He had to snake kitchen drain three times before it worked. He kept at till it worked
He was friendly and very professional
Every thing perfect
Kevin is very polite, I am sure new customer's will welcome his expertise along with his knowledgeable offerings while evaluating the problem.
Diagnosed the problem and stayed with the project until it was repaired.
I was having a problem with a noise in part of my humidifier, and Jesse immediately identified the cause and solution. All the LBA employees I have interfaced with over the years have been polite, respectful, and knowledgeable. They know what they are doing and work quickly and efficiently.
Checked the power burner for the paint booth for no heat with the flame safeguard in alarm. Found the falt history of internal failure and jumpers changed with the jumpers undisturbed. Replaced the module. Verified operation after repairs.
Customers kitchen line was backing up into the sink. I cabled the line out through the sink and everything tested good. Can't warranty work that was done today.
Found system that was not operating had a tripped wet switch. Reset switch. Checked temperature split on system. 20 degree split on system. System pressures are not at factory specifications due to indoor system filters are clogged. Customer is aware filters need to be changed. Systems are up and running at this time.
Finished the pma on Mercedes Benz storage building. Washed out the condensers checked amp draws,capacitors, contactors, temp splits. 2- York rtuâ€™s and one York split system, one mini split are operating properly at this time.
Call was hand washing sink behind the counter faucet not shutting off and dripping. I shut off water at stops and pulled cartridges Cartridges need replaced. Reinstalled old cartridges. And ordered new. Came back 7/26 with new cartridges and installed. Checked operation . No leaks and operating well
Restrooms in jag/Land Rover parts depth were backing up , I opened cleanout in menâ€™s room floor and cabled drain line , was unsuccessful , i checked multiple cleanouts with camera and found all lines holding an employee said there was a 2nd pump system across the driveway in the other building , willie an I checked pump system and found breaker in main panel tripped and pumps not functioning, I turned the breaker on the pumps both to hand mode , pumps tripped out again , reset breaker and only used 1 pump in hand mode , and alternated them , both pumps work good individually , I called liberty and they informed me there needs to be 2 - 230v lines coming into that box for pumps to properly operate , I turned off pump 2 and left pump 1 in auto . Electrician will need to remedy this issue for pumps to properly operate again .
I found several issues with the air conditioning system, the main issues is the compressor has open windings. The system is 32 year old I suggest replacement. No money has been collected
Trap arm for 3 bay sink is broken out of sani tee in wall , i got permission and opened wall in dining room , in removed bad sani tee , and installed new one , i ran new trap arm to 3 bay drain and left support piece under trap , tested all functions , all are ok . 3 bay sink faucet is dripping from behind sink, and hand sink behind register is dripping as well . Would have to pull out 3 bay sink in order to repair faucet , and will have to order parts for hand sink to repair .
Replaced bad sump pump under warranty , customer still need to have dedicated circuit ran to sump , said she has electrician coming during this coming week . Tested new pump all ok .
Arrived onsite to look at York rtu that serves the parts warehouse not cooling. Upon investigation of the unit I found the main control board flashing an alarm code for supply air vfd failure. I then checked the vfd and found it in an error code. I then reset the vfd and watched the unit cycle on properly. After watching the unit cycle on and run properly I then spoke with cfm tech support and they stated that the supply air vfd will flash the error code when the blower motor is over amping. They then had me check the amp draw of the blower motor I found it reading 2.3/3.6 amps at full speed which is within range of the ratedamp draw. After finding this they stated that the unit appears to be running properly and this possibly could have been caused bye a power surge but if the issue persists then we may need to look into the vfd possibly failing. The unit is now running properly with a 20Â° cooling split at this time. This will not be billed any labor due to the unit still under the f
Installed new sump pump and water heater. Customer will be responsible for electricity to be ran over to pit.
Estimate for sump pump and water heater
Called out for rtu8 smoke alarm fault. No issue found at the unit. I advised the customer contact the fire alarm company and have them verify proper operation on their end.
Customer has P-trap drain that goes into the wall under the three basin sink. It has been hit that it because the connection in the wall to break the seal. I was able to re-seal it currently the customer does not want to cut in the wall at this time to do a more permanent replacement. I did explain to the customer that this will probably happen again but the next time I do suggest we do the mechanical connection to prevent future issues. Currently everything is leak free at this time.
Checked the West paint booth for no heat. Found the Honeywell flame safeguard failed. Customer ordered the replacement control yesterday. Customer will install the control themselfs and call if more repairs are needed.