Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I have had Nathan come to my house several times for service. He has always been friendly, courteous and professional. He explains everything and will repeat the information making sure I understand what he has said. He is very reliable.
Nathan and Chris were courteous and friendly. Aware of rain and making sure to wear their shoe covers.
Checked no cooling complaint, found outdoor unit not running, found no power to uni, checked for shorts, found a grounded compressor. Recommend replacing heat pump
Performed peco inspection, replaced very dirty air filter, tested electric back up heaters. Blew out condensate trap. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, heat pump doesnâ€™t start, found outdoor unit locked out on high pressure. Reset lockout, started heat pump, checked refrigerant charge ok lockout must have occurred from dirty filter. Recommend having unit maintained, $189.00 per year to join maintenance plan
Doing some boiler maintenance and mini split checks in Folsom
Hello Delaware County! Here in Folsom we are installing a Daikin Mini-Split System. This system has three systems running off of it. The upstairs bedroom has a 12,000 BTU unit, while the Living Room and Sitting Room on the first floor both have 7,000 BTU units.