Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
No heat, oil furnace flue pipe blew off the chimney base, upon arrival found furnace off, noriced system has open return and right next to it there is a atmosphere water heater, furnace is in bad shape, soot every where flue pipe burner and heat exnchager cleaning ports, noticed no oil filter installed, told land lord this furnace is not safe to operate and red tagged furnace, informed land lord about situation, necessary repairs need to be done for furnace to be in safe working condition, will need a return cut in return on first floor to basement and use joist base to create a rerun boxt then we can attached to furnace return, we could use flex and 14 in flue pipe, will need there to four 90s, sheet metal and grill, on cleanis side of furnace will need new strainer new nozzle new electrodes, and also installation of new RF-1 oil filter currently has no filter, and the deep cleaning on furnace with a 6 in draft regulator damper....we will get back to customer with pricing
No heat call in Marcus hook turns out to be an unbled oil line after a refill of oil. Furnace was bled and resident has heat for the snow storm about to arrive in hours.