I have used LBA for many years each repair person has been very good
Great guy very plesent and courtesy to the upmost👍👍👍 up
Always trust LBA’s opinion / assessment of the situation! Long time customers
Jason was very knowledgeable and efficient
The technician was very professional and knowledgeable
Justin was terrific. Knowledgeable, pleasant, friendly, professional, and smart! Thank you for sending him
10/27/2020 11:31:17 AM - Option 1 <a clicktracking="off" href="https://partsgatorstorage.blob.core.windows.net/proposals/10272020 43503 PM - 1 - 3-102720113117-Sands Enterprise-Proposal-Copy.pdf?sv=2014-02-14&sr=b&sig=%2FdnDSNbYTdlVdYN3i0E%2BRvUnIj1QoCMAhCMoh6HJjTU%3D&st=2020-10-27T16%3A38%3A45Z&se=2520-10-27T16%3A43%3A45Z&sp=rw" target="_blank">View PDF</a>
Spoke with Patrick and Charlie. Found dryers 2 and 4 not operating correctly. # 2 Solaronic Model: DJTE-95-230 Serial: 0078516-4 to have a few issues. Found Honeywell board out on flame sensor fault and not making good connection. Resecured board and cleaned hole for flame sensor eye. Also found some loose wiring to contactor. Secured contactor and unit is functioning at this time. #4 Solaronic Model: DJTE-95-230 Serial: 0078516-1 found to have bad ignitor. Ignitor wire is freyed and broken in a few locations and not allowing spark to get all the way to the ignitor. Needs replaced quote was sent to customer.
Perform preventative maintenance on Lennox hot water boiler. Checked all the electrical components and safeties for proper operation. Check the combustion on the exhaust. The readings were showing high oxygen and high carbon monoxide. After further investigation discovered there was a leaf blocking the Air divider. After removing the leaf readings were back to normal and safe. Boiler is currently operating under manufacture specifications.
Performed full heating preventative maintenance on one rooftop unit, checked all electrical and mechanical components, changed all filters
Customer complaint that sale floor is too cold and office area is ok Unit#1 found thermostat was in cooling mode switch over to heat an inspected operation of heating mode everything is working working ok Unit#2 found unit off on a fault code, open rollout switch, removed an clean electrical connection reset switch than checked operation of heating mode everything seem to be working properly Unit #3 set thermostat to 80 degrees ran unit for 20 minutes unit seems to be working just fine didnâ€™t find any problems at this time Work was performed on all trane units serial#- 18282952JA Serial#-18262675JA Serial #- 18271933JA
Changed all filters on four rooftop units
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I changed your air filter and cleaned flame safety system. I found microbial growth in system and recommended the customer have a iwave r installed and she agreed. Performed humidifier tune up Everything else tested as it should at this time
Upon arrival,found the unit not running,checked the unit out and saw that the unit would come on then shut down,also found two big hole in the duct work,we pulled the burners and clean it,clean the flame sensor,repair the two big holes also had to order a air temperature sensor,because the unit was getting too hot.,repair the unit all systems are working.
Replaced thermal expansion tank Charged to appropriate air pressures and tested for leaks.
Estimate to replace meter pit and lid. If valves must be replaced the water department must shut off water or locate curb stop.
Met Errol on repairs to the tunnel air make up. Details on his ticket.
Purchase Order: 3600598680
Upon my arrival, found heater in a alarm on flame sensor failure, remove and clean photo eye sensor, cycle for about 45 minutes at this time everything is working ok, if problems reoccurs may need to replace photo eye sensor I explained everything I done to manager on site
Checked all condensate pans and lines on all roof top units. All lines are clear and flowing properly. Checked ceiling tiles in space and looked above. Can not verify where leak might have come from but sealed a crack in duct work joint with sheet metal tape. No present leak at this time. Ductwork runs down the middle of the reception area and does not affect ceiling tiles on exterior wall. Called Christina and left a voice mail of todayâ€™s findings and explained to tenantâ€™s receptionist the same. No leaks visible at this time.
Upon arrival I found that the service valve was leaking. I resealed leak spot and recharged system. Everything else tested as it should at this time