Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed cooling maintenance on 2 air conditioners, replaced air filter. Cleaned condensate trap and drains. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioners, checked refrigerant charge and temperature drop across coils