Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Technician Kurt is a great guy. He always does clean and professional plumbing work for us. Plus he answers all my questions with accurate and good humor.
On time. Works neatly. Professional and courteous.
Kurt did an excellent job. Efficient yet thorough. Would be happy to have him again.
Performed heat pump check up check electrical low and high ok both filters ok test humidifier and also test 20 kw back up heat ok check split ok both coils are clean indoors and outdoor, check outdoor unit pressures capacitor and contactor ok test defrost cycle heat pump ok
Performed 6 month quality check, found filter stuck. Found return elbow damaged and when attached to the furnace it was not squared. Removed front of ell, pulled square and opened slot for filter. Sealed duct and test fit filter, now filter fits but is snug because of the damaged ell. May need to replace if filter getting stuck in the future. Started heat pump, measured btu output. Started gas furnace, performed combustion test. Checked furnace setup. Checked operation and temperature rise.
Found pressure relief valve leaking, check boiler water pressure while boiler is running and pressure was at 30psi expansion tank is full of water, quoted to drain expansion tank and also price if customer want to replace relief valve, customer passed in relief valve he will call Office if continues to leak, after draining expansion tank check boiler operation and pressure/temperature and looks ok, 15 psi cycle and test boiler on limit ok emailed price to installed electric water heater
Performed Quality Assurance on Hybrid/Dual Fuel System. Reviewed all settings. Completed checklist Form in system. Installed a backplate for the Thermostat to cover the unpainted wall.
Performed precision heat tune up on 2 Armstrong oil furnaces. Both were very dirty. Both 16x25x1 air filters are clean. Checked all electrical conections. Replaced 2 .65x80b nozzles. Replace rf1 oil filter. Performed combustion test on both furnaces. Both furnaces were working fine at time of service. Chimney needs brushed out let homeowner know.
Performed propane gas heat tune up, check electrical low and high. Clean sensor and check burners ok check split ok, performed combustion test cycle furnace ok, test pump ok also replaced both air filters High efficiency filter and service humidifier replaced pad and test humidifier cycle system ok
Shut Supply Water Supply off to the Water Heater and turn off Gas Supply. Drain Water Heater down and Remove the Outlet Piping at the Water Heater. Remove the Anode Assembly. Install new Anode Assembly. Reconnect Outlet Piping to the Water Heater. Turn Water Supply on to the Water Heater to refill. Turn Gas Supply on and insure water heater relights and is leak free. 11/20/19 installed new anode rode cut to length and checked for leaks . Put water heater back in working order. Anode rod was very bad from water heater installed 11/21/17. Recommended to homeowner that a water softer system be installed to fix the hard water issue. Homeowner does not like the way a water softer makes the water feel.
Reclaimed and removed old attic system. Installed new Amana 2 stage communicating condenser on new pad and snow feet. Flushed lineset and purged with nitrogen. Brazed in with nitrogen. Installed new Amana high efficiency condensing gas furnace in new drain pan. Placed a new evaporator coil on top. Brazed in with nitrogen and installed adjustable txv. Pressure tested to 300 and evacuated to 160 microns. Raised whole supply ducting up and made a 11 inch piece to compensate. Reconnected condensate, venting, gas, and electrical. Tested gas for leaks. No leaks found. Installed ez trap and wet switch to prevent water damage. Installed April aire 213 upgrade kits in both systems. Installed Honeywell uv light system. Installed Honeywell Iaq system and red link wireless accessory. Tested system and performed combustion test. Adjusted refrigerant charge. Tested system. Everything working great at time of install.
Found several rooms without heat. Administration showed me the boiler they believed heated those rooms . Found thermostats calling but not pulling in contacter on triple aquastat. Tapped on aquastat contacter and circulator pump came on and sent heat to the rooms that did not have heat. Honeywell L8148a aquastat needs replaced, called distributer for price and availability. Will return once we receive part. Told administrator until this is replaced it will be intermittent. Went to remove old aquastat and weâ€™ll begin to leak. Got a new well ran out to job site and installed new well and new aquastat.
Performed two propane gas heater tune ups, check electrical low and high ok filters ok clean sensor and check burners, ok gas manifold pressure ok performed combustion test cycle both heaters ok, second floor system wet switch might be going bad, would open circuit when it get touched, informed customer about about situation
Performed heating maintenance, replaced media filter. Checked voltage, amperage and electrical connections. Serviced humidifier, cleaned and replaced water panel. Started gas furnace, measured fuel pressures and adjusted. Performed combustion test. Checked operation and temperature rise.
Had previously been onsite due to the system making a vibrating rubbing noise. Ordered replacement bearing and blower wheel assembly. Returned to site and disassembled the Indoor Unit to Access the Blower Wheel. Removed the Bearing Assembly and Blower Wheel. Installed a new Wheel and Bearing. Reassembled unit and put back in operation to test. Blower wheel is not balanced and is vibrating the unit. Blower Wheel is in proper position. If the Motor and shaft are slightly off position then this would be causing the imbalance in the blower wheel. This could have also been causing the previous bearings to wear and cause the noise from the unit. There is no access to Motor without disconnecting the refrigerant Coil from the unit. Need to follow up with Daikin to see if we can get a new Indoor Unit. Told Homeowner we will follow up with him next week.
Performed Heat pump check up with propane furnace back up, and also second floor attic propane furnace, check electrical low and high ok clean sensor and check burners ok check gas pressure combustion test ok replace filters, cycle both units ok service first floor humidifier set to winter 35% on heat pump check reversing valve ok, on second floor furnace found locked out pressure switch p, found intermittent problem with motor and control board, control board spark igniter is falling, and inducer was seized, got it to work for now, due to condition system should get replaced also would recommend upgrading filters to 2200 upgrade kits,
Performed two propane gas furnaces check ups, check electrical low and high ok replace both filters, clean sensors and check burners, manifold gas pressure ok, flushed furnace trap, blower caps ok second floor units checked out ok good readings combustion test and smoker test ok, on first floor unit found heat exchanger lot of rust and also did not passed Smoke test, informed customer about situation and gave them options,
Found that the primary control was off on a hard lockout. Reset control and found air in the oil line. Oil tank was replaced this summer plus oil pump has about 4 feet of lift , pump had lost its prime. After bleeding oil line started up oil burner a few times, furnace Did not fire constantly. Found that transformer was very weak, replace with transformer homeowner had previously purchased ( no warranty on part). Got furnace to fire but furnace is around 25 years old told homeowner donâ€™t know how long it will stay working really needs replaced, homeowner is not ready for this step at this time.