Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
On time, explained options, completed the job without any issues!
Plan member AC Maintenance; 3 Ton communicating Amana AC system: Replaced Aprilaire 413 Filter Checked temperature split. Measured static pressure. Checked EZ trap; tested pump. Checked wiring, controls, electric motors and components. Both indoor and outdoor coil are in good condition. Checked refrigerant pressures and diagnostics. AC system is operating well at the time of this maintenance.
Heat Tune Up: 80KBTU Amana 2-stage gas furnace. Made call for heat from thermostat. Replaced humidifier pad and serviced humidifier. Replaced 16x20x1 Filter Measured temperature rise. Measured static pressure. Checked all controls, wiring, electric motors and components. Checked gas pressure. Verified flame sense circuit. Checked pressure switches and components. Inspection of burners, heat exchanger, and ignitor: Good Combustion/draft test: Good Homeowners became AC/Gas Heat service plan members. Furnace is operating well at the time of this maintenance.
Arrived to do oil maintenance, changed nozzle and oil filter checked combustion, vacuumed out heat exchanger and flue, checked smoke, checked water pressure and temperature. Everything is working correctly at this time.
Perform gas heat tuneup check electrical low and high voltage connections check air filter 413 OK Clean flame sensor checked gas pressure low and high stage performed combustion test also check airflow supply and return temperature 40Â° delta test condensation pump cycle gas furnace provided an estimate to install a whole house air purifier
Customer has issues with thermostat WiFi connections, thermostat goes offline every one hour, check thermostat internet connection and is very strong, replaced t10 thermostat under warranty, set up thermostat one heat one cool and also set up phone app and thermostat, if customer still having issues with internet connections would recommended upgrading modem.
Performed 6 month inspection on on recently installed unit check all settings ok replaced filter, check airflow and temps ok, check outdoor unit refrigerant pressures sub cooling and super heat ok cycle unit ok 235/110 with 6 super heat and 7 sub cooling supply air 42 return air 66
No heat, upon arrival found the off, set stat to heat and check operation, found blower motor not running, check motor cap and actual motor ok, found Burnt wire on delay board relay, new board is needed, hot wire blower motor, to get customer heat, check electric heat ok we will be coming back to install new board customer paid 50% 1-26-21 Luis installed new oem fan time delay board, check and test operation of electric heat back up and regular heat ok
We took the old furnace out and all connections to it. We also removed the old humidifier and all connections from that. Install new furnace and added a filter mount to the side and connect to return drop. Adapted new flu and intake pvc. Connected new condensation pipes to whole system including humidifier and drain boot. Ran new water line to humidifier and added a sharable valve. Tested out and went over new system with customer.
Replaced failed surge protector under warranty. Tested to ensure proper operation.
Thermostat only goes up to 70 customer set thermostat to 74 it never reaches 74, customer stated flames would come on but they would go out after minutes of running, found blocked on furnace trap, cleared blockage and test operation, propane as fuel source, secondary heat exchanger collector box is leaking, also needs new burners, also heat exchanger did not passed safety test, ran furnace with out blower for 4 minutes to get steady combustion once blower was energized excess air went up from 115% to 140% carbon monoxide only went up 3 ppm due to condition would recommended replacing furnace
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. Condensate drain proper and no leaks. Venting proper and secure. All penetrations sealed. Duct connections sealed. Outdoor unit and disconnect level. Did find surge suppressor incorrectly wired and took out surge suppressor. Did not have one on my truck. Need to return and replace under warranty. Customer moved the sensor before I got here to a new location and seems to be better upstairs now. Was having issues with the app but I believe it is the phone as it is an older phone. Customer is going to download the app to their newer tablet and try it and call me Monday to let me know if that fixed the issue. If it didnâ€™t fix it then we should also bring a new T10 thermostat with when we come to replace the surge suppressor. System running great at this time.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and flushed lineset. Placed new Amana condenser on pad and brazed in lineset with nitrogen. Wired in high and low volt connections. Installed new Amana high efficiency gas furnace and evaporator coil. Installed April aire media filter. Secured and sealed return and adapted supply ductwork and sealed. Ran new vents to exterior of home and tied into furnace. Brazed in coil with nitrogen and pressure tested to 300 psi then evacuated down to 129 microns. Installed new ez trap and condensate pump. Ran vinyl tubing to discharge. Wired safetyâ€™s to break r. Reconnected gas and leak checked. Installed new switch and receptacle. Wired all high and low volt connections. Installed horizontal drain kit on intake vent. Installed t10 thermostat. Tested operation in heating and cooling. Adjusted refrigerant charge and adjusted gas pressures. Performed combustion test. System working great at time of install.
Performed precision oil tune up on burnham oil boiler. Replaced rf1 oil filter. Replaced.75x80a nozzle. Cleaned and brushed out boiler and smoke pipe. Performed smoke and combustion test. Made sure both heat zones were getting hot. Oil boiler is working fine at time of inspection.
added refrigerant to system for system to work properly, added r22 to adjust superheat and sub coolin based on temperature , wet bulb, and humidity levels now system is working up to standards supply air 53 return air 74
No ac, found system off upon arrival set stat to call for ac, check airflow check split supply 63 return 76 check outdoor unit refrigerant pressures and found to be low on refrigerant, provided solutions to customer performed a leak search, add refrigerant or both, due to age and condition of system would recommended replacing system