Cause of the issue was bad thermostat which was causing a short in the control board of the furnace. Replaced thermostat. Inducer motor is a little loud on furnace and contactor was getting very worn out on outdoor coil. Recommend customer monitors operation and repair as needed. System is operating normally at this time.