AC went out. Called, arrived the next day. Repaired, had it up and running by 6pm.
The only problem I had was when Michael came to the front door he said he was there to service my furnace. He was reading this off his tablet so when I made the appointment to have my air conditioner maintained they got it wrong he immediately changed his tablet and came in and maintained my air conditioner with great service
Very professional and polite. Great price too
Angelina was very friendly and explained everything she was doing and why. Very pleased with the work and the experience. Punctual and fast work.
I appreciated Kent listening to what I thought my problems were. I appreciated he gave me different options and let me choose the option I wanted. He fixed my problem in a reasonable amount of time. He was pleasant.
Kent was very courteous and professional. My concern deals with the pricing model LBA is using. I supplied the new part, so all they supplied was the expertise and time (< 1 hour). Even with a $50 off online coupon my bill was $208. That seems a bit high to me. I had a friend who will be needing a plumber, but I can't recommend LBA due to this "one size fits all" approach.
Service tech was both knowledgeable and personable. Quickly replaced the malfunctioning garbage disposal left no mess or signs that she had been there. Very pleased.
Very efficient work. Easily understood.
Nathaniel Reece did a good job. I was impressed that he worked out a reasonable price to install my new garbage disposal even though I disagreed with the pricing options the company provided. He was mannerly and quick to complete the job.
Jerry was very efficient and courteous. He is easy to talk to and answered questions with respect.
Tenant room 203 apartment 1411 no cooling. I found one wire had came loose and was not sending signal for condensor to come on. Reconnected the wire and tested the system is operating properly at this time
Upon arrival found 3935 E not cooling as unit was out of refrigerant leak searched with nitrogen and found leak in king valve cap tightened and quoted price of refrigerant to customer who stated they wanted me to pull a vaccum on the system and they would recharge it Found 4009 C unit tripping breaker and not sending low voltage to the condenser found wired incorrectly and with a faulty disconnect replaced with customer supplied disconnect now operating well Found 3910 C not bringing on condenser due to incorrect wiring corrected and installed condensate drain so the unit would not drip on the control board
I arrived to find the blower wheel sitting idle and humming. I found the voltage enhancement system to have a fault. I made a band aide level repair that comes with a 30 day warranty.
Taped unit for apartment 203 building 117 loose seams and around the filter operating well with an 18 degree split.
Found unit had power off from meter informed Tina that power had been shut off most likely from the power company and could not test unit.
Corrected wiring on apartment 200 building 117 now operating well while diagnosing discovered 202 was not operating properly will need to return to diagnose.
Room 203 in apartment 117 was low on refridgerant i added to 2 pounds of of 410a. I also noticed that the return had a lot of openings and wasnt sealed very good so its sucking in warm air from the attic which is another factor this room might not reach the temp its set too.
Found wiring incorrect to unit corrected and unit is now operating well.
Air conditioning unit was not cooling correctly. The low voltage wiring to the outdoor unit had come loose from the terminal connection from the indoor air handler. All wires have been reconnected and the unit is cooling properly at this time. All repairs are covered under warranty.
Installed double clean out.
2 full system
Air conditioning unit for 201-117 found to be low on charge. Found the metering device to have a loose connection to the indoor evaporator coil. Connection was tightened and checked for further leaks. All leaks have been repaired and unit has been charged correctly with R410a. Unit is cooling properly at this time. All repairs are covered under warranty.
Completed cooling pma. Washed condenser coils , replace air filters, flush condensate drains , test electric compontes, and check cooling operation. See quotes for recommend repairs.
Estimate to install a clean out in yard
Conducted preventative maintenance on (4) Carrier RTU systems. Inspected all electrical and mechanical cooling functions. Inspected electrical tolerances on all motors and capacitors. Checked the supply and return air temperature differences to ensure correct refrigerant charge. Cleaned outdoor coils and flushed condensate drains. All filters have been changed. All deficiencies have been quoted for repair.