Cause of the issue was the inducer limit had to be reset. Took flue apart from the furnace to the basement wall and cleaned it out. Didn’t see anything big enough to clog the flue. Put flue back together and tested flue draft. System appears to be operating normally. If problem reoccurs the flue May need taken apart outside the house and possibly replaced.