Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I always use these guys for Hvac needs. Techs were on time / quick / efficient / professional. Good group of guys.
Service call that the Gas Boiler was working but was making loud vibrating noises and swooshing sounds from the baseboards. Upon arrival turned thermostat up to turn system on to monitor. After system starting heating the baseboards could be heard making a loud swooshing noise due to air being in the lines. Also found Expansion tank was full of water. Isolated and Purged baseboard loop and drained Expansion Tank. Put system back in operation to test. Allowed system to fully heat up and cycle on/off. Monitored water pressure and temperature. Checked baseboards and all rooms were getting hot with no noises from the baseboards. Would recommend having Boiler serviced each year and would also recommend having the AC serviced before the summer time.
Returned to site to test Oil Boiler after Oil Delivery. System was in operation upon arrival and at Setpoint on thermostat. Turned Thermostat up to test operation. Measured 0.62 Amps on Circulator Pump. Checked Baseboards to ensure they were getting hot. Performed Combustion Test, Smoke Test, and Draft Test on system. Adjusted Air Band on burner due to improve combustion readings. Performed Smoke Test again after Air Adjustments were made. Ran hot water to ensure Aquastat was working with the domestic coil. Combustion Readings within standards upon completion. Cycled system upon completion.
Checked no heat complaint, found no call from thermostat, checked thermostat, found display flashing heat and fan. But no call to W. Jumped out thermostat. Furnace comes on and heats. Found a bad thermostat. Customer is going to replace the thermostat.
Performed heat tune up on Peerless oil boiler but we were stopped by an empty tank. Heat exchanger and flues are clean. Replace RF -1 filter and .75 80B. Tested transformer. Upon start up, while trying to bleed he pump we discovered the tank was empty. Informed homeowner to have oil delivered as soon as possible. M
Performed Precision Heating Tune Up on Gas Fired Trane Furnace. Checked High Efficiency Air Filter. Homeowner is going to order and replace Filter. Cleaned and serviced Humidifier. Setup humidifier for 35% and tested operation. Tested electrical components on Furnace. Cleaned Drain lines and condensation Pump. Removed and cleaned Burners and flame sensor and inspected Heat Exchanger. Performed Combustion Analysis on Furnace and measured Air Temperature readings.
Performed Precision Heating Tune Up on Ruud Gas Furnace system. Replaced 16x25x1 Air Filter. Tested electrical Components on system. Cleaned Flame Sensor and Ignitor Assembly. Inspected Burners and Heat Exchanger. Put system in heating mode and performed Combustion Analysis on Furnace.
Performed Precision Heating Tune Up on Gas Fired Furnace. Replaced 16x25x1 Air Filter. Inspected Electrical Components on system. Cleaned all Furnace Drain Lines and Tubing. Cleaned Condensation Pump on unit. Removed Burners and cleaned. Burners are rusting and visual inspection of Heat Exchanger shows rust along inside walls of Heat Exchanger. Put system into heating mode and performed Combustion Analysis on unit and measured Air Temperature readings. System operating within manufacturer standards at this time.
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Service call that the AC was not operating. Upon arrival set system to cooling to test. Found outdoor unit was intermittently coming on/off. Inspected Components and found Dual Capacitor had failed. Installed a new 35/5 Mfd Dual Capacitor to test system. Inspected wiring at outdoor unit to ensure it was in good condition due to signs of mouse presence in the control panel. Put unit in operation and System started and ran with no issues. Measured Voltage and Amp Draw on Compressor. Measured refrigerant charge on system. System is operating to standards.
Performed Precision AC Tune Up on system. Replaced 16x25x1 Air Filter. Cleaned AC Drain Line and Condensation Pump. Inspected electrical components on the Indoor and Outdoor Units. The dual capacitor is testing at its lowest recommended rating. Spoke with homeowner about replacing the Dual Capacitor. Measured refrigerant charge on system and air temperatures. Refrigerant levels were to standards at this time. Homeowner inquired about Duct Cleaning. Recommend using Mold N More Out of Exton: https://moldnmoredecon.com/
Performed cooling maintenance, replaced media filter. Cleaned condensate drain and pump. Shut off humidifier for summer. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed gas heat tune up check electrical low and high ok check filter ok clean sensor check blower cap ok split ok measure low and high stage ok combustion test cycle furnace ok
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Measured fuel pressures. Checked operation and temperature rise.
Performed Precision Heat Tune Up on system. Cleaned and serviced Humidifier. Tested Humidifier and set Control at 35% for the Heating Season. Cleaned Furnace and Humidifier Drain Lines. Cleaned and tested operation of Condensation Pump. Inspected all Electrical Components on system. Inspected Burners and Heat Exchanger. Performed Combustion Analysis on Furnace. Air Filter is starting to get dirty. Homeowner is going to purchase new Filter and replace. System is operating to standards at this time.
Performed Precision Air Conditioning Tune Up on System. Replaced Air Filter provided by Homeowner. Cleaned Drain Line and Condensation Pump. Inspected Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge on system. System is operating to standards at this time. Had previously recommended an Air Cleaner/Air Scrubber. With the Humidifier and High Efficiency Air Filter this would help to maintain the Air Quality in the Home.