Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Installed new daikin floor mounted unit in attic room area. Installed new daikin wall mounted unit . Installed new slim duct for wall mount unit to the knee wall in attic area. Installed new outdoor unit on leveled stone and pad. Installed new pump up legs on outdoor unit. Installed new disconnect and whip for outdoor unit. Installed new 10 wire from panel to outdoor and added new breaker for outdoor. Installed new lineset, communication wire and condensate lines for both indoor units. Flared all connections, pressure tested past 350 psi and evacuated below 500 microns. Tested each indoor unit in heating and cooling, tested condensate for each unit. System working properly. Install area cleaned and install went over with customer.