Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Talked to homeowner about issue that peco found. They said joints needed to be sealed on duct work. Gave homeowner a price to seal duct using aluminum tape. Homeowner is going to do the work themselves instead.
Service call that the Upstairs Bedroom was overheating past the Setpoint on the Thermostat. Upon arrival, spoke with Homeowner about issue with the Thermostat. Found Thermostat was set to 71 Degrees and the Temperature readings on the Thermostat was 75 Degrees. System operates 3 Zones: Apartment Bedroom, Kitchen Area, and Basement. The Kitchen area was calling for Heat and the other two Zones were satisfied. Confirmed Temperature inside the Bedroom with a digital thermometer to ensure the Thermostat was reading accurately. Tested each Zone individually and checked the Zone Dampers and Zone Panel Control to ensure proper Voltages. The Damper for the Bedroom area is not accessible, and the location of the Damper in the Ductwork is not known. The Ceiling is insulated and dry walled immediately around the unit. When the Bedroom Zone is not calling for Heat, but one of the other Zones is calling, Air appears to be leaking by into the Bedroom Zone. To further troubleshoot, we would need to
Performed Precision Heating Tune Up on Propane Fired Lennox Furnace. Air Filter was recently changed and was in good condition. Was informed by Homeowner that there was a leak coming from one of the Pipes for the Furnace. Found water dripping from one of the 2" PVC Fittings on the Exhaust Pipe. Used Slilicone to seal around Fitting. No further water was detected. If leak persists, then we will have to repipe a section of the Exhaust Pipe. Cleaned Drain Lines for Furnace. Removed and cleaned Flame Sensor. Inspected Heat Exchanger and Burner Assembly. Brush cleaned Burners in place. Burners are beginning to rust but are currently clear and lighting properly. The Blower Motor Capacitor is testing at its lowest recommended rating. Also found the the Hot Surface Ignitor is very worn in appearance. Recommend replacement of the Blower Motor Capacitor and the Hot Surface Ignitor. Performed Combustion Analysis on Furnace while measuring Gas Pressure. Gas Pressure is set lower than recommended,
Install 6 ecobee WiFi thermostats custard men supplied thermostats run new wire to 2 thermostat common was missing, and also added a transformer to propane furnace to the three zone furnace/ac, went over all settings with customer shoded how to use and how to change battery on room sensor, Test and cycle all thermostats ok
Performed Precision Heating Tune Up on Oil Fired Boiler. Replaced Oil Filter and Oil Nozzle. Electrodes were in good condition. Cleaned Electrodes and checked for proper positioning. Removed Flue Pipe and cleaned Chimney Base and Flue. Heat Exchanger was full of corrosion and debris. Cleaned Heat Exchanger and reassembled Boiler. Put Boiler in operation and performed Smoke Test, Draft Test, and Combustion Test. Tested Expansion Tank and found that there was no Air Pressure in the Tank. No Water was present when testing the Valve. Due to the age of the Expansion Tank would recommend replacement of the Expansion Tank.
Replaced customer supplied aquastat and set aquastat to 180 degf. Tested operation. Performed combustion analysis and efficiency test, smoke test, and draft test on unit.
No heat oil boiler, aqustat not working properly bad transformer needs new aqustat quoted for repairs
Performed Precision AC Tune Up on Lennox system. Checked 20x25x5 Air Filter which needs to be changed. Homeowner is going to order a new Filter and change. Checked Refrigerant Charge and Temperature split of system. While performing Tune Up on system, found Blower Motor Capacitor was testing below the recommended rating. The Contactor on the Outdoor unit is worn and pitted. Also found one of the Compressor wires was wearing through the outer insulation of the wiring. Recommend repairing the wire, and replacing the Contactor and Blower Capacitor. Also found damage to the Outdoor Coil. Inspected the Indoor Coil and found that it is rusting. Due to age and condition of equipment recommend replacement of the Furnace and Air Conditioner. We did not perform a Heating Tune Up on this system for this current ESA Membership. Two Air Conditioning Tune Ups were performed, as requested by Homeowner. ESA Membership will be Up for renewal in July 2018. The office will call and schedule a Heating
Repaired low voltage wiring issues on Rooftop carrier unit in Devon for a restaurant