We’re continually impressed and thankful for the excellent you provide to us. Noah did the work this week and he really did a tremendous job with all of the leaky faucets, shower head and replacing a gas line valve. Our hot water pressure is the best it’s ever been since we moved in 6 years ago! The pressure is seriously night and day better so he really cleaned things up. Noah was polite, respectful and communicated well. It was evident he knew what he was doing.. Plus, my wife hasn’t been comfortable with most repairmen who we’ve used over the past 13 years or so. But you all keep sending over quality people who do great work so I was able to work in my home office knowing that my wife wasn’t uncomfortable. In addition, you all are easy to work with from the scheduling to notifying me when someone is driving over. Thank you!
Jose Perez did an excellent job and very satisfied with his services at my home.
We had LBA replace the furnace, humidifier, A/C, and hot water heater in one day. They did a fantastic job. Quoted with excellent price on Monday and completed by Wednesday. Financed for 36 months no interest which took maybe 5 minutes on my prone. Guys could not have worked harder, explained everything clearer or cleaned up better. They’ll be servicing everything at the house from now on. Great experience.
Efficient prompt service
Austin and Noah were very thorough and took the time to explain our recurring plumbing problem that other companies never solved. After their attention to detail and expertise, we are confident we will not be dealing with the same problem and will recommend LBA to our friends and family!
Upon arrival pressure assist commode in womenâ€™s ada stall was continuously running. Replaced pressure assist cartridge and tested for proper function.
Upon arrival manager took me to the water heater where there is fluid beneath. I took a flashlight and crawled underneath water heater and around water heater. I could not see an active leak. Water heater is a 2007 making it 13 years old. Water heater is reaching age of replacement. I suggested to manager that they clean thoroughly underneath and around water heater. And if the fluid reappears to call us and we will Set up a time for replacement. Iâ€™ve written down serial number make and model and taking pictures on iPad for possible replacement information.
No heat, trouble-shoot unit and found gas valve shut off and wiring for W1 and W2 been remove so a heat call was never process, so I inspected both heat exchanger for crack, stage#1 heat exchanger checked ok I was able to wire stage#1 back to normal and everything is working properly Stage#2 have a small crack in the heat exchanger , it will remain disable until heat exchanger is replace, I explained everything to the customer and he like to have a quote for repairs Lennox #3 Model- KGA180S4BS2G Serial- 5614E13084
P3 Furnace Maintenance Tuneup- Inspected thermostat, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Performed humidifier maintenance, replaced water pad, cleaned drain line and inside of humidifier, humidifier is set for the winter. All heating ops are normal at this time.
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I changed your air filter and cleaned flame safety system. Everything tested as it should at this time
Upon my arrival both boilers had display service is needed, basically a timer that need to be reset, After resetting the timer checked operation of boilers and supply temperature both are working properly Boiler#1- serial# 1839 112032119 Boiler#2- serial# 1839 112032120
Arrived at customers house Tuesday, October 27. Customers concerns in home being upstairs master lavatory faucets both right and left side faucets dripping from handles and or spout. Master bathroom shower constantly dripping. And key valve for fireplace needing to be replaced tagged by gas company. Customer chose to replace both master bathroom lavatory faucets with customer supplied faucets And to repair master bathroom shower faucet as well as replace key valve for gas to fireplace. Replaced both lavatory faucet and pop-up assemblies in master bathroom and replaced customer supplied shower valve cartridge in master bathroom shower. Replaced fireplace key valve in basement and added new union to easily replace valve if needed. Tested newly installed faucets and shower for leaks and proper function. Newly installed faucets are working properly with no leaks and same with shower valve. Key valve for fireplace gas is now functioning properly tested thoroughly for leaks and proper func
Found that humidifier water pressure was turned up too high causing it to leak water. Adjusted water pressure and everything tested as it should at this time
Checked all operations in the heating mode. Performed a combustion analysis on furnace. Cleaned out housing of humidifier and housing of furnace. Found the high temperature safety system to be tripping at this time at improper temperatures. Replaced failed component upon customers request. Tested all operations. Furnace filter is OK at this time. Replaced humidifier pad. Furnace is operating properly at this time.
Arrive to replace all four burners to allow the system to operate safely and light properly. Cleaned up housing of furnace and tested all operations. Furnace has had major water damage but is operating properly at this time.
Completed the indoor portion of full heating maintenance.
Performed planed maintenance as contract states. All systems are running at factory specifications at time of departure. Nothing further at this time.
Customer complaint of noisy RTU, found loose belts, tightened loose belts and greased shaft bearings checked operation of fan motor amps everything seem to be working ok All work was service on RTU#1 model- KGA210S4BH2G. Serial-5614B01692
Upon arrival found pressure sensing system had condensation inside of it from an issue with the flue pipe. As well as found the burner to be extremely rusty not allowing the system to properly combust system is 17 year old and in very poor shape. Sent customer a repair quote. Customer is going to try and repair themselves.
Inducer trap is clogged causing water to back up in the system, quoted customer cost on this repair, due to the customers maintenance for the furnace Tune up is scheduled for the first week of November, customer will wait to have the repair done during the furnace Tune up.