I love My new furnace and air conditioning.
I was impressed with the professionalism and response. The technician was well manered and very informative. I will be using LBA for my repairs in the future.
Pressure cleaned approximately 80â€™ of main sewer from 4â€ access behind first set of machines, camera of line determined that first 10â€™ of pipe is pitched backwards towards c/o causing back ups when everything is running at same time. Line is open and flowing at this point. Also cleaned from 2â€ floor drain in mechanical room 50â€™ and tested. Cleaned up work area.
Camera 4â€ line from a stack c/o in restroom, found no obstructions in line up to 78â€™, line is open and flowing at this time. Also cabled toilet same restroom, line open. Recommend jetting of 2-4â€ lines from behind washers and camera for inspection. $556.00 and needs scheduled for Thursday morning 7:00 on May 14. 4 hrs.
Lennox air conditioning tune up spring check
Boiler tune up and repair.
Carrier furnace tune up.
Air conditioner is shutting on and off. Charging Lennox equipment
Cleared floor drain
Repair full air conditioning system
Performed professional all inclusive furnace tune up.
Check heat pump contactor on Armstrong unit stuck on in in Grain Valley
Check for 1st floor system not heating heat pump. found r22 leak refrigeration on the indoor coil. set up for system design specialist to visit with this customer.