Nathaniel did a great job for us. Thanks LBA.
Doug was great, has skills
Nathaniel was on time, explained options and quickly corrected the problem.
Eli was totally professional, polite, courteous, friendly
Exhaust fan for kitchen was not removing air from kitchen. I got on the roof and Inspected the exhaust fan and I found the belt was so worn and old it had broke. I bought a new belt and replaced the old one turned on the fan and it is operating properly at this time.
Replaced control board under warranty
Completed furnace tuneup, high-voltage wiring and low-voltage wiring landed at ports and stable in Firm. Performed a combustion check on supply, no CO found in supply line. Performed combustion motor checked, combustion motor is running to manufacture specification. Blower motor running a normal amps. Performed heat exchanger check after truly Evaluating the heat exchanger no cracks found at this time. Will take a look at heat exchange again next year. Cleaned all safety switches and recalibrated. This system is performing and running to manufacture specification
Checked all operations in the heating mode. Performed a combustion analysis on furnace. Cleaned out housing of furnace and housing of humidifier. Replaced furnace filter and left 3 extra furnace filters. Replaced humidifier pad and set humidifier to proper specifications also found that the voltage enhancement system was to be operating out of factory specifications. Customer chose silver repair allowing me to get the system back up to optimal specifications. System is heating properly at this time.
Arrived to find system not operating. Due to the control system has failed. Showed customer options. Customer chose bandaid option. Performed all work under the bandaid option. Performed safety testing to ensure system is operating properly. Unit is heating at this time.
***air movement fault/motor bearings worn allowing shaft to have side to side movement*** I performed a safety and maintenance inspection on the furnace. During my inspection I discovered a fault within the air movement system. The motor bearings are worn to the point the shaft is allowed side to side movement. There isnâ€™t any noise during operation at this time but I did explain to the customer that if they hear any squealing or grinding noise that is when the air movement motor has failed and could cause more damage to other components. The customer didnâ€™t want to make any repairs today as they felt that due to the age of their equipment they would rather put money towards new equipment versus making repairs to the existing equipment. Thank you
Upon arrival found that the water distribution valve had failed. System does have a limited manufacture warranty which was credited towards repair. Made bronzer repair by replacing the water distribution valve and tested system afterwards. system is now operating within factory specifications.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and tested humidifier, found that solenoid valve was not operating correctly, customer wanted to wait to have furnace and humidifier replaced at the same time. performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Upon arrival found that the fan setting was higher causing a louder noise checked all operations system is heating properly at this time.
Both furnace were locking out due to high limit. We raised the fan speed and let the systems run. The temperature dropped bet 8 and 10 degrees. If the systems continue to lock out we will need to cut in a larger return.
Arrive to find pilot out in garage unit. Relit pilot light. Perform safety testing to ensure system is operating properly. Unit is heating at this time.
Found that customer did not switch thermostat to emergency heat, advised to switch to emergency heat when it is under freezing
Found that thermostat batteries needed replaced, Changed batteries and system tested as it should
Performed a full heating inspection. Cleaned indoor unit. Checked all wires and safety switches. Performed heat exchanger inspection. Heat exchanger passed all test. Unit is operating within factory specifications at this time.
Completed silver combustion blower install, recommended having maintenance performed on system and heat exchanger inspected