Michael gave a range of options and maximized discounts
Jamie was very professional, courteous, friendly, knowledgeable, hardworking and thorough!! He reviewed and explained everything carefully and alerted us to maintenance items we might want to consider. We would love to have Jamie service our HVAC units again.
The tech was extremely polite and informative! I had a good experience!
Performed maintenance on a Lennox AC in Chula Vista. Condenser motor and compressor are amping in range. Starter component is showing signs of failure. Indoor blower motor is leaking oil heavily and is amping high. Indoor unit has signs of condensate leak on the floor. Evaporate coil is clean.
Replace existing system with listed equipment.
Technician arrived on site and started performing one HVAC combo tuneup. Started with the heater. Went through entire 20 point safety inspection. Static, motor amperage, heat rise, and safety components all checked out. Customer changed his own filter. Went outside to condenser and checked The coil, it was in good shape. Cleaned it with water as per the data plate no chemicals. Check motor amperage on start up and while running, and it was within the manufacture specifications. Tim sport is good indicating a good refrigerant charge. The coil, it was in good shape. Cleaned it with water as per the data plate no chemicals. Check motor amperage on start up and while running, and it was within the manufacture specifications. Tim sport is good indicating a good refrigerant charge. The ducts on the system are completely trashed insulation is falling apart could not get duck sizes off ducts because of wear and tear. Recommend replacement with new or six or eight insulation for better air
Arrived on site to perform fall tune up on a 2 furnace. Both furnace located in attic. Client stated no issues but was interested in some repairs that were recommended last visit. Cycled both systems to ensure operating.found both filter to be good as they were just replaced . Blower assembly are good slight dust. Motor were replaced as client wanted to replace motors. Both secondary motor controls are good. Both Inducer motors are in range. Evaporator coils good as they are new. Drain lines are good. Inspected heat exchangers and found they to have heat impingement over the years of operation. Advised due to age of heaters system are on borrowed time as they are operational just have some age to them. Temperature rise is good and in range. No protection on either unit. Cycled both systems to ensure system operating. Went over all summary of findings and areas of concerns and recommendations. Client are aware of how system are running and the condition. Clients did want to go forward
Adjusted the gas valve pressure and blower motor fan speed to reduce the vibration on the system during operation. Measured temperature rise and confirmed system much quieter now. Temp rise is 38F degrees. Checked filter.
Installation of a Single Stage Furnace, including plenum, thermostat, gas piping, flute connection, HERS, Permits, 1â€ EZ filter rack, and filter. Check Pricing.
Includes Installation of 2.5 Ton Single Stage 16 SEER Lennox Full System with MERV 11 Filtration Current offers include FREE UV Light resulting to $119/mo
Installation of 4 ton Lennox Condenser and Coil. Permits and HERS, and WiFi Thermostat.
Tested operation of system to diagnose and repair faults.
Installation of 4 Ton Variable Speed 20 SEER XC20 with Pureair upgrade and ducting. With $775 Lennox rebate, totals at $18,854
Installation of Comfort Pro 2 Stage System
Customer only had 10 minutes. Didnâ€™t give any pricing
Customer has a plumbing issue, has nothing to do with new install. Water coming out of copper piping under sink.
Also includes permits and hers testing Warranty: 10 yr parts 2 yr labor
Performed AC diagnostic on 13-year-old Goodman condensing unit. Upon my diagnostic I found that the systems R22 Refrigerant levels were very low this was the reason why the mid floor and top floor was not becoming cold. I was informed that the system was also charged up once in the past. There is a leak somewhere within the refrigeration cycle. After finding out that there was a leak present within the system I then found out that the compressor was failing under a load which was causing compressor not to energize once the condenser is turned on. System is only one stage and should be typically a multi stage or two stage system to improve efficiency and capacity to cool a three-story home. Repairs were available to charge of system with the required amount of pounds of refrigerant along with injecting a leak dye into the refrigeration cycle to return within 30 days to investigate possible leak location. Replacement options were discussed with Mr./Mrs. Olympia over the phone