He was friendly and very professional
Every thing perfect
Kevin is very polite, I am sure new customer's will welcome his expertise along with his knowledgeable offerings while evaluating the problem.
Diagnosed the problem and stayed with the project until it was repaired.
I was having a problem with a noise in part of my humidifier, and Jesse immediately identified the cause and solution. All the LBA employees I have interfaced with over the years have been polite, respectful, and knowledgeable. They know what they are doing and work quickly and efficiently.
I found several issues with the air conditioning system, the main issues is the compressor has open windings. The system is 32 year old I suggest replacement. No money has been collected
Trap arm for 3 bay sink is broken out of sani tee in wall , i got permission and opened wall in dining room , in removed bad sani tee , and installed new one , i ran new trap arm to 3 bay drain and left support piece under trap , tested all functions , all are ok . 3 bay sink faucet is dripping from behind sink, and hand sink behind register is dripping as well . Would have to pull out 3 bay sink in order to repair faucet , and will have to order parts for hand sink to repair .
Replaced bad sump pump under warranty , customer still need to have dedicated circuit ran to sump , said she has electrician coming during this coming week . Tested new pump all ok .
Arrived onsite to look at York rtu that serves the parts warehouse not cooling. Upon investigation of the unit I found the main control board flashing an alarm code for supply air vfd failure. I then checked the vfd and found it in an error code. I then reset the vfd and watched the unit cycle on properly. After watching the unit cycle on and run properly I then spoke with cfm tech support and they stated that the supply air vfd will flash the error code when the blower motor is over amping. They then had me check the amp draw of the blower motor I found it reading 2.3/3.6 amps at full speed which is within range of the ratedamp draw. After finding this they stated that the unit appears to be running properly and this possibly could have been caused bye a power surge but if the issue persists then we may need to look into the vfd possibly failing. The unit is now running properly with a 20Â° cooling split at this time. This will not be billed any labor due to the unit still under the f
Installed new sump pump and water heater. Customer will be responsible for electricity to be ran over to pit.
Estimate for sump pump and water heater
Called out for rtu8 smoke alarm fault. No issue found at the unit. I advised the customer contact the fire alarm company and have them verify proper operation on their end.
Customer has P-trap drain that goes into the wall under the three basin sink. It has been hit that it because the connection in the wall to break the seal. I was able to re-seal it currently the customer does not want to cut in the wall at this time to do a more permanent replacement. I did explain to the customer that this will probably happen again but the next time I do suggest we do the mechanical connection to prevent future issues. Currently everything is leak free at this time.
Checked the West paint booth for no heat. Found the Honeywell flame safeguard failed. Customer ordered the replacement control yesterday. Customer will install the control themselfs and call if more repairs are needed.
No hot water
Installed two new American standard champion toilets that the customer supplied. Also install two new shut off valves for both toilets
Gas line repair
Ac tune up for customer trane unit in highland crest park neighborhood