Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision AC Tune Up on System. Replaced 16x20x1 Air Filter. Inspected Electrical Components on Indoor and Outdoor Units. Cleared Condensation Drain Pipe. Would recommend installing an EZ Trap to better clean the Drain Line. The EZ Trap would be wired to the system and if the Drain line clogged and tripped the Float Switch inside the EZ Trap it would shut power off to the system. Measured Refrigerant Charge on system. Refrigerant Pressures are fluctuating due to possible moisture and/or non-condensible in the system. System is cooling and refrigerant levels are within safe operating range.