Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I forget the name but he was excellent. I would highly recommend your company
Heat tune up on Lennox single stage 50k BTU natural gas furnace. Inspected Hot surface ignitor and flame sensor. Burners are rusted but upon visual inspection during heat cycle are functioning well. Gas pressure 3.5 In. W.C. Natural gas. 42F temp rise. 5 MFD blower capacitor reading 4.8 MFD; OK. Furnace drawing within design amps (2.11). Combustion test proves integrity of heat exchanger; furnace operating at 88.1% efficiency. Customer is experiencing black dust from supply more than likely caused by deteriorating ductboard. Advised homeowner to call office concerning duct cleaning. The furnace itself is rusted inside (photos provided). Furnace is operating well at the time of this maintenance/tune up.
Heat Tune Up on 3 ton Goodman heat pump. 18F temp rise with 42F OAT. Replaced Aprilaire 413 filter (provided by homeowner). Cleaned drain. Indoor unit amp draw good. Electrical components of heat pump and pressures good. System is operating well at the time of this tune up.
Checked no heat complaint, found furnace set to 64 and itâ€™s 70 in the house, raised temperature, cycled furnace on the burners light and the blower came on and heated. Cycled furnace. Checked condensate drain itâ€™s clear, checked flame signal, itâ€™s strong. Checked blower and temperature rise. Blew out condensate drain, and cleaned flame sensor. No lockouts. To save the lockout code raise the thermostat temperature above room temperature and the thermostat says heat on and you have no heat.
Performed precision heat tune up on Rheem gas furnace. Aprilaire 201 air filter is clean. Checked all electrical conections and components. Blew out condensate drain. Cleaned flame sensor. Checked temperature rise and performed combustion test. Gas furnace is working fine at time of inspection.
Found that the outdoor fan motor is locked up on 21 year old system. Gave homeowner a round about price of $1500.00 to replace the outdoor fan motor. But told him that if the system is low on charge also( we wonâ€™t know this until fan motor is replaced) than it was definitely not worth replacing on a 21 year old system. Also found indoor fan motor on gas furnace making some noise. ( homeowner is not worried about the furnace at this point. Recommend to homeowner to replace the a/c system. Called office and office sent over a quote to replace the system.
Performed 6 month quality check, checked air filter ok. Checked furnace setup. Tested water safety. Shut off humidifier. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Found outdoor unit capacitor weak , replaced 35/5 440v capacitor. Also performed precision a/c tune up on amana a/c system. 16x25x1 air filter is clean. Checked all electrical conections and components. Blew out condensate drain and tested pump with water. Found pump saftey not tied in, and not other water protection, recommended wet switch. Also checked out outdoor a/c unit. Found that installing contractor just put a/c pad on top of exsisting pad and ground has shifted. Recommend pulling out old pad and using several existing bricks to re-level, homeowner is going to leave it go at this point. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of inspection.
Performed cooling maintenance, checked media filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
reclaimed and removed old ac unit. Removed old heater and coil. Installed a new amana gas furnace with a amana coil on top. Ran new copper lines from indoor unit to new amana outdoor ac unit. Reconnected return duct work and adapted supply duct as needed. Taped and sealed all all duct work . Brazed and leak checked all joint in the copper lines, with 300 psi of nitrogen and soapy bubbles. Let vacuum down to 120 microns. Installed a new condensate drain with a ez trap wired in to the heater. Ran a new pump with new vinyl tubing ran over to discharge pipe. Installed a Aprilaire humidifier and wired it in to the unit with a humidistat. Replaced filter 16â€/25â€/1â€. Installed a new electrical box with a switch and outlet. New ac is on a plastic pad with rocks underneath. Installed a new disconnect and an electrical whip to unit. Installed a new t10 stat.
Disconnect, remove, and dispose of old water heater. Install new water heater over a new drain pan and elevate with 4 bricks, install water alarm and completed all connections using pro press fittings. Fill, purge and test water heater. Fill out water heater form. Measure and record water pressure. Adjust water temperature to Hot setting and take a picture of all control settings. Clean up work area.
Checked no heat complaint, found collector pan pressure switch not closing, found condensate backed up into pressure switch port. Blew out condensate trap and drains. Cleared pressure switch. Cycled gas furnace and checked operation. No charge just did heat ptu
Performed gas heat tune up, check electrical low and nigh ok replace filter and service humidifier test humidifier ok new pad and 201, clean sensor and check burners ok gas pressure ok performed combustion test and test condensation pump ok cycle furnace ok
Performed Precision AC Tune Up on Rheem System. Checked High Efficiency 201 Air Filter. Filter was clean and in good condition. Closed Damper on Humidifier. Cleaned Condensation Pump and AC Drain Line. Filled and tested operation of Pump. Inspected and tested electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge on system. Measured Supply and Return Air Temperatures. System is operating to standards at this time.
Performed heater precision tune up. Tested all safety devices, cleaned flame sensor, inspected air filter, inspected and tested humidifier, tightened electrical connections, performed combustion analysis and efficiency test. All working ok. Left humidifier enabled and turned on and set at 35%.
6 month inspection. Changed filter . Tested overall system and system is running to factory standards.