Friendly and explained everything to me.
He was very professional very courteous we we both felt he was a very good plumber Yelp
Jerry (tech) arrived on time, was respectful and worked hard in the hot attic to get my AC up and running. he called later to verify that all was in order. All in all I was very pleased.
I have used LBA for many years and plan to continue.
AC went out. Called, arrived the next day. Repaired, had it up and running by 6pm.
The only problem I had was when Michael came to the front door he said he was there to service my furnace. He was reading this off his tablet so when I made the appointment to have my air conditioner maintained they got it wrong he immediately changed his tablet and came in and maintained my air conditioner with great service
Very professional and polite. Great price too
Angelina was very friendly and explained everything she was doing and why. Very pleased with the work and the experience. Punctual and fast work.
I appreciated Kent listening to what I thought my problems were. I appreciated he gave me different options and let me choose the option I wanted. He fixed my problem in a reasonable amount of time. He was pleasant.
Kent was very courteous and professional. My concern deals with the pricing model LBA is using. I supplied the new part, so all they supplied was the expertise and time (< 1 hour). Even with a $50 off online coupon my bill was $208. That seems a bit high to me. I had a friend who will be needing a plumber, but I can't recommend LBA due to this "one size fits all" approach.
Lobby toilet clogged , augured toilet and tested, all flowing ok now
Began insulation on building 117 and adding filter doors will need to return next week. FOUND unit 200 bldg 1419 not cooling properly. Meter device has been adjusted, unit is now cooling properly. Services conducted are covered under warranty.
Performed a full coin inspection. Washed and cleaned outdoor unit. Checked all wires and safety switches. I also performed a mini split inspection. All units are operating within factory specifications at this time.
Upon arrival.Talked to landlord and diagnosed main line issue. Prepared options and explained the 89.00 would be applied to the option she chose. She wanted to talk to my supervisor. I contacted Pat. They talked. She declined to pay .89.00 trip charge.
Carrier and Lennox RTU Systems not cooling properly. Found outdoor coils to be dirty with debris not allowing for proper airflow. Also found indoor filters filters dirty. Coils have been split and washed of all debris. Air filters have been replace. Unit have been checked for correct charge. Unit cooling properly at this time.
Upon arrival tenant in apartment 4001 c states that over night theba/c is not able to keep up wonâ€™t go below 76. I inspected the unit and found that part of it was frozen up and it was thawing out. The system is low on refrigerant again, Cody was out here June 18th and added refrigerant and recommend a leak search be performed. The exact same thing has happened again leak search needs to be done to find the leak and the condenser is old, doesnâ€™t have a electrical components cover so all the electrical is exposed to the elements. And there is no disconnect for the condenser. The filter needs to be replaced it was very dirty.
Conducted a light maintenance on 6 units. All filters have been changed. All deficiencies have been quoted for repairs.
Estimate for new tub
AC unit for computer room found to have a frozen evaporator coil, dirty outdoor condensing unit, and low on charge. Evaporator coil has been dried out. The outdoor condensing has been washed of all debris to allow for proper airflow. Unit has been charged with (3) lbs of r22. Unit is operating at the correct pressures and temperatures at this time.
Made repairs to the system replacing the voltage enhancement system that had nothing to do with the original repair. Covering under warranty even know this has nothing to do with our previous work. If we have to return again charges will be charged.
Arrive to find exhaust removal system not operating due to a component failure. Motor was still under warranty from Band-Aid repair. Replaced exhaust removal system under warranty. System is cooling at this time.
AC unit was found to have a frozen evaporator coil. The unit can not be worked on at this time. Will need to wait 24 hours for ice to melt to further diagnose issues.
Arrived to find units not operating due to a wiring fault. Showed customer options customer could not afford options. Unit is not cooling at this time.
Found that condenser fan motor had failed, customer went with bandaid option
Found that thermostat was on the wrong setting causing it to turn the heat on when set to cool