We are applying the second application of our rubberized duct lining material to all of the heavily rusted underground duct work.
We are cleaning all the underground duct work and applying our trenchless cast mortar to restructure all the weak rusted metal duct work with holes allowing the backfill under the slab to enter the system blowing dirt and sand into the home. We are also sealing the entire underground duct work with 2 applications of our rubberized duct lining material to completely seal the system leaving a nice clean and efficient air flow quality.
Homeowner is experiencing heavy amounts of white dust being blown in house when the furnace is on. Televised ducts under slab floor. Ducts are spiral wound metal ducts that are rusting and deteriorated. Suggest spin cast mortaring ducts then spray lining ducts with Duct Armor duct lining material
Televised ducts under slab floor. Ducts are pvc with metal fittings. There was slight standing water in the one run. Metal is showing slight signs of rust. Gutters look like they need to be cleaned as water is sheeting over next to the building during rains. Once water is resolved the ducts should be spray lined with Duct Armor duct lining material to rebuild rusty metal and encapsulate the pvc for possible mold.
Televised ducts under slab floor. Ducts are pvc ducts with metal elbows and fittings that are showing signs of rust. Inspection outside shows downspout on side of house needs to be extended. Water is pooling next to house on side. Grading on side and front can also be raised slightly to help water flow away from the house. Ducts should be spray lined with Duct Armor duct lining material to encapsulate pvc and cover rusted metal.
We are lining a section of 6” clay tile sewer which has heavy roots growing in at each joint.
We are lining a 6” clay sewer that has many leaking joints allowing water to seep out and overwhelm the sump pit and pump during heavy rains, we are lining 81’ of 6” clay from and outside clean out near the house all the way out to the city main.
Lined the 4” clay sewer that ran under the crawl space 22’ to new PVC pipe outside of the house. The pipe was getting heavy root growth in joints of the old clay tile, the liner will prevent the roots from growing into the sewer causing back ups.