Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
My problem was difficult to diagnose, but Luis let me observe and educated me about the process and how my furnace functions and is malfunctioning. He was polite and professional.
Removed existing furnace and hung coil and installed a new amana gas heater in existing location modified a piece of supply ductwork as needed and taped all ductwork. Modified drain piping to work with heater applications. Modified flue piping and tested unit in both heating and cooling.
Found 60 amp breaker tripped to 5 ton outdoor heat pump. Reset breaker and instantly tripped on a call for heating. Contactor is black and burnt. Pulled power wires off of contactor that power the compressor and found compressor is electricity shorted to ground. To replace the compressor would be around $4,000 to $6000. Recommended to homeowner to replace the heat pump system. She is going to talk to a friend about the situation and get back to us on the next steps.
AC Tune Up 4 Ton Amana AC system. Found weak blower capacitor. Mr. Franklin decided not to replace. Is considering replacing furnace soon. Cleaned outdoor coil. Completed AC tune up form System is operating well at the time of this tune up.
16.5 F temp split. Filter ok. 65 Lo Pressure 50 superheat. Indoor metering device is a piston. Insulated section of suction line near evaporator where Mrs. August noticed frosting. Presented estimate to charge system up to 2# of R410A. Mrs August decided to wait to see if system continues to undetperform/struggle this cooling season. Emailed estimate for charging system.
PECO heat pump tune up. Can not control electric heat with existing thermostat. There is a 6â€ flex lead in crawl space that is detached at take off fitting and collapsed (laundry room lead). We will provide an estimate to replace flex lead. Mrs. August paid for ECOBEE 5 thermostat install. 50F degree temp rise from Heat pump. Replaced Aprilaire 401 filter. Repiped evaporator drain that was pitched backwards. Verified condensate pump operation. All electric motors and components ok. Both coils are in good condition. Refrigerant pressures ok. Also checked newer Carrier air handler that serves as an electric heat only air handler for basement duct system. Cleaned washable filter. Mrs. August signed up and paid for GAHP Membership for Gibson (Norodyne System).
PECO Heat Pump Tune Up for 2.5 Ton heat pump system. 16F temp rise during heat pump operation. Replaced 16x25x1 filter. Coils, electric motors and components ok. Heat pump pressures ok. I also made a call for cooling as the cooling season is approaching and the equipment is mismatched. Subcooling 6 Superheat 6. There is a noticeable kink in suction line near service port. Recommend EZ Trap and a membership with us so that we can assess equipment during cooling season on a demanding/reasonable day.
No heat , found system off upon arrival asked customer to set stat to call for heat and found system giving a code 32 pressure switch issue, check all venting and drain ok inducer pulling good vacuum, check intake and exhaust pipes ok, check secondary collector box, found some carbon, also found that inducer is getting weak, canâ€™t over come the resistance across heat exchanger and also due to heat exchanger starting to malfunctioning, performed inspection on furnace found blower wheel super dirty restricting airflow, performed smoke test on unit and system failed heat exchanger test, would recommend upgrading furnace due to problems. Currently furnace is in operation by customer would recommend doing recommend repairs or furnace replacement for safety purposes
Performed Quality Assurance On recently installed Amana AC system. Completed Checklist Form in System. Reviewed installation with homeowner.
Reclaimed and removed old condenser and evaporator coil. Installed new condenser and evaporator. Installed new disconnect and whip. Installed and leveled new pad. Installed new line set and brazed in equipment. Installed new ez trap and condensate pump. Ran vinyl into sump pump. Wired safetyâ€™s to cut r wire. Reconnected ductwork. Evacuated line set down to 265 microns and leak checked. No leaks found at time of install. Tested new system. Delta t 21 degrees. System running perfectly at time of install.
Custome has two Fujitsu ductless outdoor units, one outdoor has three head and the other outs door has two heads, all heads, need drain repairs, needs new drain currently drain donâ€™t go all the way down with line set, the unit with three heads, is low on refrigerant, pipes freezing during testing, repairs are needed for only the three head unit, need to recover refrigerant pressure test all 3 set of lines and outdoor unit, find the leak, fixed the leak and pull vacuum then charge unit back up based on manufacturer data, recommend having Sam out here to give customer a price to replace units, we we email customer with estimate on repairs as well total lightning of drain hose needed is about 100 feet,