Haas was quick to get us on their schedule & come out to investigate our problem. It turned out to be something the power company needs to fix, but we wouldn’t have known that without their rapid response. Nick came right on time, the problem was & explained what to expect. We will definitely call Haas in the future.
Nick provided excellent customer service.
Service charge Receipt
Todays visit stemmed from a previous estimate. We installed a dedicated 60A 240V circuit through the basement bulkhead and into the garage. Circuit is about 80ft long and purposed for EV Charging.
We have provided pricing regarding the EV charger.
Customer lost power to half their home. I arrived at the home and opened the 200 amp QO series Square D panel located in the front corner of the basement. The panel is in excellent condition showing no signs of burning, corrosion or rust. I tested both wires feeding the main breaker and quickly determined that a phase was lost. This is a power company issue (BG&E). Meter can is a pedestal type.
Replace the two switches in the closet in the master. Replace the two switches in the kitchen. Install new dedicated circuit for the sump Install new sub panel next to main panel to clear up and organize main panel. Change receptacle in kitchen and living room to white currently almond.
Replaced attic fan motor and thermostat with new customer supplied thermostat and motor.
This estimate includes the installation of 2 customer supplied devices This estimate includes the installation of the customer supplied light fixture in the pantry. This estimate includes the installation of a new customer supplied thermostat. We have installed the new customer supplied lighting at basement and pantry. In addition we have made a repair in the panel, circuit controls internet. We have also repaired the bathroom receptacles. Gfci was installed in the powder room. Lastly we have installed a customer supplied thermostat.
Replaced a faulty dimmer at bottom of basement steps for basement recess. Also replaced a switch for kitchen light. Verified proper operation of all completed work with customer.
Ran a new feed for the light post out front
I ran a new feed for the light post out front I drilled from a receptacle in the living room to outside into a newly installed weather proof box. I then siliconed around the box to protect any weather getting into the home. Then I trenched from there to the existing light post. I ran 1/2 inch pvc pipe and ran thhn from the weather proof box to the light post. Then made my connections in the light. The existing photo cell was burnt out so I installed a new one on top of the weather proof box. I installed a weather resistant gfci with a in use bubble cover to protect the light from potential electrical hazards. I then back filled my trench and tested everything Customer has a 1 year warranty on work preformed
We have replaced 5 existing fixtures with new customer supplied fixtures on the first and second floor. 3 near garage entrance, 1 rear exterior and 1 in the master bedroom entrance. In addition we have installed a new customer supplied recess light in the master bathroom. Lastly we have repaired the rear exterior receptacle and have provided GFCI protection.
Local electrician to install light fixture
Installing ceiling fans in family room and master bedroom
Replace timers to exterior lights.
Installed timers for exterior lights. Removed old timers.