Michael called when he was on his way. He completed the job. He was very professional throughout the whole process. Would recommend Michael and the Haas company.
Alex was the technician on the job. He was positive, personable and professional. He quickly provided an estimate on the work and gave me some options for adding recessed lighting to a closet ( even though I chose not to do it). He was very knowledgeable and explained all the work. He did an excellent job !! I would give him 5 stars !!!
Excellent work. Good review of work & products prior to doing the work. Alex is an e excellent worker. Keeps on the job and cleans up after.
Alex did a great job ! He was friendly and personable. He explained the work that was needed, and provided me an estimate of the work within minutes. He completed the work in no time at all and did a thorough job. In addition, he provided recommendations to improve the electrical system throughout the house.
Nick was personable and knowledgeable. I’m grateful for the same-day service call that fixed three different electrical problems.
Reason for today’s visit was to assess power loss in the home. When I arrived at the home, customer stated that she was using the treadmill earlier and then realized that she lost power to most of the Home. Well going to the Home I started to notice that This was definitely larger than a single circuit shorting out. This led me to go check the main panel to see if there was proper power coming into the home. When I tested the main log above the main breaker, I was only getting power on one leg. And then went outside and opened up the meter and found one of the legs was no longer in the crimp For the line side of the meter. I noticed that it was occasionally arcing because it was trying to make contact. I had customer call Pepco while I was on site to help them get this remedied. While standing over there, checking the power we looked up and noticed that the main triplex line coming to the home was resting on the roof. There’s not enough clearance, allowing the cable to properly termin
I ran a #4 bare copper ground wire from the main shut off valve in the utility room. Stapled it to the joists then ran it through the finished ceiling in the basement to the main electrical panel. Then i installed the ground wire and landed it on the ground/neutral bar in the main electrical panel I removed all smoke detectors in the home (3. One for each floor) these were the ones you could remove the battery. I replaced them with carbon monoxide smoke detector combination 10 year built in lithium battery hard wired interconnected units (customer has a fire place) i also labeled them the date installed and the date recommended to change them out I removed a standard receptacle the wash machine was plugged into and i installed a tamper resistant GFCI
Replaced broken single pole switch controlling kitchen sink. Also replace the switch control and the disposal while we were in the two gang box. Well on site we provided and installed a new LED flat panel surface mounted light to replace the older style fluorescent light in the kitchen.
Remove existing federal pacific panel and replace with new 32 space panel and add cold water ground as well as properly bond and ground water heater and gas furnace. Also replace existing service cable as it’s damaged.
We have installed the new customer supplied light fixture in the dining area.
We have installed a new customer supplied chandelier in the living room, customer to hang the crystals. In addition we have installed a new dimmer to operate the chandelier, surge protection and have bonded the water heater.
VIP Membership for customer #review
Run 15 amp circuit from main electrical panel to the kitchen in then basement 15 amp Homeline arc fault breaker for dishwasher they are adding in the future Gfci protected Also from existing outlet on kitchen counter top drop down and add a plug on corner of the wall so the customer can plug in a fridge when they get it We are not responsible for patching and painting any holes we need to make for running the electrical wire I ran a 14-3 wire from main electrical panel to the basement kitchen. I ran the 14-3 wire in case the customer wanted to put the garbage disposal on its own circuit like the code requires they can. Dishwashers and garbage disposals are allowed to share a neutral. I then installed a 1900 box with a gfci and a RS cover plate for the new dishwasher Also i ran a new jumper from a kitchen counter top receptacle to a old work box i cut out next to the cabinets and installed a new tamper resistant receptacle for a new fridge customer will be getting Customer has a
I removed and replaced a customer supplied ceiling fan
Customer called about multiple issues I removed and replaced a faulty stacker switch in bathroom Tested everything 30 day warranty
This estimate includes the installation of a new customer supplied ceiling fixture. We have installed 2 customer supplied fixtures, alleviation of the double tapped neutrals, installation of a proper rated breaker and have demoed the under the cabinet light.
This estimate includes the installation of 2 new breakers in the existing panel. This estimate includes the installation of a whole home surge protector. We have installed a new whole home surge protector and have replaced the 2 bottom breakers in the main panel.
Customer had a damaged switch which stopped the circuit from feeding to other rooms I removed and replaced the switch and everything works fine now 30 day warranty
I removed and replaced devices in customers master bedroom Needed to be gfci protected due to no grounds in boxes Removed a switch and wire in closet and put it the attic in a new work box and blank plated it off 30 day warranty
I removed and replaced two upstairs bathroom exhaust fans with company supplied bathroom fans with lights I also vented the new bathroom fans through the rough of the house into gooseneck vents I removed and replaced the front light outside with a company supplied dusk till dawn LED wall sconce and I siliconed around the fixture to protect it from weather Customer has a 6 month warranty on all work