My water heater was replaced in a timely manner and LBA had options that didn't cost a premium
Chris was very profession and kept on schedule so I could make my appointment.
I appreciate the dependability of this company to send quality service representatives who can diagnose the problem quickly and recommend a solution that doesn't require taking out a loan! The service representative was clean, personable and professional and made the experience easier. I appreciated the fact that the office called just prior to the representatives arrival to let me know he was on his way.
$173.25 to hose out Condenser Coil was extremely high, since I supplies the hose and water and it took only about 15 min. to complete. I had offered to do it myself but he said that it would be no problem for him to do it. I did not realize it would have costed $176.25 and I would have done it myself. Also $326.99 for a Dual Run Capacitor seems extremely high. I thought the whole service work was overpriced and I will not be using LBA in the future.
Angelena did a wonderful job, and I highly recommend her!
Jim was very professional and very personable and on time. Jim would be the one I would want to do any plumbing job I would have. Highly recommend.
Performed PMA. Cleaned condenser coils, condensate drain traps, and replaced air filters. Inspected all electrical and mechanical components. All units are working as designed but there is one missing condenser unit north side of the building. Contact us if you are interested in replacing this missing unit.
Performed PMA. Cleaned condensers, condensate drains, and replaced air filters. Check all mechanical and electrical components. Created a estimate to repairs. For further information please see check sheets or estimates.
Performed PMA. Cleaned condensers, condensate drains, and replaced air filters. Checked all electrical and mechanical components. Created and estimate for recommended repairs. Please see estimate or check sheets for further information.
Performed the PMA. Cleaned condensers, and condensate drains. Replaced air filters. Checked all electrical and mechanical components. Created estimates for any recommended repairs. Please see check sheets or estimate for further information .
I found the system low on refrigerant, I was able to locate the leak in the indoor coil. I added R22 refrigerant to get them by until we can get a new system in.
I performed The HVAC APP assessment of all RTU's on the building/property to assure the condition of the HVAC equipment. Both units are operating properly within manufacturers specifications, only recommended filter change. Quote created for Air filter change.
Performed PMA. Cleaned condenser coils, condensate drains, and economizer filters. Replaced air filters, checked all electrical and mechanical components. Tested the cooling cycle of each unit and found no issues or recommendations at this time.
Goodman RTU system leaking down onto the ceiling tiles in the space. Found the evaporator coil has a cracked condensate drain pan causing condensation to leak down the supply duct into the space below. The drain pan will need to be replaced to allow for the condensation to drain properly to the outside of the unit. Goodman can have a replacement drain pan delivered within 3-4 days. An estimated quote has been submitted for repairs.
Performed final leak check with UV light and glasses, found no leak. Checked pressures on both circuits, pressures are fine at this time.
Returned and capped 1.5 washer line in wall , removed remainder of copper piping and cleaned up ceiling tiles from floor . Didnâ€™t charge for customer satisfaction.
Ra 13 and furnace tenant was not home today Scott M the sales person knows the person who owns all the units, Scott will collect for project
Upon arrival talked to Jason. He took me to apartment with odor. We checked the toilet,shower and removed cover from ada lav. Opened access cover for valve isolation no water visible inside wall opened access panel in hall adjacent to apartment and traced vents in attic. No breaks or separations.Jason has just replaced wax ring under toilet. This may have been the problem. And area may need to be aired out.
Cleared main line from 3â€ stack c/o in mechanical area of basement, line is open and flowing for now. Main line special. Line is on septic.
Found the thermostat terminal on the Prodigy control system to be disconnected. I reconnected the thermostat terminal, checked temperature split, belt tension, and ran the system through a test of both stages of cooling. The u it is working as designed at this time.
In unit 780 , turned water on and discovered freeze damage to water lines I shut water off and opened wall and repaired freeze damage to restroom water lines as well as installing new stops valves because the old ones blew off due to the freeze damage , I abandoned an capped unnecessary lines from old tenant finish . Turned water on and tested , all ok now , customer will have to repair walls before we can return and reinstall fixtures . There will be additional charges to reinstall fixtures .