Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Very nice job.
Kurt was professional, listened to my concerns and tackled the problem. Kurt also made suggestions for better performance in the future.
Very smooth. Fixed problem.
Luis had to climb into the attic and fish wire to the new themostat. Took the time to walk us through the setup of the wireless thermostat. Very professional and attentive to cleaning up after the job was completed.
Came at the time stated. He was friendly and spoke to us about the problem we were having. He went right to work. Told us what happened and showed us a broken wire that he replaced. We were thankful that someone was able to come on such a hot day.
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain and cleaned pump. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge. Checked operation and temperature drop across coil.
Performed cooling maintenance, checked air filter ok. Cleaned eztrap and drain. Checked voltage, amperage and electrical connections, measured capacitor values.started air conditioner, checked refrigerant charge. Checked operation and temperature drop across coil.
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain and trap. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge. Checked operation and temperature drop across coil.
Homeowner described that during recent windstorm house lost power for 2 hours. He tried resetting breakers. Found blown 3 amp fuse at air handler control. Replaced fuse and tested system operation. Made call from heat from honeywell Prestige IAQ stat. Checked filter. Measured temperature rise. Checked electric heat amps. System is operating well at the time of this service. Encouraged homeowner to become a Heating and Cooling plan member. Explained benefits, discounts and details of plan membership; Emailed quote.
Performed QA on Amana Heat Pump system. Reviewed installation with homeowner. Completed checklist form in system. Tested system in heat pump and auxiliary heat mode. This install passed the QA inspection. Only item that was addressed was the snow legs underneath of the outdoor unit were not under the unit completely. Was able to adjust the snow legs and reposition under the unit.
Installed new Amana heat pump and air handler. Installed new supply plenum with canvas connecter. Installed air handler on new 12in return box. Installed new Aprilaire 413 HE filter. Installed new return transition and canvas connector. Sealed all duct connections. Installed new 3/4 lineset. Installed new T4 thermostat Installed heat pump on riser legs and leveled pad. Installed new disconnect and whip. Pressure tested to 300 psi and evacuated below 500 microns. Installed new condensate pump ez trap and vinyl tubing to point of indoor discharge. Made all necessary high and low voltage connections. Tested condensate pump and tested system. System working properly. Install went over with customer, cleaned work area.
Replacement of water panel, cleaned canister and distribution tray, noticed lot of static on return, lowered water flow going to humidifier to prevent any leaks from humidifier cycle and test humidifier test condensation pump ok set humidifier to 35% No charge
I removed insulation from furnace exhaust piping. I was able to find the point where pipe is leaking. 45 fitting. For the time being I glued outside of fittings. Reinsulated pipe. Informed homeowner that the office will contact him regarding scheduling repair/repipe.
Found crack on heat exchanger and secondary is emitting a bad smell which happens when it is blocked up and has soot in it.
Humidifier leaking due to high static pressure sucking water off the humidifier pad. Second floor returns are not moving any air and system is working overtime to pull air from first floor and basement. Need to replace attic return duct work.
Perform heat pump tuneup/inspection check filter ok 20x20x1, test back up heat 39 amp on back up heater, check temperature rise on regular and back up heat, ok check blower capacitor and motor, found blower cap running just below standards, also noticed some mold inside air handler showed condition to customer, check outdoor unit heat pump, refrigerant pressures contactor and capacitor, capacitor is reading below standards, contactor is pitted, unit is from 2001 would recommend replacing system rather than trying to fix any issues. We will revise previous proposal and send an updated proposal for system replacement options.
Performed heating maintenance, replaced air filter, cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches. Performed combustion test and checked temperature rise.
Found blown 3A fuse. Traced out cause of short as being both the 240v 2 pole contactor and the 240/24V transformer. Replaced both contactor and transformer. Tested emergency heat and heat pump operation. Office to bill. System is operating well at the time of this service.
Installed 2 ton heat pump with electric back up, pressure tested ref. Lines to 300psi and held for 15 min, connected suppley duct and taped all corners, all electrical up to code and tested everything out, check all operations. Customer not home at time of completion, locked door behind us per customer.
Performed gas heat tune up on three gas furnaces. Replaced filters check electrical low and high voltage connections ok, cleaned sensor and burners check manifold gas pressure performed combustion test check temperature rise and blower motors ok, cycle furnaces, would recommended system upgrade on older fist floor system, found igniter reading below ratings and transition adapter is starting to leak, informed customer about first floor older unit and he would like someone to come out in Monday at 9 am.