating dust and debris is entering system over time. Temperature rise is good and in range. Voltage of furnace at 122. No protection on high efficient system. Recommend adding surge protectors to prevent system from getting damaged from electrical surges and power outages that can damage or short out components or even s
Performed routine spring maintenance on Lennox in Huntington beach
Two system Carrier Ac maintenance in Huntington Beach.
Furnace maintenance in Huntington Beach
Performed routine spring maintenance on lennox unit in Huntington beach
Air conditioning maintenance in Huntington Beach
Gated community in Huntington beach routine check uo
Repairing Carrier air conditioners in the peninsula at Huntington Beach
Cleaning out two Carrier air conditioners in the peninsula at Huntington Beach for a nice family
Install germicidal UV light filtration system.