we had a clog but don't have reliable drawings of our facility. Phil did a survey of the building noting drains and looking for access points to the drainage system. Took 7 hours but he finally found the issue and resolved it.
The plumbing check was thorough and provided options for repairing potential problems. It was very helpful to have a review of the entire plumbing system.
I was impressed by the quality of service and the fact the technician found a small gas leak in our system - which was quickly fixed.
I think the charge of $129.00 to come and do nothing is ridiculous.
Am totally satisfied with the service provided!
DO NOT USE
This estimate is to replace menâ€™s and womenâ€™s locker room toilets . Each handicap stall will get an ADA compliant power flush toilet and the other stalls will get a standard elongated power flush toilet . This cost doesnâ€™t include and flange repairs if needed , we wonâ€™t be able to tell that until toilets are pulled . Expect each toilet to take 1.5 - 2 hours to pull and reset new toilet . Old toilets will be taken away from property and trashed unless customer wants to keep them . Menâ€™s room left stall , replaced broken flange . Menâ€™s room right stall , repaired broken flange Womenâ€™s room left stall , replaced broken flange Womenâ€™s room right stall , replaced flange that was just set in pipe too high . Installed 4 new pressure assist toilets , install included new wax seal, closet bolts, supply line , seat . Tested functions of all toilets , all working great at departure .
Obsolete equipment, the repair parts needed are no longer manufactured. We will be in contact about a replacement quote
I replaced the high limit that I dropped into the duct work. I tested the unit and burned off the heat exchanger.
Made sure water shut on an off went thru without issues .
Preformed planned maintenance inspections on one RTU and 12 unit heaters. The RTU is working 11 out of 12 UH are working properly, however UH 11 is not operating due to a faulty sequencer. The supply store is closed right now. I will build a quote in the morning.
Checked the second floor IT room for too warm this morning. Found the room being cooled by two LG portable units with one supply register from the building heat and cool system. Closed the supply register to prevent heat supply to the room from the building system. Advised the customer to remove the two unused egg crate returns from the room and replace them with ceiling tiles to help seal the room. Verified the two LG units were cooling normal.
Checked the Northeast York Rtu serial N1C6474540 for no heat with no power supply the the thermostat. Found the smoke detector in the return section tripped. Reset the detector and verified operation. Shut the unit down and removed the sampling tubes. Cleaned the tubes. Reinstalled the tubes and verified operation. Noted the repairs to the customer and advised if the detector trips again that I recommend replacing the detector.
Upon arrival found Ptac unit not operating. Chased electrical wiring to outlet. Customer was informed and is aware they need to call an electrician to fix supply voltage to system.
We removed the old heat exchanger that had failed and replaced it with a brand new one. We were not able too turn the unit back on due to we broke the high limit switch. I will return on Monday once the part store when part stores are open to install the new high limit switch and burn off the heat exchanger.
I created a equipment replacement form. Parts that are needed for repair are no longer available.
Estimate for sump pump and pit Estimate for log lighter Estimates include all discounts from P3 agreement
Performed cpma on all equipment. Changed filters and checked all electrical and mechanical functions. Unit heater 1 and 2 will need further diagnoses by service technician. All other systems have nonissues at this time
I found the blower wheel shaft to be broken damaging the scroll cage, blower wheel, both bearings, both brackets, and the heat exchanger case. Also the cover separating the heat exchanger and the inducer has a hole rusted through it and will need to be replaced. I am waiting on parts pricing to get a estimate worked up. I will e-mail a estimate as soon as possible. Depending on the price of the repairs we may wan to replaced the roof top unit.
Performed the preventive maintenance for the heating season. I checked the amp draw of the blower motor and inducer motor, I made sure that the blower wheel and belt were in good working condition, I took readings of the capacitor to make sure that it was within the manufacturer's recommended tolerance, I looked over the heat exchanger to make sure there were no cracks or holes, I took a temperature split reading and I changed the filters.