Justin was terrific. Knowledgeable, pleasant, friendly, professional, and smart! Thank you for sending him
After a third visit I believe everything is fine
It was a warranty problem that should never of happened and I waited half a day for him to get here but when he got here he got the problem solved
Great service but way too expensive
He did a great job. And he was a pleasant young man.
Thanks for fast response
Was very friendly and informative, I would recommend them to anyone
Conducted PM equipment site survey. Captured equipment info and verified customer info.
Upon arrival kitchen sink was holding water. Lines under kitchen had been previously replaced by LBA. Portion of pipe from kitchen stub out to pvc beneath, approximately 3 feet, is still galvanized. Determined after augering that the issue was within that 3â€™. Work done: Augered kitchen drain Tested flow and checked for leaks
RTU#1- has a burnt 3 pole 240v compressor contactor that was replaced today. RTU#3- has a 10mfd condenser fan capacitor that was replaced today. RTU#4- has a 10mfd blower motor capacitor that was replaced today.
Today I completed your annual cooling tuneup, Checked air filter and all indoor operations. Everything tested as it. I checked refridgerant and all electrical operations on outdoor system and they tested as they should as well. Cleaned system. Customer did not pay apon visit she said she would call in to customer service and pay over the phone. Thanks for having me out today, Eli
Performed an air conditioning inspection. Performed an electrical receiving 220 V air conditioner and low-voltage wiring communicating properly. Based on compressor readings of refrigerant, air conditioners performing to manufacture specification. Based on sub cooling and superheat refrigerant is flowing properly. Drains are draining properly.
Conducted plumbing inspection for customer. Made customer aware of recommended repairs and offered to send customer estimates for repairs and customer does not want any estimates.
Install tags on backflow preventerâ€™s and get signatures
Arrived to put on thermostat for unit we hung n ceiling
Found thermostat for rtu 1 blank. Check power supply to t-stat found 0 volts at T-stat. Discovered shorted transformer to be the reason for power loss at stat. Replaced transformer and installed 3amp fuse. Test unit operation and found shorted contactor. The shorted compressor contactor is the most likely reason for the short in transformer. Replace contactor and rechecked operation. The unit is heating and cooling properly now. All repairs were approved by Katie.
Preformed backflow test. 2â€ backflow in sprinkler room passed #1held at 8.5 #2 held at 3.5 relief opened at5. Bypass water treatment room serial #436623 passed #1held @8.7 #2 held @2 relief opened@ 3. Serial #436633 passed #1 held@ 8.5 #2 held @2.5 relief opened at 3.5. We will contact Erin with tags.
Main line was backing up into the house in the basement floor drain. There is a cleanout in the basement and the front yard by the sidewalk. The clog was between the house and the clean out outside. I had to cable the line from the basement. About 30 feet out the water started to drain. I tested by running water in the house and everything tested good.
Arrived at residence to check inspectors concerns of out door unit not cooling. Took readings from my gauges and matched them with manufacturers specification for sub cooling and all readings with within manufacturers data plate. Also took a delta T. I received a temperature difference of 19 degrees
Finalized paperwork got signatures and elevations emailed pictures to Liz
Purchase Order: 3600287245
Gave quote for installation of 2 new hot water heaters. No charge estimate