Our old furnace and air (28 years old) was removed and replaced in one day. Neat and well done job LBA! One less thing to worry about🙂
Great guy! Very knowledgeable
My water heater was replaced in a timely manner and LBA had options that didn't cost a premium
Chris was very profession and kept on schedule so I could make my appointment.
Upon arrival checked air filter, clear the condensate drain, checked temperature drop across the coil, clean the condenser coilâ€™s, checked Electrical components, tightened all electrical connections, checked systems refrigerant charge. AC system is working properly at this time.
Performed preventative maintenance on two rooftop units checked all electrical components, changed all filters, washed all coils
Upon further examination of system. Certain parts of this system are not made any more and are unable to be bought. Customer is aware of this and is waiting for replacement quote.
Today I completed your annual cooling tune up. I tested all indoor operations. Tested temperature split and checked filter. I tested all outdoor operations. Checked refrigerant and cleaned outdoor system. Everything tested as it should at this time. Thanks for having me out today, Eli
Performed full preventative maintenance on one rtu. Checked all electrical components, changed all air filters, washed the condenser coil.
I found the disconnect to the RTU left off after a maintenance that we did yesterday. After turning on the disconnect the system came on and the code on the thermostat went away. No charge.
At time of arrival Found thumb gum on out Side line set had come off reapplied.
Performed preventative maintenance on two RTUâ€™s checked all electrical components, washed both condenser coils, washed economizer filters, and changed all air filters.
Install new Watts 3/4â€ pressure regulator with new service valve, pressure set to 80 psi. Recommended P3 Service agreement for future maintenance.
Arrived and checked in with Brittany the manager on site. See advised that she called another company that was already working on the unit. She said we were to call before coming out. No one called per her.
Checked the Goodman Rtu model DCG0902103BHXAAB serial 1705168649 for the front of the space for intermittent no cool. Found the unit cooling normal on arrival. Checked the unit and found the control board intermittently dropping the compressors out on start up. Replaced the control board. Verified operation. Repairs were approved by Scott W.
Rheem RTU Model RLNL-B120CN 000 Serial 7946F281107292 The system has blown fuses (FRN-R-60) and a cracked belt (B50) I need to make these repairs before diagnosing the system any further. I replaced the belt and adjusted it to the proper tension, and replaced the fuse. After that I turned the system on and checked the unit in cooling stage. There was a 19 degree temperature split. The system ran for 30 minutes with no issues.
I have finished the quote from the night of Thursday July 16th, and emailed it. These repairs need to be made before further diagnosis can be made.
Upon arrival I checked and tested backflows in water treatment room backflow number one serial number 019701. Watts 1.5 LF009H2QT. Check valve number one Held at 7.5 check valve number two Held at 1.75. Relief valve opened at 2.2. This Backflow passes. Backflow number two serial number 020547. Watts 1.5 LF009H2qt. Check valve number one held at 8.75. Check valve number two held at 1.5. Relief valve opened at 2.5. This backflow passes.
I found the unit in the back ( Raheem M#RLNL-B120CM 000, SSN 7946F281107292) to have a blow fuse (FRN-R-60) at the mane power disconnect. This was causing the system to run out of phase and leaving it unable to run the compressors or blower. I Also noticed that the blower belt ( B50) was cracked and very loose, this belt needs replaced. These repairs need to be made before further diagnostics can be made. At this time the supply stores are closed and I can not get prices for a quote. We will need to come back during business hours. I will make a quote in the morning and send it over.