We are applying the second application of our rubberized duct lining material to all of the heavily rusted underground duct work.
We are applying the first application of our rubberized duct lining material to all of the heavily deteriorated underground duct work. The air ducts will be completely sealed and the air in the home will be safe for the customer to breathe.
We are repairing all of the heavily deteriorated underground air ducts with our Trenchless cast mortar process. This process involves spraying a mortar slurry on to the rusted elbows and connections to give them a strong structure. We will then apply two applications of our rubberized duct lining material to all of the underground air ducts. This will completely encapsulate them and sand will no longer blow out of the air vents.
Televised ducts under slab floor. Ducts are pvc with metal fittings and connections that are allowing sand into ducts. There had been water in ducts from previous events. Some downspouts need to be extended. After that the ducts should be spin cast mortared and then spray lined with Duct Armor duct lining material.
Televised ducts under slab floor. Ducts are PVC. Water is getting into system near the elbow going up to the furnace at the lowest point. The drain tile that was installed was not installed deep enough. Waterproofing company needs to install a drain tile from furnace area leading to the sump pit to lower the water table.