Was very friendly and informative, I would recommend them to anyone
Good maintenance and service but a little pricy.
Friendly and explained everything to me.
He was very professional very courteous we we both felt he was a very good plumber Yelp
Jerry (tech) arrived on time, was respectful and worked hard in the hot attic to get my AC up and running. he called later to verify that all was in order. All in all I was very pleased.
I have used LBA for many years and plan to continue.
AC went out. Called, arrived the next day. Repaired, had it up and running by 6pm.
The only problem I had was when Michael came to the front door he said he was there to service my furnace. He was reading this off his tablet so when I made the appointment to have my air conditioner maintained they got it wrong he immediately changed his tablet and came in and maintained my air conditioner with great service
Apartment 4008 C had a low temperature split and I found it to be under charged on refrigerant. I added 1 lb or R22 and now the unit is cooling properly with a 20degree temperature split. One thing I did notice is that the return temperature is higher than the apartment temperature. This means we are getting return air from other spaces than the apartment that is being cooled. I found the return vents to not have actual ductwork and it is just pulling air down between the wall studs. This is probably pulling air from above the ceiling. This is not s new issue and most likely all of the apartments were built this way but this will make it hard to get down to low temps on hot days. Apartment 4021 C had no temperature split. I found a leak in the liquid line right outside of the condenser. I repaired the leak them pressure checked it. I then pulled a vacuum and charged the unit with 4.5 lb's of R22. After charging the unit to the proper superheat it still had a slightly low temperature sp
Moved gas lines for Zach s
Disconnected the electrical lines and refrigerant line set. I just it down to the roof but was not able to pull it into the space below.
Opon arrival I found condenser #5 shut off at the disconnect out back, this is one of the three u its that coils the treatment area. I spoke with Brian and he told me it was turned off two days prior and he turned it back on. So someone must be turning it off. So I would keep an eye on it and if it keeps happening we should get a lock put on all 6 of the disconnects. After I turned the unit back on it was working fine. I found the unit that coils the back offices and the break room to have a supply duct that had fallen off. This duct was the only supply to the break room. I reconnected the duct and tested this unit, it is working as designed. Unit #6 was completely empty on refrigerant and had been since at least August 5 because that was when we did our maintenance here and we made an estimate to check this unit for a leak. That's what I did today. I found the leak on the liquid line right where it goes into the furnace at the evaporator. I repaired the leak, pressure checked it, vacu
Gave estimate to install new backflow assembly.
Purchase Order: 3600090156
Upon arrival 4008 apartment A was cooling properly at this time. I found multiple issues causing the unit not to run properly. The blower leads had melted off, the compressor lead had melted as well. I also found the system low on refrigerant again. Recommended that the system be completely replaced due to age and how many issues Its currently having
Upon arrival tenant stated her a/c was not working again. After inspecting the unit I found very small amount of condensation had gotten in the secondary drain pan and happen to hit the wet switch directly. I dried off the wet switch and set it on a raided rubber pad. Unit is operating properly at this time
I arrived to check out 4008 apartment A. The key i was giving could not open the apartment, and the office did not have any other key to get in. Just charging a trip charge. Shannon said she would call us back out when the key was sorted out
We performed the preventative maintenance today. We washed the coils, changed the filters, and checked electrical components. We found 3 repairs and the quotes have been created and sent
We performed the preventive maintenance today. We washed all condenser coils and economizer filters and replaced all filters. We checked amp draws, temp splits, bearings, capacitors, belts, and wiring connections. All units are operating this time. Rtu-3 needs a new ax46 belt and (2) 10 mfd capacitors. I created a quote for those repairs.
I arrived to find there was little airflow coming out of the vents but the room temperature was at 73 and the thermostat was set to 73. After further inspection, I found that the furnace blower housing was cracked. The housing is no longer available from the manufacturer so I added bracing to the blower housing and secured the blower motor bracket to the housing. The blower motor and blower wheel are now in the right position and the furnace is producing more airflow now. I also washed the blower wheel since it was packed full of dirt and debris which is also causing a low airflow issue. The temperature split across the evaporator coil is at 20Â°. The system appears to be operating properly at this time.
Performed the scheduled light cooling inspection. We changed filters and checked cooling operations-ok. Both systems are operating within factory specifications.
Upon arrival customer took me to the kitchen faucet which was leaking from under side of valve. After discussing options Ken chose bandaid replacement. 30 day warranty. Installed new moen faucet and checked operation.
Replaced sump pump backup battery wet cell to dry cell maintenance free owner supplied. 30 day warranty labor only.