Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt did great. However being charged $160 extra on top of the $84 for the visit is totally unfair. And that is for a spliced wire. No parts or anything else. If that doesn’t get severely reduced, I will be looking for a different vendor. Because the trust will be broken.
Arrived on time, could not have been more professional, Excellent service. Thank you!
We have received excellent service from DiBiase Heating and Cooling Company. The administrative staff is friendly and professional and the service technicians are prompt, courteous and knowledgeable. I highly recommend this company to anyone seeking HVAC service.
Excellent service, kept me informed & very professional.
I called many heating companies to come out and check my unit but DiBiase heating within an hour called me back and got my heat working again. It's only been about an hour since they worked on it but my home is heated again with no problems. Thank you guys again for doing a great job. Definitely 5 star satisfaction rating.
Removed heater and installed a new amana gas heater on pump he existing return box . Installed filter inside unit like it was before. Adapted gas piping and flue piping as needed. Installed a new piece of metal to get the height to attach to existing coil. Taped , caulked and sealed all ductwork. Adapted to coil drain and heater drain into a new condensate pump. Pump is wired in to heater. Installed a new thermostat.
Performed heat pump tune up check electrical low and high ok replaced air filter, inspect and test back up heat ok also check indoor coil for any dye signs did not see any dye on inside and outside unit, needs more time to show up the dye, check outdoor unit refrigerant pressures ok 400/100 capacitor and contactor ok high side little higher than normal but is matched to high velocity unico system, cycle unit ok
Performed propane gas heat tune up check electrical low and high voltage, clean flame sensor and burners, burners have lot of rust, check gas pressure performed combustion test ok also noticed some condensation on bottom portion of secondary heat exchanger, also performed a smoke test and heat exchanger failed on test, combustion results are within safe range, still recommend having the system replaced,
Oil leak, found some oil under oil filter canister, check gasket, filter and o ring, found bottom screw to be leaking, recommend replacing canister, called customer with option and pricing customer approved repairs, replaced canister and oil filter, test and cycle furnace .... oil flow ok, performed combustion test ok
No ac found unit locked on low pressure short cycling, reset unit and found pressures to be low 410, added 2 lbs and also added dye to see if there is any leaks or valve caps are leaking no charge, we will check indoor and outdoor coil during next service visit
Replaced both thermostats and also female adapters on inlet and outlet of water heater. Adjusted thermostats and tested temperature. No leaks present.
No hot water, found breaker in the off position, also cold water side shut off valve closed, cold water side shark bite connector is leaking pretty bad, water got into insulation and both thermostats have water, all connections are wet, ohm out both Elements ok, would recommend replacing both thermostats and replace shark bite with new copper/brass fitting quoted for repairs
Performed ac check up, on high velocity system attic, check electrical low and high ok replace customer supplied filter 14x30x1 flushed drain ok check outdoor unit 410 pressures check capacitor and contactor ok super heat and sub cooling ok Cycle unit
No ac found system off upon arrival,,,room temp is registering 78 set to cool 74 and unit came on check indoor blower ok temp split supply air 49 return air 74 check filter ok outdoor unit ok refrigerant pressures ok 200/75 cap and contactor ok cycle unit and unit came on with no issues
Performed ac tune up check electrical low and high ok flushed drain and test pump, pump making grinding noise and takes long time to discharged, check filter and quoted for replacement customer ok price, new high efficiency filter, check impose coil, lots of rust on copper coil, high risk on coil to start leaking, check outdoor unit refrigerant pressures only was able to check back pressure high side could not get reading capacitor and contactor ok cycle unit check temp split ok emailed quote to replace condensation pump
Performed ac tune up check electrical low an high ok filter ok check split, flushed drain test pump ok check outdoor unit refrigerant pressures capacitor and contactor ok cycle unit ok recommended adding ac renew due to previous compressor problem emailed proposal
Found unico air handler with amana outdoor heat pump. Found 2 amp fuse blown on unico control board in attic. Fuse is a special size but there was a spare fuse on the board. Went and checked over low voltage wiring and found out at outdoor heat pump low voltage high pressure switch wiring had rubbed against copper tubing and had a bare spot where it was arching against piping, this would cause it to blow small fuse at air handler. After replacing fuse and repairing shorted wire heat pump system came right on and is functioning again. Checked refrigerant pressures at outdoor temp of 39 degrees 410a pressures were 290/70.
Performed precision heat tune up on oil furnace. Aprilaire 401 air filter is ok. Checked all electrical conections and components. Replaced.75x70a nozzle. Replaced rf-1 oil filter. Checked pump screen. Vacuumed out soot inside furnace and at chimney base. Oil furnace is working fine at time of service.
Performed precision heat tune up on unico heatpump system. Replaced 14x30x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Performed ac check up, on high velocity system attic, check electrical low and high ok replace customer supplied filter 14x30x1 flushed drain ok check outdoor unit 410 pressures check capacitor and contactor ok super heat and sub cooling ok cycle unit ok