Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt did an excellent job. Efficient yet thorough. Would be happy to have him again.
They truly care that you are more than 100% Satisfied and do quality work! Companies like DiBaise are getting harder and harder to come by. They stand behind you and their work!
Nathan is highly competent, thorough, and honest. As long as he’s on our account, we’re a customer!
Nate always does a great job for us!
After talking to homeowner he said that randomly the a/c would kick on and the heat at the same time. Homeowner had a Nest thermostat, possibly the thermostat was causing the malfunction. Recommended we replace it with a Honeywell t4 thermostat. Replaced thermostat and checked r22 pressures they were 200/70 pretty good. Homeowner signed up for maintenance contract. Performed precision heat tune up on York oil furnace. Replaced 16x25x1 air filter. Replaced.65x70 b nozzle. Replaced rf1 oil filter. Checked temperature rise of oil furnace. Furnace is older but running fine at time of service.
Performed quality assurance evaluation on system. All work looked good. Customer very happy with installation.
Performed Quality Assurance On recently installed Daikin Mini Split System. Reviewed Installation and completed Checklist Form in System. Corrected any issues that were found.
Performed Quality Assurance On recently Installed Amana Gas Furnace/Heat Pump System. Corrected issues that needed to be addressed. Reviewed installation with Homeowner. Completed Checklist Form in System.
Performed Quality Assurance On Amana Heat Pump System. Completed Checklist Form in System. PECO # is recorded in the Notes. Reviewed installation with Homeowner. Need to follow up with Homeowners about the Oil Tank and possibly insulating the Plenum.
Performed ac check 6 month inspection washed filter check electrical low And high ok check split Ok check outdoor unit pressures ok capacitor and contactor ok cycle unit ok
Installed a new furnace on feet on existing plastic pad . Installed a new 3 ton coil on top of the furnace and modified duct work as need . Ran new condensate drain with an Ez trap and added a new pump . Drained over to sewer drain. Reconnected existing return duct and changed the filter 20â€x25â€x1â€ filter. Ran new copper lines to the outside 3 ton Ac unit . Ac is on heat pump feet on a new plastic pad. New disconnect box and sealtight on exsisting wire to indoor. Calked and sealed all penetration. Put in a new thermostat prestige iq with eim and outdoor sensor walked threw with customer .
Took out old ac coil and outdoor unit, also removed the old line set and comm. wires going to outdoor unit. Installed new indoor coil on top of existing oil furnace and did metal work to fit it properly. Installed new ez trap and condensate pump with discharge line going into the sewer line. Tested and works properly. Leveled out outdoor area and installed new pad for outdoor unit and ran new line sets and communication wires. Pressure tested lineset to 300, no leaks. Evacuated lineset to 266 microns. Tested all components and is all working as it should.
Replace blower bearing for living room ductless head, test and cycle operation ok
Put batteries in new daikin remote and cycled ductless in both heating and cooling mode, I placed remote on table below indoor unit.
Reclaimed and removed old equipment. Installed new pad, disconnect, lineset, whip, and heat pump on heat pump feet. Brazed in outdoor unit and reconnected electrical. Installed new return box, return duct, and new air handler. Reconnected supply and return ducting. Installed heat kit. Ran new wire for air handler and tied into panel and unit. Installed new ez trap and condensate pump to break r wire. Brazed in air handler and pressure tested to 300. No leaks found. Evacuated down to 145 microns. Removed old oil tank fill and vent lines and closed holes. Removed old oil supply line. Installed new receptacle for condensate pump. Capped old chimny pipe. Ran vinyl into discharge line. Tested system and adjusted charge. Delta t 21 degrees. System working properly at time of install.
Found bearing assembly making noise,, tried to lubricated sounds is lower but still making some sound, called supply house, they will send new assembly takes couple days to get it since they donâ€™t have it in stock, office will get back to customer when part has arrived to schedule repairs
Performed ac check up, oil furnace with ac unit, flushed drain test pump ok, check blower cap ok filter, ok split is only 15, return is 73 supply 57, check outdoor unit found low bare low voltage wires, contactor making buzzing sound, and unit is low in r22, blower wheel is really dirty needs cleaning, quoted for repairs due to condition and repairs recommend replacing system current units is from 1989 bill to come tomorrow around 5 pm for quote on new system
Performed two ac check ups, attic and basement units, check electrical low and high ok replace both filters, 16x24x1 and 20x20x1 flushed drain ok check split, replace blower cap for attic unit, check outdoor units r22 pressures capacitor and contactors ok cycle units ok
Performed precision ac tune up on 2 carrier acs. Filter sizes are both 16x25x4 homeowner to replace. Checked all electrical conections and components. Blew out both condensate drains. Checked refrigerant pressures and temperatures at indoor and outdoor units. Both systems working fine at time of service.