Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt did great. However being charged $160 extra on top of the $84 for the visit is totally unfair. And that is for a spliced wire. No parts or anything else. If that doesn’t get severely reduced, I will be looking for a different vendor. Because the trust will be broken.
Arrived on time, could not have been more professional, Excellent service. Thank you!
We have received excellent service from DiBiase Heating and Cooling Company. The administrative staff is friendly and professional and the service technicians are prompt, courteous and knowledgeable. I highly recommend this company to anyone seeking HVAC service.
Excellent service, kept me informed & very professional.
I called many heating companies to come out and check my unit but DiBiase heating within an hour called me back and got my heat working again. It's only been about an hour since they worked on it but my home is heated again with no problems. Thank you guys again for doing a great job. Definitely 5 star satisfaction rating.
Replaced both thermostats and also female adapters on inlet and outlet of water heater. Adjusted thermostats and tested temperature. No leaks present.
No hot water, found breaker in the off position, also cold water side shut off valve closed, cold water side shark bite connector is leaking pretty bad, water got into insulation and both thermostats have water, all connections are wet, ohm out both Elements ok, would recommend replacing both thermostats and replace shark bite with new copper/brass fitting quoted for repairs
Performed ac check up, on high velocity system attic, check electrical low and high ok replace customer supplied filter 14x30x1 flushed drain ok check outdoor unit 410 pressures check capacitor and contactor ok super heat and sub cooling ok Cycle unit
No ac found system off upon arrival,,,room temp is registering 78 set to cool 74 and unit came on check indoor blower ok temp split supply air 49 return air 74 check filter ok outdoor unit ok refrigerant pressures ok 200/75 cap and contactor ok cycle unit and unit came on with no issues
Performed ac tune up check electrical low and high ok flushed drain and test pump, pump making grinding noise and takes long time to discharged, check filter and quoted for replacement customer ok price, new high efficiency filter, check impose coil, lots of rust on copper coil, high risk on coil to start leaking, check outdoor unit refrigerant pressures only was able to check back pressure high side could not get reading capacitor and contactor ok cycle unit check temp split ok emailed quote to replace condensation pump
Performed ac tune up check electrical low an high ok filter ok check split, flushed drain test pump ok check outdoor unit refrigerant pressures capacitor and contactor ok cycle unit ok recommended adding ac renew due to previous compressor problem emailed proposal
Found unico air handler with amana outdoor heat pump. Found 2 amp fuse blown on unico control board in attic. Fuse is a special size but there was a spare fuse on the board. Went and checked over low voltage wiring and found out at outdoor heat pump low voltage high pressure switch wiring had rubbed against copper tubing and had a bare spot where it was arching against piping, this would cause it to blow small fuse at air handler. After replacing fuse and repairing shorted wire heat pump system came right on and is functioning again. Checked refrigerant pressures at outdoor temp of 39 degrees 410a pressures were 290/70.
Performed precision heat tune up on oil furnace. Aprilaire 401 air filter is ok. Checked all electrical conections and components. Replaced.75x70a nozzle. Replaced rf-1 oil filter. Checked pump screen. Vacuumed out soot inside furnace and at chimney base. Oil furnace is working fine at time of service.
Performed precision heat tune up on unico heatpump system. Replaced 14x30x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Performed ac check up, on high velocity system attic, check electrical low and high ok replace customer supplied filter 14x30x1 flushed drain ok check outdoor unit 410 pressures check capacitor and contactor ok super heat and sub cooling ok cycle unit ok
Had previously been onsite and found that Indoor Unit flashing a 2 Error Code. After troubleshooting with Technical Support, determined that the Indoor Coil and Room Temperature Thermistors had failed. Manufacturer recommended replacement of the Indoor Unit Control Board. At the time of the service call the second Indoor Unit was operating. Homeowner informed us 24-48 hours later that the second Indoor Unit was flashing a Code also. If the Second Unit is not operating properly it will require additional troubleshooting and diagnostics. 7-12-18 luis replace indoor control P.C. board, coil thermistor and ambient temp thermistor cycle and check split on u it ok supply 52 return 76 other head working ok no issues found at this time
Found Mitsubishi mini split system has 2 indoor heads connected to one outdoor unit. Found bedroom indoor head working perfectly fine and living room head flashing error code 2 on operation light. Called Mitsubishi tech support case number 443788. Found it to be open thermistor error code. They recommended rempalcing indoor thermisters and indoor control board to solve issue. Distributors are closed at this time will call tomorrow to get availability.
Found unit turned on and was running when homeowner turned on at thermostat. She described yesterday when she went outside hearing a humming noise, but nothing running. Pulled out 25/5 capacitor and tested. Found that capacitor was bad. Also found single pole 40 amp contactor was wearing out and was pitted. Recommend replacing both capacitor and contacter. Replaced and checked r22 pressures at 66 degrees were 153/59. System is back up and working fine at time of service.
Upon arrival everything worked ok filter #213 needed replaced I saw there was no saftey wired in for the condensate pump or an ez trap recommend replacing and adding eztrap upon further discovery noticed barcteria and mold growing from coil insulation, showed customer and recommended a reme left brochures. Delta t 18 degrees.
No heat oil furnace, found clogged nozzle, also electrodes need to get replaced, flat ends, will need new oil filter and strainer both items are very dirty almost clogged, quoted fore above repairs, customer ok, replce nozzle .75x70A new pump strainer, new RF-1 and set of new electrodes, purge oil line and check for leaks at oil filter and strainer ok, adjust air on burner, combustion test and Smoke test ok cycle heater ok check 401 filter ok