Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Quality Assurance On recently installed Amana AC system. Completed Checklist Form in System. Reviewed installation with homeowner.
Reclaimed and removed old condenser and evaporator coil. Installed new condenser and evaporator. Installed new disconnect and whip. Installed and leveled new pad. Installed new line set and brazed in equipment. Installed new ez trap and condensate pump. Ran vinyl into sump pump. Wired safetyâ€™s to cut r wire. Reconnected ductwork. Evacuated line set down to 265 microns and leak checked. No leaks found at time of install. Tested new system. Delta t 21 degrees. System running perfectly at time of install.
Custome has two Fujitsu ductless outdoor units, one outdoor has three head and the other outs door has two heads, all heads, need drain repairs, needs new drain currently drain donâ€™t go all the way down with line set, the unit with three heads, is low on refrigerant, pipes freezing during testing, repairs are needed for only the three head unit, need to recover refrigerant pressure test all 3 set of lines and outdoor unit, find the leak, fixed the leak and pull vacuum then charge unit back up based on manufacturer data, recommend having Sam out here to give customer a price to replace units, we we email customer with estimate on repairs as well total lightning of drain hose needed is about 100 feet,