Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed precision heat tune up on Rheem gas furnace. Aprilaire 201 air filter is clean. Checked all electrical conections and components. Blew out condensate drain. Cleaned flame sensor. Checked temperature rise and performed combustion test. Gas furnace is working fine at time of inspection.
Found that the outdoor fan motor is locked up on 21 year old system. Gave homeowner a round about price of $1500.00 to replace the outdoor fan motor. But told him that if the system is low on charge also( we wonâ€™t know this until fan motor is replaced) than it was definitely not worth replacing on a 21 year old system. Also found indoor fan motor on gas furnace making some noise. ( homeowner is not worried about the furnace at this point. Recommend to homeowner to replace the a/c system. Called office and office sent over a quote to replace the system.
Performed 6 month quality check, checked air filter ok. Checked furnace setup. Tested water safety. Shut off humidifier. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Found outdoor unit capacitor weak , replaced 35/5 440v capacitor. Also performed precision a/c tune up on amana a/c system. 16x25x1 air filter is clean. Checked all electrical conections and components. Blew out condensate drain and tested pump with water. Found pump saftey not tied in, and not other water protection, recommended wet switch. Also checked out outdoor a/c unit. Found that installing contractor just put a/c pad on top of exsisting pad and ground has shifted. Recommend pulling out old pad and using several existing bricks to re-level, homeowner is going to leave it go at this point. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Performed cooling maintenance, checked media filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
reclaimed and removed old ac unit. Removed old heater and coil. Installed a new amana gas furnace with a amana coil on top. Ran new copper lines from indoor unit to new amana outdoor ac unit. Reconnected return duct work and adapted supply duct as needed. Taped and sealed all all duct work . Brazed and leak checked all joint in the copper lines, with 300 psi of nitrogen and soapy bubbles. Let vacuum down to 120 microns. Installed a new condensate drain with a ez trap wired in to the heater. Ran a new pump with new vinyl tubing ran over to discharge pipe. Installed a Aprilaire humidifier and wired it in to the unit with a humidistat. Replaced filter 16â€/25â€/1â€. Installed a new electrical box with a switch and outlet. New ac is on a plastic pad with rocks underneath. Installed a new disconnect and an electrical whip to unit. Installed a new t10 stat.
Disconnect, remove, and dispose of old water heater. Install new water heater over a new drain pan and elevate with 4 bricks, install water alarm and completed all connections using pro press fittings. Fill, purge and test water heater. Fill out water heater form. Measure and record water pressure. Adjust water temperature to Hot setting and take a picture of all control settings. Clean up work area.
Checked no heat complaint, found collector pan pressure switch not closing, found condensate backed up into pressure switch port. Blew out condensate trap and drains. Cleared pressure switch. Cycled gas furnace and checked operation. No charge just did heat ptu
Performed gas heat tune up, check electrical low and nigh ok replace filter and service humidifier test humidifier ok new pad and 201, clean sensor and check burners ok gas pressure ok performed combustion test and test condensation pump ok cycle furnace ok
Performed Precision AC Tune Up on Rheem System. Checked High Efficiency 201 Air Filter. Filter was clean and in good condition. Closed Damper on Humidifier. Cleaned Condensation Pump and AC Drain Line. Filled and tested operation of Pump. Inspected and tested electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge on system. Measured Supply and Return Air Temperatures. System is operating to standards at this time.
Performed heater precision tune up. Tested all safety devices, cleaned flame sensor, inspected air filter, inspected and tested humidifier, tightened electrical connections, performed combustion analysis and efficiency test. All working ok. Left humidifier enabled and turned on and set at 35%.
6 month inspection. Changed filter . Tested overall system and system is running to factory standards.
Upon arrival found thermostat frozen. Needs replaced . Temparily installed t4 until we can come back to replace with the correct thermostat. Took pic of the back of the thermostat. Replaced EIm and thermostat with HD display Honeywell and Redlink EIm. Programmed and tested and provided customer with instructions.
Performed Precision Air Conditioning Tune Up on system. Checked High Efficiency Air Filter. Their is no access to the Condensation Drain Pipe. Recommend installation of a Cleanout Tee and Union onto the Drain Pipe. While testing system, found Blower Capacitor and the Dual Capacitor for the Outdoor Unit were Testing below recommended rating. Recommend replacement of both Capacitors. Washed Outdoor Coil with water. Checked Refrigerant Charge onsystem. System is only producing about 13 Degree Temperature Split. Recommend adding R-22 Refrigerant to system. While onsite, inspected Hot Water Heater. Due to age and Condition of Water Heater recommend replacement. Included an Estimate for the recommended repairs and for the Water Heater. Estimate includes a Service Membership is an annual plan which includes 1 AC Tune Up and 1 Heat Tune Up. A Service/Trip Charge may be added to Recommended Repairs.
Upon arrival found thermostat frozen. Needs replaced . Temparily installed t4 until we can come back to replace with the correct thermostat. Took pic of the back of the thermostat.