I love My new furnace and air conditioning.
I was impressed with the professionalism and response. The technician was well manered and very informative. I will be using LBA for my repairs in the future.
Performed heating tuneup, and installed IWave R Air purifier. Cleaned and removed all debris off burner compartment and electrical wires. Performed combustion check on heat exchanger. Checked temperature rise. System is running with a manufacture specs at this time
Installed parts from previous invoice.
Performed furnace diagnostic. Found a fault in the combustion pressure system. Customer approved a basic combustion pressure sensing system renovation. Was able to get the customer heating temporary, office will call and schedule a return visit to install the part. Thanks for choosing lba, Eli.
At time of arrival found flame proofing system was reading below manufactures specifications and causing the furnace not to run. Cleaned up flame proofing system and system is running within manufacturers specs at this time. Customer wanted to purchase the Iwave R system and would like it to be installed once we are out here for the furnace maintenance.
Today I completed your annual cooling tune up. I tested all indoor operations. Tested temperature split and checked filter. I tested all outdoor operations. Checked refrigerant and cleaned outdoor system. Found that drain line and pan were excessively dirty. Recommended having air scrubber plus installed. Everything else tested as it should at this time. Thanks for having me out today, Eli
Customer had Back up in floor drain over the weekend after arrival on site tested drains themselves and lines are open and flowing properly at this time. Gave customer option to clean out line itself and customer wants to wait, also noticed leak on hot side line of water heater, water heater itself is nine years old giving estimates for replacement of water heater and or water leak repair.
Pressure cleaned approximately 80â€™ of main sewer from 4â€ access behind first set of machines, camera of line determined that first 10â€™ of pipe is pitched backwards towards c/o causing back ups when everything is running at same time. Line is open and flowing at this point. Also cleaned from 2â€ floor drain in mechanical room 50â€™ and tested. Cleaned up work area.
Camera 4â€ line from a stack c/o in restroom, found no obstructions in line up to 78â€™, line is open and flowing at this time. Also cabled toilet same restroom, line open. Recommend jetting of 2-4â€ lines from behind washers and camera for inspection. $556.00 and needs scheduled for Thursday morning 7:00 on May 14. 4 hrs.
Lennox air conditioning tune up spring check
Boiler tune up and repair.
Carrier furnace tune up.
Air conditioner is shutting on and off. Charging Lennox equipment
Cleared floor drain
Repair full air conditioning system
Performed professional all inclusive furnace tune up.