Polite and went right to work
LBA is always all about great service
I was very satisfied with Nathaniel Reece's work. He did a great job.
Noah did all he could but ultimately a specialist was required.
Orientation of Sewage Ejector was incorrect.I rotated sewage ejector to where float was on the far side of Pitt. I checked operation of ejector and system operating normally. I disinfected area around both floor drains and everything that came in contact with water. A small inflatable kayak got damp as well. Customer agreed to disinfect kayak.
Checked all operations in the heating mode. Replaced pure air filtration system. Cleaned out housing of furnace and housing of humidifier. Replaced humidification pad. Also replaced drain lines due to drain lines being corroded and clogged. The drain line service was completely complementary for a good customer discount. Performed a combustion analysis and the furnace is operating safe and properly at this time.
Changed Warehouse RTU filters.
Change out filters on all RTUS
Checked all operations in heating mode. Performed heat exchanger inspection. Found heat exchanger to be intact at this time. Customer does not use humidifier that is un operational. Replaced filter with customer supplied filter. Customer still has a leak coming from the bathroom through the floor. Furnace is heating at this time.
Completed heating maintenance checks and changed filters. Verified mini split operation and cleaned filters. All units functioning at this time
Performed heating tuneup on furnace. Replaced air filter with new one off the van, I highly recommend replacing every month left customer estimate for a box of 6-20x25x1 filters. Checked temperature rise. Performed combustion check on heat exchanger. Inspected all electrical components and electrical wires. System is running within manufacturers specs at this time
Installed a 4â€ double pattern c/o on back side of building and Hydro-scrubbed approximately 100â€™ towards front of property, line is open and flowing at this time. With camera found a solid grease blockage back into building towards restroom. Installed gavel. Customer is responsible for backfill.
While on site customer ask if tech could replace an heat only thermostat, tech replaced thermostat than check operation of heating mode , everything is working ok
One time price for monthly a filter change on on (6) 25 ton rooftop units. This can be scheduled monthly.
1-20-21 Verified 6 New York RTU filters. Changed filters for office Lennox RTUs only and one split system for offices.
Arrive to customers home Tuesday, January 19. Customers master bathroom Jacuzzi tub faucet constantly dripping as well as hot side handle in misaligned angle when shut. Customer chose to have both cartridges of hot and cold valves replaced. Made quick trip to supply store and picked up proper parts for repair. Return to home and shut off water. Removed cartridges from both hot and cold valves. Replaced with new delta brand cartridges. Removed paneling on Jacuzzi tub to access valve itself. Was able to turn valve body to proper position so hot outside handle we close and open in proper angle. Re-tightened valve body onto body of tub. Turn water back on to home and tested both hot and cold. Both hot and cold valves are now working properly with no leaks and are closing in proper alignment. Company will honor six month warranty on both hot and cold cartridges of Jacuzzi tub. Thank you for choosing LBA have a wonderful day
Augured toilet in room 217. Cleared restriction. And checked operation. Restriction caused by size of stool and lack of flushing .
Upon arrival customerâ€™s icemaker line was not functional. I showed customer options to replace stop for ice maker. He chose a Band-Aid option with a 30 day warranty. Are you please stop and check for leaks and operation.
Estimate for jetting