Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis came out and went beyond the minimum and did additional insulation and and reconfigurations of essential elements of the system. Thank You.
They did a great job troubleshooting for possible future problems
Routine check but all went well, as expected.
Great job. Personable and enthused professional.
Bryan was very professional and thorough.
Performed peco heat pump tune up. Replaced 16x25x1 air filter. Checked all electrical conections and components. Found condensation vinyl hose is ran to outside of home. Gave estimate to run vinyl hose to inside to prevent freezing. Also suggested getting a membership for discount on repairs and to perform heat tune up on gas furnace. Heat pump is 48,000 btuâ€™s. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of inspection.
Found weak capacitor. Replaced 15 mf capacitor. Also found dirty air filter. And a lot of junk in condensate tubing. Suggested we do a tune up on the gas furnace. Performed a precision heat tune up on trane gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of service.
Extended exhaust pipe all the way passed deck, and insulated also cutback intake, during same visit eliminated discharge line going outside and attached discharge line to drain inside the house, this will eliminate any potential from freezing during very cold times, test and cycle condensation pump and working ok
Performed gas propane furnace check up, check electrical low and high ok replace filter, check manifold gas pressures low and high ok, combustion test cycle furnace ok clean flame sensor, check venting and found exhaust vent is not insulated and terminates under the deck we need to extend exhaust all the way out and insulate , (2)45 three inch is needed and also foam insulation for 3 in pipe
Performed precision heat tune up on Lennox heat pump. Replaced 20x20x1 air filter. Checked all electrical conections and components. Serviced Aprilaire humidifier with #35 humidifier pad. Checked operation of emergency heat. Found humidistat reading 46% humidity. Put humidifier into test mode and humidifier ran fine. Explained to homeowner that as warm as a winter we have been having humidifier will not cycle as much due to less heating run cycles. Turned up humidistat to highest setting. Checked refrigerant pressures and defrost mode. Did hear compressor change in an audible sound while running, this is wear and tear with age of compressor. Let Neal know that the compressor could stop all together or it could run like this for a while. He is going to see how it goes at this point.
Injected a/c renew into Lennox heat pump, and checked refrigerant pressures. They were 205/47 r22 pressures. With a subcooling of 17.9 degrees. De energized And re- energized the reversing valve to work the ac/ renew thru the system. Heat pump is working fine at time of service.
Performed precision heat tune on Lennox gas furnace. Replaced 16x25x1 air filter. Checked gas pressure. Performed combustion test. Checked all electrical conections and components. Gas furnace is working fine at time of service.
Performed heat tune up, during visit customer informed heat would not come on during last weekend, found open igniter, replace igniter noticed control board always sending 120 volts to igniter during call for heat, thatâ€™s the cause why igniter went, quoted for new board and also upgraded to 120 volts igniter, customer ok with repair, installed new board and 120 igniter, clean sensor and check gas pressures ok combustion test cycle heater ok furnace running ok Now,
Performed precision heat tune up on Payne gas furnace. Homeowner to replace 14x14x1 air filter and 20x20x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Adjusted gas pressures and performed combustion test. Also found 2to3â€ reducer installed incorrectly, recommended changing fittings. Gas furnace is working fine at time of service. Found 2x3â€ reducer horizontally installed and is a water trap
Performed precision heat tune up on Lennox gas furnace. 16x25x1 air filter is clean. Blew out condensate drain. Checked all electrical conections and components. Checked gas pressure. Performed combustion test. Also cleaned flame sensor. Found thermostat is not working correctly and needs replaced, homeowner to replace at this time. Lennox gas furnace is working fine at time of service.
Water leak coming from ac indoor coil, inspect drain and flushed drain ok, no problem with drain, check filter ok check refrigerant pressures, customer had compressor replaced this summer and was converted to R438A refrigerant slightly different pressure differential, new compressor is rated at 45 degree coil temp, check super heat and subccoling 200/55 with 30 superheat and 11 subccoling calculated target superheat, target is 12 with outdoor temp and indoor wetbul temperature relation, system is low in refrigerant
Performed ac check up check electrical low and high ok check filter split ok, check outdoor unit r22 pressures contactor and capacitor ok sub cooling and super heat ok cycle unit ok
Found carrier ac slightly low on charge added 1 lb 10 oz of r 410a. Now have a subcooling of 14.6 unit called for 14 system has a slight leak. System is an 03. Told homeowner they need to start thinking about replacing,they are going to wait at this point. Also performed precision ac tune up on carrier ac. Replaced 20x22x1 air filter. Blew out condensate drain and cleaned pump. Checked all electrical conections and components.checked refrigerant pressures and temperatures at indoor and outdoor units.
Performed ac check up, check electrical low and high ok found blower cap reading 6 rated at 7.5 filter ok flushed drain noticed ac drain slope is not away from coil, primary pan is full of water, causing high humidity and potential for mold, recommend repairing drain line, by installing an ez trap, check outdoor unit 410 pressures ok capacitor and contactor ok cycle unit ok quoted to replace drain trap and correct problem with slope, customer ok with price customer does not want blower cap replace
Performed precision ac tune up on lennox ac. Found clean 16x25x1 air filter. Also found that thermostat switch on older Aprilaire thermostat is going bad and no always switching correctly, recommended replacing with Honeywell t4 programable thermostat. Homeowner is going to let husband know about issue. Also found mouse nest in outdoor unit cleared out and found no wires chewed at this time but could happen in the future. Checked all other electrical components and connections. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.