Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Fast, efficient and answered all of my questions.
DiBiase is a great HVAC company. Their service is ALWAYS great.
This rating is based on the follow-up inspection as the unit was installed at the beginning of April. The unit has been running as expected without issues. I mentioned an area or two where I felt the unit was not quite proficient; however the technician went into the control settings and made and adjustment that has resolved the issue, and the unit has been working fine ever since. The technicians were the ones who installed the unit, and were great to speak with for both installation and follow-up. They were both personable and answered all of the questions I had; in addition, they allowed me to ask specific follow-up questions in order to get a better understanding of how the unit works and certain maintenance items. I have dealt with a handful of HVAC contractors in the area for both home warranty work, and when pricing out replacement units. DIBIASE was by far the most professional, prompt, and attentive to the needs of our situation.
Dibiase Heating & Cooling is all about keeping the client updated. Like the confirmation and reminders of appointments and the follow-up on the work completed with copies of the data and invoices. All the technicians are skilled and friendly. Thanks Dibiase.
Performed Precision Air Conditioning Tune Up on American Standard System. Checked 24x24x1 Air Filter. Filter was recently changed by Homeowner and in good condition. Found the Blower Motor Capacitor was testing below rating. Also found Double Pole Contactor was worn and pitted. Contactor was making a buzzing noise which indicates that the coil is becoming weak. Spoke with Homeowner about recommended Repairs. Provided estimate for repairs which were deferred at this time. Measured Refrigerant Charge on system. System is operating but due to age of system, 16 Years, would recommend to begin planning/saving for replacement of the Gas Furnace/AC system. Thank you for renewing your Service Membership with us today!
Performed cooling maintenance, checked media filter. Cleaned condensate drain and pump. Checked voltage, amperage and electrical connections, measured capacitor values, found compressor capacitor getting weak rated at 40 reading 38.4. Replaced start capacitor and relay. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed cooling maintenance on 2 ton air conditioner. Checked media filter itâ€™s good. Cleaned condensate drain and pump. Checked voltage, amperage and electrical connections. Measured capacitor values. Started air conditioner. Checked refrigerant charge and temperature drop across coil.
Performed precision ac tune up on amana ac. Replaced Aprilaire 413 air filter. Checked all electrical conections and components. Recommend installing an ecm surge protector on the indoor blower moter, homeowner to possibly install next service. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working well at time of service.
Performed heating maintenance on gas boiler. Cleaned burners, and pilot burner. Checked voltage,, circulator amperage and electrical connections. Measured fuel pressures. Inspected heat exchanger. Started boiler, tested limits and safety switches. Performed combustion analysis. Checked boiler pressure and temperature.
Found no surge protector on ecm moter. Installed surge protector. Performed precision ac tune up on amana ac. Replace Aprilaire 413 air filter homeowner provided. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Homeowner had got an error code a few weeks ago on the ecobee of hardware error code but then went away . Called ecobee tech and the said it might have been a power fluctuation if it only happens once and a while. They said it should be fine at this time. System is working well at time of service.
Performed precision ac tune up on American standard ac. Replaced 16x25x1 air filter. Checked electrical components and connections. Blew out condensate drain and tested pump. Found pump saftey not tied in and no ez trap installed on drain line recommended. Also checked refrigerant pressures and temperatures at indoor and outdoor units. Also found outdoor unit pad sinking and compressor a little noisy in its older age.
Performed precision ac tune up on carrier heat pump. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate. Checked all refrigerant pressures and temperatures. System is working fine at time of service.
Installed water heater, due to current water hester leaking, new water heater is Rheem 50 gallon natural gas power vented, installed expansion tank and also new 3/4 shut off valve, Also water heater seats on a pan with water sensor cycle and test new water heater ok
Performed ac check up, check electrical low and high ok flushed drain test pump ok, check filter ok, check split, outdoor unit 410a pressures ok sub cooling and superheat caps and contactor ok cycle wc unit ok
Performed ac tune up. Check electrical low and high ok replce filter flushed drain test pump ok, check split ok check outdoor unit 410 pressures ok capacitor and contactor ok cycle ac unit ok
Reset furnace and observed operation. Found furnace firing up and shutting down after 5 seconds. Tested flame sensor and removed and cleaned sensor. Tested operation. Recommend full thorough cleaning on furnace and removing and cleaning of blower assembly. No filter is installed on unit. Recommend installing filter right away. Filter size is 18x18x1. Pitch on vent pipe is incorrect and also the vent pipe is too close to drywall and needs to be corrected for safety . Drywall needs to be removed to assess what needs to be done to repair.
Service call that the Humdifier was leaking. Humidifier was turned off upon arrival. Turned Humidifier on and tested. Found Humidifier Panel was corroded and water was leaking over the top of the tray. Humidifier was cleaned and serviced in December. Hard water could cause the Water Panel to corrode prematurely. Cleaned Humidifier Tray and replaced Water Panel. Blew through Drain Tubing to ensure it was clear. Turned Humidifier back on and monitored. Allowed Humidifier to run for 10-15 minutes and found no signs of Water Leaking. If was leak occurs again, recommend replacement of the Water Panel Tray and Feeder Tube. If the Feeder tube cannot sit in the proper position on the top of the tray is it can cause water issues. Included an estimate for the Water Panel Tray and Feeder Tube for an Aprilaire 500 Humidifier.
Found no oil getting to bleeder so replaced very dirty rf1 oil filter also found .85 80 degree a nozzle all clogged up so replaced the pulled apart burner and found coupler rounded out so replaced and still no flow at oil bleeder , found bad oil pump . Had a becket clean cut oil pimp on the truck so replaced. Most of these issues were caused by lack of maintenance. Also after getting furnace running blower moter didn't sound real good starting up , furnace is getting pretty old and recommended getting a quote to replace.
We replaced the thermostat control with a new Redlink Pretige IAQ control with internet Gateway and outdoor sensor. We completed all wiring modifications to the system and setup and test all components to ensure proper operation.