Came in, determined problem, gave price, fixed problem, offered advice.
The electrician showed up in a timely fashion and wired a box for a fan we want to install when our deck ceiling is completed. He did a nice neat job and was at the house just a short time.
Mr. Weber was efficient and knowledgeable, he was able to give me several options and prices and immediately went to work after a choice was made.
The technician was very helpful and knowledgeable and was very helpful.
Electrician was professional, courteous, efficient, and kept me informed at all times.
Had a ceiling fan installed. Showed up in the early portion of our appointment window, completed work quickly and cleanly. Also didn’t mind my cat pestering him and laying on his tool bag :)
We had a great experience with Haas & Sons electric inc. The technician Mike was very knowledgeable and also solved our problem very quickly! We are very satisfied with the work he has completed!
I had a great experience with Haas & Sons. Mike came on time, assessed the problem, and quickly got to work addressing it. I highly recommend!!
Installed a customer provided dining chandelier nd a customer provided hook to move it over to above the table. Verified proper operation of all completed work with customer.
Customer had a faulty breaker on the refrigerator circuit. Replaced breaker with a 20 amp BR breaker and tested wires to verify there was no problems. If problem happens again there is a problem with the refrigerator.
Customer had an exhaust fan install by another company and needed us to vent the fan to the exterior of the home. We ran 4inch flexible venting up to ta new gooseneck vent out that I installed. We cut a 4inch hole through the roof and sealed flashing down with roofing tar. We placed shingles back and secured them down with roofing tar as well. this new vent out has a metal screen to keep birds and squirrels from entering venting as well as a damper to keep insect and outside air from entering when fan is off.
Removed 3 flood lights on home. 1 light out front on second floor soffit and 2 in the back 1 at each corner. Lined lights up according to customers needs and based on what was there previously. Lights were provided by company. Verified proper operation of all completed work. Provided quote for damaged SEC Larry 240-575-0063
Installed a new 50 amp circuit from panel to disconnect with gfci protection to a plug on garage door frame for a car charger using 6 awg copper wire. Tested voltage at receptacle, customer does not have charger yet. Panel is a cutler hammer BR series GFCI disconnect is a QO home line series
Customer has a GE gas stove/oven combo unit. The oven part only was constantly tripping the duel function breaker. I found that igniter in the oven was causing the breaker to trip by giving a false Ground fault reading. After checking the stove location (distance) from the sink i found that the outlet was far enough from the kitchen sink that the GFCI feature was over kill. The outlet was around 8ft away. We changed out the duel function breaker for a combination breaker and the issue was fixed. The oven is now working properly.
Customer drilled a hole to relocate doorbell button, in doing so it nipped the wire causing the wire to break and the transformer to short out. We replaced the transformer with a larger/ stronger one to power a video doorbell as well as repaired the broken wire. We hooked everything back up and tested the doorbell and chime and it worked properly. Doorbell is now ready for ADT to install video doorbell.
Located 2nd set of switches for kitchen lights.
Installed 2 new fan boxes on top floor of home. 1 in bedroom at top of steps to left and 1 in master bed closet/sitting room. Both use the switch for the scr and the receptacle has been wired to stay on. Installed a customer provided fan in the bedroom and customer is going to get a light for the closet. Verified proper operation of all completed work with customer.
Installed a new 50 amp circuit in garage with a nema 650r receptacle. Circuit is on a 50 amp gfci breaker. Also replaced wire for existing plug and put that circuit on a 50 amp gfci breaker. Verified proper operation of all completed work.
Rough in ceiling fan on porch getting power from sconce light outside. Mount fan box so when soffit is complete fan can be hung on box.
Replaced smoke detectors in home with new smoke/ carbon monoxide combo detectors (1 on each of the 3 floors). These new units have 10 year lithium ion back up batteries. We replaced customers standard thermostat with a new customer supplied NEST smart thermostat. We started setting it up but left the WiFi setup and the app setup for the customer. We left the box with all the setup instructions with MR. Dillard.
Installed a new circuit for shed out back of home and 2 receptacles under steps of deck. Shed has 2 receptacles and a switch for a future light fixture and receptacle outside. All 3 outdoor receptacles have in use covers on them and are weather resistant receptacles. Circuit is fed by a 20 amp dual function breaker. Also re routed wiring in laundry room that was inside a wall that has been removed. Also installed a gfci over water heater for power vent to plug into and a second keyless fixture for additional light. Verified proper operation of all completed work with customer.
Tapped out of pull chain fixture in the basement crawl space and and a plug next to the new humidifier. Moved washer outlet over roughly 8 inches away from water drain for the washer and installed a GFCI in its place.
We have repaired the oven/stove circuit. We have installed a new 50A GFCI breaker and have corrected the 240V receptacle. In addition we have corrected the wire short associated with the master bedroom ceiling fan. Lastly we have safely capped off the existing exterior wire that was still live, this wire has also been removed from the existing breaker and also capped off in the panel.