Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Chris was great. Friendly extremely knowledgeable
Service call that the system was not cooling properly. Upon arrival found system running but unit was only cooling with a 10 Degree temperature split. Measured refrigerant charge and found system was low on refrigerant. Added 2 lbs of refrigerant to system, charging by Subcooling. Replaced 16x20x1 Air Filter. Inspected electrical components on system. Inspected indoor Coil and found indoor coil very dirty. After adding refrigerant temperature splits increased to 15-16 degrees. Due to the poor condition of the coil, would recommend removing the coil and cleaning and then retesting refrigerant charge again and adding any additional refrigerant. System is cooling but with the condition of the coil the system is struggling to maintain temperature and may continue to have issues keeping temperature on high heat/humidity days. Due to the coil condition did not add the leak dye into the system at this time. Will provide an estimate to remove and clean coil as well as to replace the indoor c
Performed Precision AC Tune Up on Goodman Downflow system. Replaced 16x25x1 Air Filter. Cleaned Drain Line and Condensation Pump. Pump was excessively dirty and the check valve had to be removed and cleaned for it to pump properly. Vinyl tubing also appears very dirty and could be forming blockages. While pump is working, due to being so dirty there is no guarantee that the pump will not clog internally again and fail to pump out. Pump does not have a safety float switch so if the pump fails to pump out it will overflow onto the floor. Inspected electrical components on indoor and outdoor units. Measured refrigerant charge and system is low on charge causing a higher superheat than recommended. System is cooling with a 15 degree temperature rise, but on high heat/humidity days the system may struggle to maintain temperature. Due to the overall condition of the system, the lower efficiency, and the age (15 Years) would recommend begin planning for replacement of the Gas Furnace/AC Sys
No ac, found blower running but no outdoor found open capacitor quoted for new one customer ok replace capacitor and test unit check r22 pressures 250/80 supply temp 63 return air 79 amp draw on compressor 9 could not verify with nameplate all faded also customer will replace filter
Performed Six Month Inspection on Amana Heat Pump System that was Installed in February 2019. Changed 16x20x1 Air Filter. Inspected EZ Trap to ensure it was clean and clear. Measured Refrigerant Charge on system. Due to extended length of Lineset, added 2lbs 8oz of 410-A Refrigerant to the System Charging by Subcooling/Superheat. Upon completion Subcooling was maintaining 8 Degrees and the Supply/Return Differential was at 16 Degrees. System is operating to standards at this time. Spoke with Homeowner about leaving Fan setting in Circulate to help move air in between the cooling cycles.
Service call that the Heat was working intermittently. Arrived onsite and spoke with the Homeowner about issue. Found Heat was running upon arrival, but after cycling the unit the Heat was working intermittently. Found Control Board Relays were not staying closed and were causing the Furnace not to run. Ordered new Control Board and returned to install. After installing new OEM Control Board turned System on to test. System was operating but then would shut down while running. Need to further troubleshoot system. Luis and Paul replc auxiliaryâ€™s blower limit and also found 12.5 blower cap running at 9.5 quoted for repairs customer ok also reduced gas pressure to 3.2 wc and combustion test, would recommend cleaning blower wheel and coil cycle and test heater ok
Finalized installation of 1.5 ton heat pump system with 5 kw backup heat. Installed additional return in 2nd bedroom and ran flex duct and connected to return air box. Inspected all wiring and connected wiring to EZ trap. Added additional insulation to supply runs. INstalled 16x20 filter in unit. Installed all supply air registers in ceiling 8x8. Installed thermostat. Powered systems up and tested operation. Measured and adjusted system charge, tested heat pump and backup heat operation. Provided homeowner with instructions on operation. Left system off for now. Looked at adding additional run for lower level rear family room. There is only one hole going through into crawlspace. Recommend removing 6â€ flex run and running 8â€ from trunk in basement with hardpipe through wall into crawlspace and splitting 8â€ into 2 6â€ runs and add another supply in room. Need to provide estimate on additional work.