Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Chris performed several tests to make sure all potential issues could be addressed. He was able to get the heater up and running so that we could at least have heat until we replace the unit.
Technicians arrived early, were friendly, completed work promptly and took time to answer questions and go over need to know info.
As always Luis was prompt, and professional. He did his annual cooling maintenance and also addressed a minor issue with the furnace. During the COVID-19 pandemic, he wore the proper protective gear and I just let him do his work. As always, a happy customer.
Kurt, Paul, Dave, Stephanie, Sarah & Joe are just the best. It's been my experience that they are highly customer-focused & regularly go above & beyond to ensure a quality experience for their clients. Can't say enough good things about DiBiase HVAC!
Luis was our technician. Because he has done much of the maintenance on our units after install, he is very familiar with our system. Luis is friendly, efficient and takes the time to listen to all of your questions and explain everything in detail. I've dealt with a number of different HVAC professionals as we used to have a home warranty company. Luis and the other DiBiase techs are significantly better than any of the other HVAC company's that serviced our older HVAC system.
Luis was the technician who serviced our Central Air in the spring, and serviced the furnace for the fall as well. Luis was prompt in his appointment window, friendly and answered all of the additional questions I had. Everyone from DiBiase has been very professional. Luis was great with offering little tips on what I can do as general maintenance in order to keep the unit running well into the future.
There was concern I smelled gas coming from an area right by my water heater. I called DIBIASE at about 10:30 AM thinking I would have a technician out the following day. The scheduler recognized the urgency of the situation and had a tech out the same day at 5:30 PM. The tech had been to our house before so it was nice to see a friendly face. He was able to diagnose the issue quickly and completed the repair quickly as well. The repair was completed in about an hour. As always, The tech was very friendly, personable and answered all my questions.
Fast, efficient and answered all of my questions.
Performed cooling maintenance, replaced standard air filter, cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Reclaimed and removed old coil and ac unit. Installed a new amana heater in existing location with an amana coil on top all new return ductwork and supply ductwork. Reinstalled humidifier. Cut in a new Aprilaire HE filter. Adapted to gas piping and ran a new condensate drain with a ez trap wired into unit. New pump and new vinyl tubing ran over to sump. Ran new electrical outlet and switch. Adapted to flue piping as needed. Ran new copper lines from indrooor unit to new amana ac unit. Amana ac is on a new plastic pad. With new disconnect box and electrical wiring to unit. Tested unit in heating and cooling.
No air conditioning, found system off upon arrival set thermostat to call for cool and check operation supply air 55 return air 66 check blower motor and cap air filter ok, check outdoor unit refrigerant pressures found to be high sub cooling and high super heat, pressures did not match corresponding PT CHART on manufacture specifications, removed bulb from suction new txv is needed
AC tune up for 2 Ton Ruud AC system. Filter ok. 29F temperature split. Tested condensate pump and tstat; ok. All electric motors and components ok. Outdoor voltage/compressor Amos/indoor amps ok. Both coils are in good condition. Refrigerant pressured/subcooling/superheat ok. System is operating well at the time of this maintenance.
Performed cooling maintenance, replaced standard air. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil
Precision AC Tune Up for 4 ton Fujitsu AC system. 22F temperature split. Replaced filter. Both coils are in good condition. Indoor amps/outdoor voltage/compressor amps ok. Refrigerant pressures/subcooling/superheat ok. Drain ok. Noticed humidifier tubing is abandoned and there is no saddle valve; provided estimate for repair.
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain. Inspected cooling coil. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Estimate is to remove expansion tank with compromised bladder and replace. 4/19/21. Installed new expansion tank and checked for leaks, no leaks found. Also performed 6 month inspection on amana a/c side. Tested condensation pump with water. Checked temperature split at evaporator coil. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of inspection.
Six Month Inspection. Will Return to replace sT-12 expansion tank and discuss plan option Monday 4/19.
Customer has not hot water, found pilot off upon arrival relight pilot and check operation ok, during same visit performed ac tune up, replaced air filter and flushed drain test pump ok, check temp split noticed only 10 degrees split, outdoor unit cycling on low pressure switch, check outdoor unit found open start start cap, also added some refrigerant for testing purposes, system is low on refrigerant, talked to customer about situation and she decided to not perform any repairs at this time emailed proposal for recommendations
Performed heating certification inspection, replaced air filter. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Replacement of oem nitride igniter low voltage. Cycled furnace. Combustion test; good. 55F temp rise.
Performed gas heat tune up, check electrical low and high, replaced filter, flushed drain test pump ok, cleaned flame sensor, ad check burners, found igniter with some wear, it about 70% life, would recommend replacement, emailed proposal for igniter replacement, service humidifier test and set to 35% winter, check low and high stages combustion test ok cycle unit
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system.
Reclaimed and removed old coil and ac. Removed old heater off return box and installed a new amana gas heater on existing return box and on top of a Aprilaire HE filter. Put amana coil on top and modified supply duct as needed. Ran a new electrical box and outlet. New condensate pump with new vinyl tubing ran over to discharge. New condensate piping with an ez trap wired in. Adapted gas piping as needed and leak checked with bubbles. Ran new copper lines from indoor coil to outdoor unit. Installed a new amana ac unit in a new plastic pad with rocks underneath.