Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Professional, timely, friendly and no heavy selling.
Luis was very professional, he listened to our concerns with our water softener and fixed everything. He asked us about our mask preferences, kept booties around his shoes to keep our house clean and never felt like we were being upsold
Performed precision a/c tune up on carrier a/c system. Replaced 14x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked temperature split. Found weak 45/5 mfd capacitor, replaced capacitor and tested. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of inspection.
Performed precision a/c tune up on amana a/c system. Aprilaire 413 air filter is clean. Checked all electrical conections and components. Blew out condensate drain. Tested condensation pump. Tested outdoor capacitor. Checked temperature split. Checked refrigerant pressures and temperatures at indoor and outdoor units. Found very dirty outdoor coil wash and cleaned outdoor coil. A/c system is working fine at time of service.
Performed quality assurance inspection on recently installed amana gas furnace. Aprilaire 413 air filter is clean. Wiring looks good. Checked temperature rise. Performed combustion test. Furnace is working fine at time of quality assurance inspection.
Completed installation of new amana gas furnace. Removed old furnace and return drop. Installed new metal return drop on aprilaire filter boot. Reconnected flue piping. Reconnected supply duct work with new duct board plenum and sealed duct connections. Installed new outlet and switch on furnace. Installed new condensate pump and adapted condensate drains. Tested furnace operation. Checked gas pressure, static pressure, and combustion testing.
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Found rust running all the war down the seam. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Found inducer running at full load amps and is noisy. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test. Found very high co pegged meter could not do combustion test. Recommend replacing furnace due to age, condition and needed repairs.
Heat Tune up: Crown oil boiler. Removed heat exchanger cover, brushed and cleaned heat exchanger, and chimney breech. Made call for heat from thermostat. Replaced RF-1 Filter. Replaced nozzle. Checked condition and alignment of electrodes. Tested oil pump (pressure and cutoff). Checked transformer. Tested circulator. Checked hydronic piping for leaks. Checked oil piping for leaks. Checked all controls and wiring. Smoke test: Good Combustion/draft test: Good Homeowner renewed AC/Oil heat plan membership.
Check water treatment system operation, found some gray coloring around and bottom of inside brine tank, found no salt inside tank, check operation went trough regeneration/backsplash and fill process everything works ok called novo and they said is normal some times to see that gray coloring, that comes from the salt, also they recommended to always have salt inside tank. Added three bags of salt to brine tank
AC Tune Up 2.5 Ton Ruud Unico System. Replaced Filter. Checked temp split. Cleaned EZ Trap. Checked Temp split. Checked refrigerant data. Completed AC Tune Up Form System is operating well at the time of this tune up.
2 AC tune ups. Replaced filter. 20F temp split for basement System 16F temp split for 2nd floor System. Cleaned outdoor coil for 2nd floor system. All electric motors and components ok. Outdoor voltages/compressor amps/indoor amps ok. Systems are operating well at the time of this maintenance.
Provided estimate to make some corrections on attic flex ductwork, and also installed five customer supplied registers,
Found furnace in the basement where water had been leaking out of the furnace. Removed panels to access inside of furnace. Found that down inside the blower compartment the rigid condensation trap had split possibly due to zip ties being to tight and vibration from blower. Called warranty company to inform them of the situation. Fixed and repaired condensation trap by cutting out section of broken trap and using existing drain connections . Cycled furnace and tested operation of condensation trap. No leaks. Furnace is working fine at time of service.
Went over the removal and re installation of baseboard heat with customer. Found that in kitchen area it would be better to completely remove old section of base board, and re install a new 4 ft piece of baseboard in kitchen area. Downstairs in the drum room area, baseboard could be temporarily removed and capped off until new walls are built to re install exsisting baseboard with pipes now running behind 2 new finished walls. Also talked to customer about adding a supply to basement from exsisting high velocity. There are no closets to go through so only could be installed by chasing out supply run with dry wall. Also told homeowner that we could also look at installing a mini split for the basement area. Homeowner will get back to us on there decision.
Performed precision oil tune up on crown oil boiler with 3 zone valves. Replaced rf1 oil filter. Brushed and vacuumed heat exchanger and smoke pipe. Replaced oil nozzle. Performed smoke and a combustion test on oil boiler. Oil boiler is working fine at time of inspection.
Found system completely frozen up with about 3â€ of ice on evaporator coil and suction line frozen completely back to the compressor. Checked air filter and air filter is slightly dirty but not to where it would really effect air flow. System is an r-22 system from 2005. Also found blower motor running, but not putting out any air flow due to coil being a block of ice. Can not check refrigerant pressures while system is frozen up. Talked to landlord about entire situation. Recommended to homeowner to replace the system. Talked to the office about issue, office waved the diagnostic fee and we will need to return to check to see the cause of freezing issue.
Checked no cooling complaint, found air conditioner running but not cooling. Checked outdoor unit, found only fan running no compressor, checked run capacitor, found open compressor side. Replaced dual run capacitor. Started air conditioner, checked refrigerant charge.