Our old furnace and air (28 years old) was removed and replaced in one day. Neat and well done job LBA! One less thing to worry about🙂
Great guy! Very knowledgeable
My water heater was replaced in a timely manner and LBA had options that didn't cost a premium
Chris was very profession and kept on schedule so I could make my appointment.
Upon arrival I found that the furnace was shut in a hard lock out due to furnace safety tripping multiple times. After diagnosis I found that the reason the safety was tripping is due to the cleanliness of the system. I gave customer estimates to have issue fixed and system cleaned and he decided to go with the silver repair option. I thoroughly cleaned entire heating system, cleaned all safeties, cleaned blower motor and housing, cleaned burners, replaced ignition system, replaced air filter and after all work was complete I tested system and everything tested as it should at this time. Thanks for having me out today, Eli
Unit 4 (5908B20321) Limit switch for blower and temperature was unplugged next to blower housing. Plug must have got disconnected through small vibration over time. Plugged back in and made sure it was snug and verified operation of unit. Completed a heating check out sheet.
Purchase Order: 3600598698
Talk to gentlemen in office about cooling issue and he described what was going on as thermostat kept saying cooling wait. At the unit for front lobby, serial (1705168649) found compressors locked out at control board. Reset unit, compressors continue to lock out through control voltage. Began troubleshooting and under further determination found the Honeywell economizer board to being shorting out not allowing either compressor to kick on and run. Quote sent over to customer for replacement of economizer board and sensors. Unit now has economizer bypassed at economizer plug in return side.
Show up tp help James trouble shoot a no cooling call
Arrived at home October 14. Customer routinely gates mainline snake from cleanout in basement yearly. Snaked mainline out to city sewer to ensure that drain remains clear. Drain is functioning properly at this time. Noticed water heater in basement was manufactured in 1990. Water heater should be replaced before it causes leak. Customer declined estimate for water heater. Thank you for choosing LBA have a wonderful day.
Upon arrival the customers hallway bathroom toilet wasnâ€™t filling up the tank and running constantly. I replaced the fill valve and flapper in the tank and tested by flushing the toilet. Everything tested good.
I returned to complete the maintenance and safety inspections on both the hot water boiler system as well as the carriage house furnace system. I found the hot water boiler system to be operating within the manufacturers tolerances at this time. During my inspection of the carriage house system I did discover a fault within the air movement system. The indoor blower motor bearings are showing their age and the motor shaft is allowed slight side to side movement and also the VEC serving that motor tested outside of the manufacturers tolerance. The system is still operational at this time. I tested in both heat and emergency heat modes both of which were operational. The customer informed me that they will be moving to Grain Valley and I instructed them that their membership will transfer with them but the boiler and furnace maintenance visits have been used after todayâ€™s services. Thank you
Rooftop unit #2 Model# YSC036A1EHA16D00000000000 Serial# 410101602L was found with a bad 12.5 mfd capacitor that read 11.00 which is out of the 10% range of tolerance
Performed planed maintenance as contract states. All systems are running at factory specifications at time of departure.
Completed full cooling maintenance from 5/28/20.
Spoke with Chris, they are to remodel garage and are asking for mini split to be installed. Wires for mini split will have to be installed during remodel to be able to run wires behind wall to electric panel down stairs. He said he would schedule accordingly with us to get this accomplished. Sent information to Brett and Gregg for estimate on install of mini split. Customer asked about solar panels and back up generator and We referred him to Pro Electric.
Performed full heating preventative maintenance on two rooftop units. Trane unit 1 model# YSC060A1EHA001S serial# 409102108L and trane unit 2 model# YSC036A1EHA16D00000000000 serial# 410101602L. Changed all filters, checked all electrical and mechanical components
Estimate for plumbing
Take survey On both carrier RTUS , after taking survey we called Troy to give her an update, she said that she wanted to have both units replacd with equipment that they will proved. we email all information over to Brett and Greg for a replacement This location does not have any roof access, tech will need a 32â€™ ladder to get onto roof. We are waiting for Troy to give us the model and serial numbers for the units that she will be providing us to install. Once I have this information I will give it to Brett so that he can finish the replacement quote.