Michael was very professional and put everything in terms I was able to understand. He explained EVERYTHING! Very courteous and knowledgable which gave me peace of mind. I vr will requedt him every time.
Always happy To use Haas and Sons
Service was amazing, excellent communication from start to finish. Will definitely use again if the need arises.
Easy scheduling, communicative process. Will call again
Very professional, easy to talk to. Will request Michael on the next project!
Haas Electric did a great job for me from start to finish. They set an appointment to assess my needs quickly, contacted me to confirm their rep Alan was on the way when expected, then offered me great options for the project. Nick arrived promptly on the scheduled install date. He confirmed what I wanted and then completed a great install that included making sure I was satisfied and familiar with my new exterior lighting. Two thumbs up.
Mike the electrician is a very honest man. I thought I needed a new ceiling fan/light but Mike took the time to trouble shoot it and was able to find the problem. He certainly could have said I needed a new one which would have definitely cost much more, but did not. He was very pleasant and took the time to explain things. I would highly recommend them to all. How nice to deal with honest people!
I will recommend your company to others! Nick was awesome! He was very efficient and cleaned up after his work!
Always a great job :-)
Haas and Sons is definitely my go to service. Alex has been out to our house a couple times and I have more work planned for him in the future. He does an excellent job defining what needs to be done with options presented as possible and the finished work is exemplary.
The service included a breaker panel upgrade to support receptacle and ceiling fan installation for a new screened in deck. All the options were carefully explained with my inputs and thoughts welcomed. The work was methodical, carefully executed and looks great.
Very thorough and precise. Faulty circuit repaired and restored in short order. Great job!
Nick is knowledgable, professional and answers all our questions.
Mike did a thorough inspection of the electrical system within my house and located the problem that I was having with one of the circuits. Mike is very professional, methodical and courteous. I would not hesitate to call him again.
This solution includes the installation of 3 new combo detectors and 3 new standard smoke alarms. This solution includes the the installation of an audible GFCI alarm for the sump pump We have installed 6 new smoke alarms. 3 standard alarms and 3 combo detectors. In addition we have installed a whole home surge protector at the main panel and installed an audible alarm GFCI at the sump pump location. We recommend that the 3 remaining smoke alarms be replaced.
Replace bathroom vanity light
This solution includes re-wiring at bathroom receptacle and installation of a gfci receptacle at front exterior to include an in-use cover. This solution includes the alleviation of the double tapped neutral wires and installation of 2 recess lights in the basement. We have begun the installation and repairs. Exterior plug now working and 1 recess light installed. We shall return on the 27th of November. Basement lights now working, switch leg was pulled to light above dog crate area.
We installed a new Emergency disconnect on the outside of the house and moved the existing grounding to the new emergency disconnect and separated the grounds and neutrals in the panel We went through the basement and replaced and rewired all loose receptacles We replaced the old/ torn service cable with a new to prevent further damage to the electrical system Permits and inspections
Pricing has been delivered regarding the various electrical projects.
This solution includes the installation of a 240V 50A dedicated circuit for EV charging. Also included is the necessary load shedding device to accommodate the 150A service.
I removed all the receptacles on the pier and i replaced them with weather resistant tamper resistant receptacles with new in use bubble covers. I removed a single pole 30 amp breaker and installed a 20 amp single pole gfci CH breaker in sub panel
Installed customer supplied ceiling fan in the family room.
We have updated the pricing for a new 200A service, panel, updates to grounding and bonding. This now includes a new generator interlock kit to be installed on the new 200A panel. Permitting and inspections included. It is our recommendation that the vehicle should not be charged on the existing 120V 15A circuit located in the garage.
Upon my electrical inspection to the home i found violations that have to be corrected according to the national electrical code. And i found issues in the home that should be corrected to ensure the safety of the residents and the Efficiency to the electrical system Someone removed the existing electrical panel and installed a 200 amp square d homeline electrical panel but did not pull a permit and the work was never inspected. The SEU cable that fed the original panel was 2 awg and thats what feeds the 200 amp panel now. The seu cable MUST be replaced with a 4 awg seu cable thats rated to handle 200 amps. Also the grounding and bonding is not up to date for code which is required anytime a panel is to be replaced. The home is missing a ground rod outside of the home and the wire size going to the cold water ground is the wrong size. It needs to be a #4 ground wire within 5 feet of the entrance of the main water shut off pipe. Also the home is missing a bonding system at the wat
i removed and replaced a ceiling fan with a customer supplied ceiling fan then installed a side mount fan rated box for the fan and replaced a 3 way switch I removed 2 3 way switches and re wired the travelers with the hot wire to make the switch with the switch leg a single pole switch. Then I installed a caseta smart switch with a pico remote so the remote switch was near the mother in laws doorway to make turning on that light more accessible
Pricing has been delivered.
Remove and replace the old motion sensor light with a new higher quality one
Replace light in landing Replace ceiling fan in master bedroom Replace light and box that fell out of the ceiling