The guys did a perfect job, clean efficient,no issues and fast.
Response from Trenchless Innovations Inc.:
Thanks for leaving us such a wonderful review. We are glad that you loved our services, our dedicated staff will be pleased to learn of your high praise.
Duct repair service call. Underground ducts were in rough shape from home settling. Installed liner and used video inspection to confirm damage was repaired.
Under slab ductwork video inspection service call. Televised ducts under slab floor. Ducts are PVC with metal fittings that are severely Rusted and deteriorated. There is also a duct located next to the furnace that is collapsed and needs to be dug up and replaced. After replacing that duct then the ducts should be spin cast mortared on the joints then spray lined with Duct Armor.
Sewer liner installation service call. Inserted a 4-6” liner through the existing overhead clean-out extending downstream approximately 70’ feet ending past the clean out in the front yard. Reinstated cleanout in front yard.
Air duct inspection service call. Televised ducts under slab floor. Ducts are PVC ducts with metal connections. Some of the metal fittings are very rusted. There was standing water in ove section leading to the master bedroom and there was also signs of possible mold. Air duct repair recommended. Suggest spin cast mortaring metal then spray lining entire system with Duct Armor duct lining material.
We are applying the first application of our rubberized duct lining material to all of the heavily rusted underground duct work.
Lined a section of 4” cast that was shifted at the foundation wall
Televised ducts under slab floor. Ducts are pvc ducts with metal fittings. Metal fittings and plenum are extremely rusted. There was no standing g water in the ducts at the time of the inspection but the house does have a higher than normal humidity level. It is suggested that all downspouts around the building be extended away to help reduce the amount of ground water that may be raising up into the ducts. After the water issue is resolved the ducts should be spin cast mortared on the connections to restore the structure then the entire system spray lined with Duct Armor duct lining material.