The tech was knowledgeable and friendly
I was told my humidifier was up and running, it was not and then the same problem happened this year that happened last year I can’t afford $200 every year for humidifier to be repaired. I’ve canceled my LB a maintenance agreement for next year I won’t be using LBJ again
I have used LBA for many years each repair person has been very good
Great guy very plesent and courtesy to the upmost👍👍👍 up
Always trust LBA’s opinion / assessment of the situation! Long time customers
I diagnosed water heaters and prepared estimates
Completed monthly filter change.
Annual P3 furnace inspection. Performed combustion analysis, cleaned furnace, checked all components for reliability, checked temperature difference across furnace and performed heat exchanger inspection. Heat exchanger has a crack in it. Blower motor making loud noises on startup and the run capacitor tested weak. We talked about repair options, Scott is on site to give options for updating system.
Ran camera in sewer. Line has one problem at transition. Estimate to repair. No guarantee for stoppages line has a known issue
Upon arrival mainline had backed up into basement floor drain. Ran full cable. An obstruction was hit at approximately 15â€™ and roots were brought back on cable. Kitchen sink also overflow on my visit. Customer declined to have it cleared at this time.
Arrive to customers house Tuesday, January 5. Customers main sewer drain clog. Open clean out And snaked drain roughly 35 feet to clear blockage. Had customer run faucet and toilet drain was completely clear. Drain is now open and flowing properly. Drain opening will have no warranty. Thank you for choosing Iâ€™ll be a have a wonderful day.
Performed full heating preventative maintenance on one carrier unit, checked all electrical and mechanical components, changed all filters. Unit is operating within factory specifications no repairs required
Perform maintenance inspection on a hot water boiler. Checked all the electrical components and safeties for proper operation. Clean the burners and checked combustion. Boiler is currently operating under manufacture specifications.
Assisted with preventative maintenance on 3 split systems. Kellan billed for this job
Performed full heating maintenance on two air handlers with electric heat strips and one gas furnace. Checked mechanical and electrical components, temperature rise, and changed filters. Gas furnace is not currently in use as there is no gas hooked up to the building. Two electric air handlers are working at factory specifications at this time.
Upon arrival customer stated that she electrically shocked her thermostat due to static electricity. Found bad thermostat. Replaced thermostat with a standard thermostat upon customers request. Spoke with customer about a humidifier to prevent this issue and to improve the indoor air quality. Customer was unable to purchase the humidifier at this time. Emailed customer a quote for this.
Estimate for new water heater. Water heater installed incorrectly. 3â€ flue to long per flue and gas code and not enough make up air. Furnace has red tag for make up air from 2008. We will not got to manufacture for warranty even though it is a RUUD because of improper install
Customer has new Undermount sink that was installed in kitchen and needs plumber to drop drain stack and consolidate two sanitary tees to one. Installation includes drains, strainers, garbage disposal, and company is going to install faucet as well for no additional charge. Material list Pvc 2 inch hard coupling 2 in San tee 2 fernco P trap 1-1/2 2 Top extension arm 1-1/2 P trap T Company returned on December 22, 2020 and installed customer provided faucet,strainers, and garbage disposal. Company also cut drain stack to lower sanitation T to accommodate new sink and ran dirty arm from garbage disposal over to feed into 1-1/2 T going into p trap feeding into new drain itself located on right side. Tested everything By running water through both sides of Sink itself everything is testing ok at this time. Customer does not like right side strainer so customer is going to replace that themselves. Customer will have 1 yr warranty on drain itself but company cannot warranty all other cu
73 or itâ€™s free special. Company ran mainline machine through accessible clean out in cellar. Obstruction was approximately 12 to 15 feet in and company was able to get cable to run through obstruction itself and line is open and flowing at this time. Company also did complementary cabling of drain for floor drain itself and company determined that transition for floor drain going into main line is possibly collapsed. Explained to customer that they have free complementary Camera inspection but customer wants to opt out of camera. No warranty on lines. Thank you for choosing lba and have a wonderful day.
Upon arrival common branch line servicing the sinks of rooms 52 & 54 were backing up. Disassembled p trap and ran cable thirty feet with line clearing within the first five feet. Flushed line with water and tested for leaks. Stops under sink had a drip at packing. Maintenance stated they would make the repair.