Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
The person who took car of the work was helpful with questions asked.
I would recommend Di Bias heating to every one. Thank for getting out quick to fix the problem.
This heating co and their employees are the best
DiBiase worked with me to upgrade my air handler to heat better. While that was going on they also came to the rescue to help my Mother in Law whose heater had to be replaced all of the sudden. They dropped everything to get her system set up on a Saturday. They also thoroughly documented everything and sent pictures and followed up. What a great business and I am glad to not only use them for my home but also for my family.
I would recommend your company for to anyone
I forget the name but he was excellent. I would highly recommend your company
Found Bradford white natural gas powervented water heater locked out on a 6/1 code ( failed to light pilot). Opened up union and checked that I had gas to the control valve. That was good. Recycled call for water heater to ignite, found water heater sparking at metal door before going to pilot assembly. Found wire had been pinched from the factory and wore threw and was speaking to ground. Tapped up wire with electrical tape and re- positioned to no pinch wire. Water heater fired right up and is working fine again.
Checked noise from heat pump. Tested electric back up heaters. Checked air filter. Started heat pump, calculated btu output. Tested defrost cycle. Checked voltage, amperage and electrical connections, measured capacitor values. Found dual run capacitor reading lower than rating. Replaced run capacitor. Checked heat pump, checked operation temperature rise across coils.
Performed gas heat tune up, check electrical low and high voltage connections, replaced customer supplied filter, cleaned flame sensor and check burners check low and high stage heat performed combustion test check supply and return air temperatures ok, check total static pressure on ductwork ok test condensation pump ok, cycle gas furnace noticed water heater is 12 years, expansion tank has failed provided an estimate to replace water heater or expansion tank only. Customer decided to replace water heater, paid 50% for down payment office will follow up with customer to set up installation date Install Bradford White 50 Gallon Natural Gas Powervented Water Heater Drain, Remove, and Dispose of old water heater. Install new water heater in drain pan and install water alarm. Complete all mechanical and piping connections. Fill and purge water heater and test operation
Orginally customer called because of two ducts inside garage wall that was sweating. Customer worried about mold. Advised customer that we would have to open up walls to access ducts. Advised customer that it would make more sense opening walls in spring time. Customer will open walls for ducts. Advised customer that a reme halo would benefit their indoor air quality. Customer went ahead with reme. Checked customer complaints about outdoor unit being noisy. Could not find any immediate issues. System running as it should. Advised customer we would go more in depth during spring check.
Found water leaking directly under inducer motor. Caulked around edge of inducer motor and behind at gasket on collector box. Ran system for about 15 minutes and looked for water leaks, no leaks found. Put system back into operation. Gas furnace is working fine at time of service. System was installed 3/5/20.
Performed heating maintenance, replaced air filter, started humidifier, tested and set humidistat to 35% rh. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches,performed combustion test. Checked operation and temperature rise.
Performed heating maintenance, checked air filter ok. Serviced humidifier, cleaned drain and replaced water panel. Started humidifier, set humidistat to 35% rh. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, performed combustion test and checked temperature rise.
Checked no cooling complaint, found furnace breaker tripped, found a shorted power wire. Found that the stairway safety switch not wired correctly at the furnace 1900 box. Had hot on neutral. Retired box. Started air conditioner, checked operation and temperature drop across coil.
Checked over where bathroom vent was above kitchen ceiling there is a small water spot. More than likely this was cause from the metal pipe sweating. Told homeowner the only real solution to fix this would be to cut open the drywall ceiling and insulate around the supply boot and metal supply pipe. She is going to paint over the spot for now and is not that concerned to rip ope the ceiling at this time.
Motor replacement, new belt and new pulley for motor... 4 in outside diameter 5/8 shaft, 4-21-21 Luis and Barry removed old motor, need a new pulley, we will order new pulley 4-28-21 Luis and Barry installed new exhaust three phase motor new pulley and new belt check operation ok
Performed cooling maintenance, checked media air filter ok. Shut off humidifier for summer. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil
Talked to customer upon arrival and they explained their issue, this issue is that they canâ€™t maintain temp in pool area once exhaust is running, check exhaust operation and found exhaust running but making noise from motor windings check belt, belt should be replaced, motor is starting to go bad, we will emailed proposal to replace motor belt and pulley, would also recommend having pool pack checked out to make sure there is no issues with pool pack,
Performed cooling maintenance, replaced standard air filter. Cleaned eztrap. Checked voltage, amperage and electrical connections, measured capacitor values. Shut off humidifier for summer. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed six month quality, replaced standard air filter. Checked furnace setup. Tested condensate pump. Started gas furnace, checked fuel pressures. Started air conditioner, found outdoor unit did not start. Found comfort alarm tripped on pressure, could not reset, tried to interrupt powered but goes directly into lockout without trying to start. Unit has refrigerant pressure but can not reset alarm. Need to replace comfort alarm in outdoor unit and start and balance charge. Returned to replace comfort alarm, replaced alarm, started air conditioner, balanced refrigerant charge. Checked operation and temperature drop across coil coil.
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. Working great at time of QA