Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that the Unit was making a buzzing noise after someone had backed into it. Upon arrival spoke with the homeowner about the issue. Was met onsite with the President of the HOA who informed me that someone had backed into the Lineset which runs along the interior wall of the parking garage. There was a metal casing over the Lineset which was dented and removed. Removed insulation from the Lineset and inspected the accessible area. Did not find any visible damage to the Lineset. Homeowner put system in Heating mode. Measured refrigerant charge on the system. Checked Voltage and Amp Draw on Compressor. Amp draw was within standards at 7.5 Amps on the Compressor and 0.5 Amps on the Outdoor Fan. System cycled several times during normal operation. Would recommend installing a new Dual Capacitor for the Outdoor Unit. Capacitor tested below rating. Spoke with homeowner about Replacement of the capacitor. They will call to schedule to replace at a later time.