Solved our problem and instructed us on future procedures
PCSA 2022 Heating Check Up Renewal Blower motor/wheel appears to be slightly off balance but not having any issues. System could be a little low on R-410A but not enough to add any at this time. Everything else was clean and checked out well. Will monitor during future check ups. System is operating normally at this time.
Nothing coming on. Cause of the issue was tripped breaker and low voltage fuse. Reset breaker and replaced fuse. Showed customer which breakers need to be off to clean electrified filter. System is operating normally at this time.
PCSAS 2022 a/c check up prepaid Contactor was looking very worn out again. Replaced it with a heavier grade one under warranty. Everything else was clean and checked out well. System is operating normally at this time.
Found bad contactor replaced. Did maint on other downstairs unit. Both cooling at this time all checks good, filter downstairs needs replaced.
Heating Furnace Repair - Cause of the issue was tripped limit. When the power went out while the furnace was running, rising heat from the heat exchanger caused the limit to trip. Reset limit, replaced filters, and checked system operation. Everything seemed to be operating normally at this time. Strongly recommend customer installs CO detector when possible.
Replaced contactor points very burnt. New filter customer stock. Damper for upstairs blowing by or sticking, very tight access, do they want to pursue this house for sale?
Mini split in resale shop not cooing well. Topped off charge tightened fittings. Got non repeatable hits inside . Cleaned filters should be done regularly.
PCSA 2021 PREPAID AC MAINTENANCE Everything was clean and checked out well. System is operating normally at this time.
Noise, turned on unit it made the noise itâ€™s from the unit rubbing the wall. Put foam behind it, seemed to fix it. If it happens again we need to send a couple guys to take the unit off the wall and foam tape the backside
Unit makes a knocking noise on initial start up during cold mornings in heat mode. Inspected unit cycled system, everything checked out. Spoke to Carl at crescent he said to adjust the charge, if that doesnâ€™t work itâ€™s probably something expanding or a reversing valve screwing up. Adjusted charge, if it happens again we need to be here on a cold morning to see it start up
1x Heating Only Check Up ckd system elec. heaters ok fefrigerant ok unit defrosts.
Contactor on outdoor coil was looking very worn. Replaced contactor and system is operating normally. Everything else was clean and checked out well.