Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt was professional, listened to my concerns and tackled the problem. Kurt also made suggestions for better performance in the future.
Very smooth. Fixed problem.
Luis had to climb into the attic and fish wire to the new themostat. Took the time to walk us through the setup of the wireless thermostat. Very professional and attentive to cleaning up after the job was completed.
Performed two ac tune ups attic and basement, replaced filters, flushed drain ok check temp split ok check blower cap and motor ok, check outdoor units refrigerant pressures 410a ok amp draw and voltage ok cycle both units ok
Performed cooling maintenance, checked air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Had previously been onsite and found 1st Floor System very low on charge. Performed electronic Leak Search on system and found a leak on the Indoor Aspen Coil. Ordered a replacement Trane Coil and returned to install. Reclaimed refrigerant and disconnected and removed old coil. Installed new Coil on Furnace and fabricated a transition between the Coil and existing ductwork due to new coil being 3â€ shorter than previous coil. Adapted Refrigerant pipes to new coil and brazed in with nitrogen. Pressure tested system with nitrogen to ensure it was holding pressure. Evacuated system to below 500 Microns and released refrigerant charge. Adapted Condensation Drain pipe to new Coil. Sealed all connections between the coil and ductwork. Replaced the 20x25x1 Air Filter. Put system in operation to test. Measured refrigerant charge and added a total of 7 lbs of 410-A charging by Subcooling/Superheat. While testing the AC, found the 70 Mfd Compressor Capacitor and the 7.5 Mfd Fan Capacitor were
Checked no cooling complaint, found unit short cycling on low pressure switch. Found unit nearly void of charge. Performed leak search, found leak on left side of coil. Need to replace cooling coil. Need aspen coil model Ace48d44210l015
Performed cooling maintenance, replaced standard air filters. Cleaned condensate drains. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners, checked refrigerant charge, found second floor air conditioner low on charge. Topped off air conditioner and balanced charge by superheat. Checked operation and temperature drop across coils.
Leak checked all connections. Pumped system down and purged with nitrogen while brazing leak shut. Pressure tested to verify fix. Evacuated system down to 148 microns. Released refrigerant and tested system. Found charge to be adequate. System running well at time of repair. 23 degree split.
Performed Precision AC Tune Up on Amana AC system. Checked 14x25x1 Air Filter. Filter was clean and did not need to be replaced. Cleaned AC Drain Line and Condensation Pump. Inspected Electrical Components on Indoor and Outdoor Unit. Checked humidifier to ensure it was turned off and damper closed for the season. Put system in AC Mode and measured Refrigerant Charge on System. Measured Air Temperature readings. System operating to standards during Tune Up.
Performed quality check and check no cooling. Checked air filter ok. Cycled furnace. Started air conditioner, outdoor unit short cycled. Found very low on charge. Leak searched system, found leak at 7/8â€ ell at the outdoor wall. Topped off charge for cooling until leak can be repaired.
Performed cooling maintenance, replaced standard air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed ac tune check electrical low and high voltage ok, replace air filter flushed drain test pump ok, check split, outdoor unit refrigerant reassures 410 contactor and capacitor clean outdoor coil recommended adding uv treatment gave customer options for air purifiers
No water protection in case drain backs up. Installed wet switch and explained operation of safety device. Also performed precision a/c tune up on trane a/c system. 14x24x1 air filter is clean. Checked all electrical conections and components. Homeowner talked about furnace making a clicking sound when it stops. Found that it was just the furnace cabinet, tightened screws around cabinet, nothing to. Be concerned about. Checked temperature split at indoor unit. Tested both zone dampers. Blew out condensate drain. Checked temperatures at indoor and outdoor units. Checked refrigerant pressures at outdoor unit. System is working fine at time of inspection.
Extend sump pump discharge pipe on the outside, pipe is under ground 3 inches and goes all the way to end of mulch bed, customer did not want leak detector,
Installed Aprilaire dehumidifier in unfinished part of basement. Electrical outlet existed. Installed a condensation pump and ran vinyl to discharge line sealed and caulked barbed fitting. Unit was set in pad on hp feet. Pump was wired in for saftey. Went over instructions with customer. Unit is running to factory standards. Replace and re pipe expansion tank as well
No heat first floor, blank thermostat blank, found first floor auxiliary pan full of water, noticed water leak was coming from secondary heat exchanger collector box, quoted for repairs, removed collector box and reapplied gasket, and replace screw, also empty auxiliary pan, test and cycle furnace after repair no leaks were found, recommended having both systems check out/tune up, customer ok performed two propane gas furnaces and service humidifier, replace filters, clean flame sensor, check manifold pressure ok combustion test cycle units ok both furnaces are working under manufacturer specifications would recommend at some near future adding ez trap for attic unit and upgrade first floor thermostat to IAQ THERMOSTAT to control humidifier from thermostat to read better humidity levels, noticed high humidity levels on basement, customer had had some mold/mildew would recommend attic problem before it becomes a big issue,
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor capacitor values. Started gas furnace, measured fuel pressures and performed combustion test. Checked operation and temperature rise.