Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed peco inspection, replaced very dirty air filter, tested electric back up heaters. Blew out condensate trap. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, heat pump doesnâ€™t start, found outdoor unit locked out on high pressure. Reset lockout, started heat pump, checked refrigerant charge ok lockout must have occurred from dirty filter. Recommend having unit maintained, $189.00 per year to join maintenance plan