Doug was on time! Very professional and courteous. He cleaned up after the service and was careful to bring in any snow or outside debris. He cleaned his shoes and wore booties inside. I am very pleased. Please have someone call me about changing my service contract to the service he explained. I feel like I got great service and a fair price for the work. This customer is very pleased,
Needed same day service to avoid the potential for freezing pipes. They were out within 4 hours and solved our problem immediately.
Totally satisfied with the work done. Very happy customers.
Upon arrival customer took me to master shower that was dripping, recommended a repair at this time versus replacement which would consist of cutting into Sheetrock and would have to be repaired. This is a Moen posi-temp faucet. Also offered P3 service agreement, she stated she uses another company at this time.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
I performed a safety and maintenance inspection on the FY5BNF036 carrier electric air handler system and heat pump. During my inspection, I discovered a fault within the air movement system. As I was feeling the blower motor shaft to test the motor bearings, I noticed that the motor was able to move much more than it should be allowed. There was one of the four legs to the motor mounting system that was missing its fastener. I looked within the air handler cabinet and I wasnâ€™t able to find the missing bolt. Furthermore, the blower wheel was found to be in poor condition. There was quite a lot of dirt/debris buildup on the wheel which prevents the air movement system from moving the adequate amount of air that it is intended to move. The blower wheel also has corrosion forming which isnâ€™t uncommon for electric air handlers. I recommended to the customer that we replace the blower wheel at this time versus just cleaning it because with the corrosion present, the wheel will pick up th
RTU#4 serial number nfkm069209 had the heat exchanger, and blower contactor replaced today. I also tightened the blower belt and tested the unit under heating. The unit is heating as designed at this time.
Arrived on site to diagnose 2 panelbloc heaters. I started to diagnose both heaters but then I found both had failed heat exchangers. Customer wanted quotes for replacing both units so i gathered information.
Upon arrival I spoke with pat he informed the IT room unit was not cooling at all. I began to diagnose the unit and I found the system was low on refrigerant. I added some r-22 and let the unit run, it began to discharge colder air and wasnâ€™t cycling on and off of low suction pressure. I performed a leak search on the indoor coil and I wasnâ€™t able to find a leak. With the sleet that were having right now I canâ€™t perform a leak search on the condenser. I finished charging the system back up with r-22 to get cooling for mean while. We will need to return when itâ€™s not raining and so windy to finish performing a leak search. I donâ€™t know how long this system will continue working.
Upon arrival investigated system and found that the system was shutting off due to ignition control failure. After investigating system found that the left two burners had cracks in the exact spot that they typically crack at. Found cracks by investigating with heat exchanger Duracurve special mirror. This furnace unsafe to operate. I Turned the furnace off and informed customer to not operate the furnace.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time on both systems, thanks for choosing Lba, Eli
Upon arrival the toilet in the upstairs was of and needed to be reset. I fixed the flang by putting a riser on it and rest the toilet after. I tested by flushing gallons of water down and looked for any leaks. Everything tested good. Also in building 6126 that they own right behind the building I just worked in the customer wanted a trip lever in the warehouse bathroom toilet to be replaced as well.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed humidifier tune up, performed combustion analysis, checked for proper heating transfer, changed humidifier panel, everything tested as it should at this time, thanks for choosing Lba, Eli
Found that ignition system had failed, was unable to make repairs on system due to not having parts
The unit heaters are all tied into one thermostat, the batteries were dead I used customer provided batteries.
Found that exhaust blower drain removal system had been plugged causing safety to trip, customer went with bandaid repair, after repair was mad everything tested as it should at this time.
Performed a full heating inspection. Checked all wires and safety switches. Cleaned indoor unit. Unit is operating within factory specifications at this time.
Upon arrival, the customer informed me that their Ruud U96VA furnace system wasnâ€™t operating. After further investigations, I discovered that the furnace had a fault code of 57 high pressure switch open with inducer motor on high speed. I cycled power to the furnace and the furnace operating without faults. I took combustion readings and pressure readings and found all to be within the manufacturers tolerances. I spoke with the customer about my discoveries and offered to waive this evenings trip charge if they wanted to sign up for a P3 membership. The customer chose to purchase a P3 membership. I instructed the customer to call in to the office tomorrow to schedule their furnace tuneup and their plumbing tuneup as the customer had questions about some plumbing accessories for their home and would like to get a cost on those accessories. Thank you