Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt was professional, listened to my concerns and tackled the problem. Kurt also made suggestions for better performance in the future.
Very smooth. Fixed problem.
Luis had to climb into the attic and fish wire to the new themostat. Took the time to walk us through the setup of the wireless thermostat. Very professional and attentive to cleaning up after the job was completed.
Found 2005 York gas furnace locked out...code 3. Voltage to inducer 120 but Inducer motor was mechanically stuck. We freed the motor mechanically for now but need to get a quote for replacement of inducer motor. Will get back to customer with replacement quote.
Performed Precision Heating Tune Up on Amana Gas Furnace System. Replaced 14x25x1 Air Filter. Cleaned and serviced Humidifier. Cleaned Condensation Pump and filled pump to test. Vinyl tubing for the Condensation Pump is dirty and has buildup forming inside of it. Replaced the 3/8â€ Vinyl tubing for the Condensation Pump. Ran new tubing over to Sump Pump in closet under stairway. Filled Pump several times to ensure it was pumping out properly. Inspected electrical components on furnace. Performed Combustion Analysis and tested humidifier. Humidifier is set to 35% and dampers are open.
Performed Precision Heating Tune Up on Propane Gas Furnace system. Replaced 16x25x1 Air Filter. Inspected and tested electrical components on unit. Inspected Burners and Heat Exchanger. Burners have rust but channels are clear and burners are lighting off properly. Cleaned Drain Lines and Pressure Switch Tubing on unit. Furnace and AC Drains are separate but both empty into the foundation. Would recommend installing an EZ Trap on the AC Drain Line and a Wet Switch on floor between the drain pipes for water protection. Put system into operation and performed Combustion Analysis and measured Air Temperature readings. Combustion levels were within standards.
Checked no heat complaint, found thermostat set at 68 and itâ€™s 74 in the house. Raised temperature and furnace started and ran. Customer said that happened every time he changed the temperature. Set thermostat to hold and raised temperature. Explained thermostat and hold. Please schedule heating ptu $89.00
Performed heating maintenance, checked air filter ok. Cleaned burners and flame, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Performed precision heat tune up on 80% trane gas furnace. Homeowner just replaced 14x24x1 air filter. Checked all electrical conections and components. Blew out pressure switch tubing. Tested zone dampers for both zones. Checked gas pressure and performed combustion test. Checked temperature rise at gas furnace. Gas furnace is working fine at time of inspection.
Performed two ac tune ups attic and basement, replaced filters, flushed drain ok check temp split ok check blower cap and motor ok, check outdoor units refrigerant pressures 410a ok amp draw and voltage ok cycle both units ok
Performed cooling maintenance, checked air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Had previously been onsite and found 1st Floor System very low on charge. Performed electronic Leak Search on system and found a leak on the Indoor Aspen Coil. Ordered a replacement Trane Coil and returned to install. Reclaimed refrigerant and disconnected and removed old coil. Installed new Coil on Furnace and fabricated a transition between the Coil and existing ductwork due to new coil being 3â€ shorter than previous coil. Adapted Refrigerant pipes to new coil and brazed in with nitrogen. Pressure tested system with nitrogen to ensure it was holding pressure. Evacuated system to below 500 Microns and released refrigerant charge. Adapted Condensation Drain pipe to new Coil. Sealed all connections between the coil and ductwork. Replaced the 20x25x1 Air Filter. Put system in operation to test. Measured refrigerant charge and added a total of 7 lbs of 410-A charging by Subcooling/Superheat. While testing the AC, found the 70 Mfd Compressor Capacitor and the 7.5 Mfd Fan Capacitor were
Checked no cooling complaint, found unit short cycling on low pressure switch. Found unit nearly void of charge. Performed leak search, found leak on left side of coil. Need to replace cooling coil. Need aspen coil model Ace48d44210l015
Performed cooling maintenance, replaced standard air filters. Cleaned condensate drains. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners, checked refrigerant charge, found second floor air conditioner low on charge. Topped off air conditioner and balanced charge by superheat. Checked operation and temperature drop across coils.
Leak checked all connections. Pumped system down and purged with nitrogen while brazing leak shut. Pressure tested to verify fix. Evacuated system down to 148 microns. Released refrigerant and tested system. Found charge to be adequate. System running well at time of repair. 23 degree split.
Performed Precision AC Tune Up on Amana AC system. Checked 14x25x1 Air Filter. Filter was clean and did not need to be replaced. Cleaned AC Drain Line and Condensation Pump. Inspected Electrical Components on Indoor and Outdoor Unit. Checked humidifier to ensure it was turned off and damper closed for the season. Put system in AC Mode and measured Refrigerant Charge on System. Measured Air Temperature readings. System operating to standards during Tune Up.
Performed quality check and check no cooling. Checked air filter ok. Cycled furnace. Started air conditioner, outdoor unit short cycled. Found very low on charge. Leak searched system, found leak at 7/8â€ ell at the outdoor wall. Topped off charge for cooling until leak can be repaired.
Performed cooling maintenance, replaced standard air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.