My water heater was replaced in a timely manner and LBA had options that didn't cost a premium
Chris was very profession and kept on schedule so I could make my appointment.
I appreciate the dependability of this company to send quality service representatives who can diagnose the problem quickly and recommend a solution that doesn't require taking out a loan! The service representative was clean, personable and professional and made the experience easier. I appreciated the fact that the office called just prior to the representatives arrival to let me know he was on his way.
$173.25 to hose out Condenser Coil was extremely high, since I supplies the hose and water and it took only about 15 min. to complete. I had offered to do it myself but he said that it would be no problem for him to do it. I did not realize it would have costed $176.25 and I would have done it myself. Also $326.99 for a Dual Run Capacitor seems extremely high. I thought the whole service work was overpriced and I will not be using LBA in the future.
Angelena did a wonderful job, and I highly recommend her!
Jim was very professional and very personable and on time. Jim would be the one I would want to do any plumbing job I would have. Highly recommend.
Replaced the compressor in the Daikin rtu per approved quote. The new compressors have been installed at this time. They have been pressure tested, vacuum below 500 micron, and charged per factory spec. While attempting start up I found that the breaker tripped again. Upon checking the breaker I found that there was a slight burn smell so I pulled the breaker panel apart and found that the lugs had burnt up for this unit. The electrician will need to repair this at this time. I have reached out to Scott and sent him an email regarding this subject.
Met Josh and helped with the compressor replacements.
Econimizer is not operating properly due to a failed air temperature sensor. The economizer has been temporarily by-passed to allow for proper cooling. The air temperature sensor has been order from Carrier and will be installed once delivered.
Air sensor has been ordered from Carrier, will return to replace when sensor arrives.
Found water heater flame blowing around burn chamber irraticly , shut off heater and inspected flue , found a heavy backdraft down flue , I went on roof and discovered that the flue pipe riser had blown off of flue and pipe was wide open . Flue pipe will need to be disassembled possibly by 2 techs to repair . Customer didnâ€™t want OT charges for hvac to come out this weekend , said he could wait until next week for repairs, i temporarily put 6â€ rain cap back on flue to try and cut back the down drafts .
Diakin RTU system found not operating properly. System had tripped the main breaker. Found the first and second stage compressors both have failed internal motor windings. The windings have an electrical short causing the motor to over amp and trip the main breaker. The unit will need to have both compressors replaced in order for the system to operate properly. The compressors are covered under warranty from the Diakin manufacture. A quote has been submitted for all repairs.
Conducted preventative maintenance on (1) York RTU system. Inspected all electrical and mechanical cooling operations. Checked all motors and capacitors for the correct amperage within tolerance. Inspected the blower wheel, and belt condition. Cleaned outdoor coils. All filters have been changed. No deficiencies at this time. Unit is operating properly.
Arrived on site for no cooling. Check southeast unit in the commons area for no cooling. Found unit not cooling due to a bad dual run capacitor. Informed Jim of findings and he approved repairs over the phone. Replace the dual run capacitor and confirmed the cooling operation. Both units in the southeast closet are cooling the temperature split is 20*.
This quote includes time and material to replace the evaporator coil found with leaks in it on the south east unit that serves the lounge area in this part of the building. This will include 1 new 3.5 ton r-22 coil from Goodman Pump down of refrigerant Pressure test New r-22 to charge correctly. Vacuum below 500 microns of refrigerant circuit Brazing connections for coil New filter dryer
Checked the South area right side (west) split system for no cool. Found the blower running with no condenser due to a failed dual run capacitor. Replaced the capacitor and the pitted contactor. Started the system and verified operation. System was running normal with a 21 deg split after repairs.
I preformed a P3 safety and maintenance inspection and found the system to be operating within factory specifications.
Performed pma inspection. Washed condenser coil, replace air filters, test run capacitors, flush condensate drains, check wiring connections and test cooling operation.
Gave ball park verbal estimate to run drain line from womenâ€™s restroom to opposing wall underground . 3-5k
Arrived on site for kitchen unit not cooling. Found kitchen unit in economizer mode. Discovered outdoor air sensor reading -23* which cause the unit to call for free cooling instead of mech cooling. After checking the o.d.t sensor it started to read the correct temperature which was 84* and the unit statred mechanical cooling. This sensor will need to be replaced. Called the manufacturer to check status on the part. The part is not in stock and will take 3-5days once order to ship to our shop.
This unit has been repaired and is now operating properly. No further repair needed at this time