On time and very complete service.
I have always been impressed w the professionals that work for LBA. I was very pleased w my service today.
So far I am pleased but I am still not finished until tomorrow.
Appreciated the depth of knowledge and willingness to be candid and complete in sharing information.
Errol was very thorough, he biagnosed our issue and got our system backup and running.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, found that 1/4 turn valve to humidifier was leaking and recommended replacement. Customer declined at this time. everything else tested as it should at this time, thanks for choosing Lba, Eli
Performed maintenance inspection on a Lennox furnace. Checked all the electrical components and safeties for proper operation. Performed combustion analysis and serviced humidifier. Furnace is currently operating under manufacture specifications.
Whole house plumbing inspection Customer has nine-year-old heater with no thermal expansion tank or pressure regulating valve. Incoming pressure is at 80 psi. Recommend repair/replacement 1. Toilet in main guest bathroom 2. Kitchen faucet 3. Water filtration system in line 4. Water heater replacement
Arrive to customers home Thursday, September 24. Customer having issues with dishwasher in kitchen. Customer said the dishwasher was not filling previously and was making abnormal noise. Had customer run dishwasher while in home. Dishwasher appeared to fill and drain normally with no odd noises or functions. Remove Bottom cover of dishwasher while at home and could feel hot water and pressure in supply line as well as see water dumping in disposal in kitchen sink. Plumbing to and from dishwasher is functioning properly. Dishwasher is functioning properly at this time. Thank you for choosing LBA have a wonderful day.
Arrived to customers home September 24, 2020. Customers concern about kitchen faucet. Kitchen faucet leaking while in use from handle. Kitchen faucet is single handle Moen brand Fossett roughly 20 years old. Customer chose to repair kitchen faucet. Replaced faucet cartridge and tested thoroughly to insure leak was repaired. Kitchen faucet is now functioning properly with no leaks from handle. Hot side of kitchen faucet has lower pressure but customer informed Plumber that was a previous issue and they were OK with that. Repair of kitchen faucet will have 30 day warranty on cartridge itself. Thank you for choosing LBA have a wonderful day.
Ran camera in sewer. Could not get to wall from floor clean out. Cast rot has caused the bottom to be gone. Cannot tell how far problem goes. House is on a foundation drain. Homeowner is going to call Johnson County Wastewater for sump pump program. Where line is this will fix a portion of the rot.
Filled back new concrete sidewalk with dirt by removing wood frame for concrete pour. Also added seeding.
Replaced customers 40 gallon natural gas water heater with new Rudd 40 gallon natural gas water heater. Installed new shut off on water heater as well as new thermal expansion tank. Installed new main shut off for home and pressure regulating valve as well as ball valve to isolate pressure regulating valve. Opened tile in upstairs hallway bathroom tub/shower. Replaced old three handle tub/shower valve with new Moen Posi temp shower valve. Replaced waste and over flow trim as well. Left valve trim with customer to call into company when tile is finished and trim will be installed free of charge. All products installed today will have 1 year warranty through company. Thank you for choosing LBA have a wonderful day
Performed maintenance inspection on both Lennox furnaces. Checked all the electrical components and tested all the safeties. Cleaned out furnace cabinet. Performed combustion analysis on both furnace flu. Replaced water panel with customer provided water panel. Did discover a gas leak in one of the gas shutoffs. Customer approved repair on fixing gas leak. Both furnaces are operating under manufacture specifications.
Customer has two outside hydrants leaking from handle and front outside hydrant is leaking behind brick but not inside house. Customer also has older lavatory faucet in Guest bathroom by kitchen, noticed customer does not have emergency stops company will have to stub in new waterlines from basement. Went over options with customer and customer wants to take a couple days to think over estimates and contact us if he wants to proceed with work itself. Thank you for choosing LBA and have a wonderful day.
Arrive to home Monday, September 21. Garbage disposal in kitchen sink leaking from base of disposal. Non-repairable. Customer chose Band-Aid level garbage disposal. Installed insinkerator badger 5 1/2 hp disposal in kitchen sink. Ran water and filled sink 3 times and ran disposal to insure no leaks present. Disposal is now functioning properly with no leaks on any joints under sink. Company will honor 30 day warranty on disposal itself. Thank you for choosing LBA have a wonderful day.
Replaced sidewalk today to a finished grade, will return Friday to pull forms and rake out yard and light seed.
Tenant was not home just the kids and they are both under 18, will need to reschedule once tenant is home or the property owner
Performed heating tuneup on furnace. Did not service humidifier. Inspected air filter and was still clean at this time. Inspected all electrical components and electrical wires. Performed combustion check on heat exchanger. System is running within manufacturers specs at this time. Checked indoor temperature rise. Customer renewed p3 membership
Upon arrival customer took me to upstairs Jack and Jill bathroom where the toilet had overflowed. I augured toilet and flushed multiple times. No warranty on toilet auger