Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
No ac, found system running upon arrival thermostat set to 74 room temp 74 check ac operation found dirty air filter, check supply and return air temperature 18 degree split 68/50 thermostat is located from of the office and main return is located at the back of the office, check outdoor unit refrigerant pressures capacitor and contactor ok super heat and sub cooling ok 320/120 8 super heat and 17 sub cooling system has new air filter, would recommended replacement of filter every 30 days
Two of rezner heaters not working, one of them will ignite but fan would no come on, found bad fan delay relay, quoted of repairs customer ok cycle heater and came on ok, on other heater found restricted orifice and also fan relay would not close, quoted for repairs customer ok repsirs, after all repairs were made cycle heaters and performed combustion test ok
Found system off when I arrived. Homeowner had just replaced indoor air filter. Turned on thermostat and went outside to outdoor unit, found everything running. R22 pressures were 240/69 with 11 degrees of subcooling. Talked to homeowner about issue and he was setting his thermostat at 69 degrees and system is running a lot but cooling. Suggested to homeowner that beacause a mobile home is not insulated very well and there is not attic, the a/c will run a lot to maintain temperature. Suggested to homeowner to raise the temp up around 75 degrees to se if he gets better results. Homeowner had someone else check out the system recently and they said they didnâ€™t see any problems also. Checked temperature split inside and it was 17 degrees. System is working fine at time of service.
Installed propane furnace horizontally right fixed the supply plennum. With 2x4 wood underneath re attached condensate , venting and gas hook ups