Great service but way too expensive
He did a great job. And he was a pleasant young man.
Thanks for fast response
Was very friendly and informative, I would recommend them to anyone
Good maintenance and service but a little pricy.
Friendly and explained everything to me.
He was very professional very courteous we we both felt he was a very good plumber Yelp
Jerry (tech) arrived on time, was respectful and worked hard in the hot attic to get my AC up and running. he called later to verify that all was in order. All in all I was very pleased.
Completed box install , see previous invoice for billing
Purchase Order: 3600141831
Purchase Order: 3600136390
Purchase Order: 3600136388
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and checked humidifier, performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Check unit for no heating. Found worn blower belt causing unit to overheat and shut down on high limit. Pick up belt from vendor. Replaced blower belt and confirmed heating operation. The unit is heating normally now.
Upon arrival I found kitchen faucet to have less pressure on the hot side of faucet, removed supply tub and cleared some type of debris from line. Recommended again that faucet needs replaced also with new stops. No charge at this time.
Upon arrival the customer floor drain in the basement would clog when she would flush the toilet right next to it. I had to pull the toilet and cabled the line. Flushed gallons of water done and everything tested good.
Upon arrival I found water behind toilet on first floor bath, after carefully diagnosing I found old 3/8â€ stop for toilet was leaking just enough and was soaking into wood below. Installed new stop with 20â€ supply and tested out.
Install new 40 gallon gas hot water heater with modifications. Also repair 3/4â€ copper water line overtop of hot water heater. Needs scheduled Wednesday 30, 1-3. Found very hard calcium build up on hot side. Kitchen faucet needs replaced also laundry valves for washing machine need replaced.
***90 psi water pressure*** I performed a safety and maintenance inspection on the furnace system. I found the system to be operating within the manufacturers tolerances at this time. The customer purchased a replacement Merv 13 air filter as well as a P3 membership renewal choosing the one year only option. I explained the P3 membership benefits in detail with the customer as well. Thank you
Reconnect electrical and gas lines to Rtu's on southwest roof.
Performed quarterly inspection on 6 split systems and 4 exhausts fans. . Replace air filters, check electrical connections, check motors, test flame signal, inspect heat exchangers, and test heating operations.
I preformed a scheduled maintenance inspection on the furnace, checked and cleaned all safeties, gas pressure, combustion gasses. Everything is operating within factory specifications.