He had to snake kitchen drain three times before it worked. He kept at till it worked
He was friendly and very professional
Every thing perfect
Kevin is very polite, I am sure new customer's will welcome his expertise along with his knowledgeable offerings while evaluating the problem.
Diagnosed the problem and stayed with the project until it was repaired.
I was having a problem with a noise in part of my humidifier, and Jesse immediately identified the cause and solution. All the LBA employees I have interfaced with over the years have been polite, respectful, and knowledgeable. They know what they are doing and work quickly and efficiently.
Upon arrival the customer informed me that there was water leaking from their furnace system. After further investigations I discovered that at the end of the condensation drain line was a 3â€™ piece of vinyl hose that was pulled up to be out of the way. With the end of the line ran vertically, it prevented the condensate from the furnace to exit the end of the drain line and the condensate was escaping through the gravel trapâ€™s lid it being the path of least resistance. I pulled the vinyl hose down near the floor drain and the backed up condensate immediately flowed out of the drain line as it was meant to. Additionally as a courtesy to the customer, I flushed water down the evaporator and furnace drain lines that both connected to one drain line to ensure the issue was resolved. During my inspection, I noticed no evidence of regular preventive maintenance being performed on the equipment so rather than treating this as a drain line flush repair I offered the customer the option of
Checked into faucet issue , found that cold cartridge was chattering , found cold water stop not fully opened , I opened stop fully and tested all functioning ok . Checked into water heater issue again in Porsche building , found element blown again , eemax will not warranty heater , we will order new unit and replace when it ships in . Removed old eemax heater , and installed new heater of same model# , tested , heater is working good at this time .
This estimate is to rebuild 2 Watts 009 Backflow preventers and retest units Returned to rebuild backflow but couldnâ€™t shut off water during business hours . Rebuilt both backflows , retested, all yielded passing results . Will send passing reports to water one .
Performed semi-annual inspection, replace air filters, check wiring connections, test motors and capacitors, test heating operations. The south thermostat needs batteries replaced. The customer will take care batteries.
Tested carbonater backflow And feed to bar , both backflow yielded failing results and will require a rebuild , will attach an estimate to rebuild both units .
Checked the power burner for the paint booth for no heat with the flame safeguard in alarm. Found the falt history of internal failure and jumpers changed with the jumpers undisturbed. Replaced the module. Verified operation after repairs.
Customers kitchen line was backing up into the sink. I cabled the line out through the sink and everything tested good. Can't warranty work that was done today.
Found system that was not operating had a tripped wet switch. Reset switch. Checked temperature split on system. 20 degree split on system. System pressures are not at factory specifications due to indoor system filters are clogged. Customer is aware filters need to be changed. Systems are up and running at this time.
Finished the pma on Mercedes Benz storage building. Washed out the condensers checked amp draws,capacitors, contactors, temp splits. 2- York rtuâ€™s and one York split system, one mini split are operating properly at this time.
Call was hand washing sink behind the counter faucet not shutting off and dripping. I shut off water at stops and pulled cartridges Cartridges need replaced. Reinstalled old cartridges. And ordered new. Came back 7/26 with new cartridges and installed. Checked operation . No leaks and operating well
Restrooms in jag/Land Rover parts depth were backing up , I opened cleanout in menâ€™s room floor and cabled drain line , was unsuccessful , i checked multiple cleanouts with camera and found all lines holding an employee said there was a 2nd pump system across the driveway in the other building , willie an I checked pump system and found breaker in main panel tripped and pumps not functioning, I turned the breaker on the pumps both to hand mode , pumps tripped out again , reset breaker and only used 1 pump in hand mode , and alternated them , both pumps work good individually , I called liberty and they informed me there needs to be 2 - 230v lines coming into that box for pumps to properly operate , I turned off pump 2 and left pump 1 in auto . Electrician will need to remedy this issue for pumps to properly operate again .
I found several issues with the air conditioning system, the main issues is the compressor has open windings. The system is 32 year old I suggest replacement. No money has been collected
Trap arm for 3 bay sink is broken out of sani tee in wall , i got permission and opened wall in dining room , in removed bad sani tee , and installed new one , i ran new trap arm to 3 bay drain and left support piece under trap , tested all functions , all are ok . 3 bay sink faucet is dripping from behind sink, and hand sink behind register is dripping as well . Would have to pull out 3 bay sink in order to repair faucet , and will have to order parts for hand sink to repair .
Replaced bad sump pump under warranty , customer still need to have dedicated circuit ran to sump , said she has electrician coming during this coming week . Tested new pump all ok .
Arrived onsite to look at York rtu that serves the parts warehouse not cooling. Upon investigation of the unit I found the main control board flashing an alarm code for supply air vfd failure. I then checked the vfd and found it in an error code. I then reset the vfd and watched the unit cycle on properly. After watching the unit cycle on and run properly I then spoke with cfm tech support and they stated that the supply air vfd will flash the error code when the blower motor is over amping. They then had me check the amp draw of the blower motor I found it reading 2.3/3.6 amps at full speed which is within range of the ratedamp draw. After finding this they stated that the unit appears to be running properly and this possibly could have been caused bye a power surge but if the issue persists then we may need to look into the vfd possibly failing. The unit is now running properly with a 20Â° cooling split at this time. This will not be billed any labor due to the unit still under the f