During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. I checked out blower motor of any dirt or debris and itâ€™s dirty. Both blower motors on each system should be deep cleaned. Dirt has built up on wheel fins. Motor controls are in good standing for both systems. Evaporator coil is starting to deteriorate on both systems. Starting to fall off during maintenance cleaning. One of the compressors for smoke shop is failing. Exceeds past 30 amps and decides to shut off after running for hour. I did last maintenance inspection, in beginning of year and this was same issue I addressed. Lots of amps are being used while running systems.