Noah, very good worker. Very thorough.
Jose was very polite and did a great job being socially distant during this crazy pandemic. I felt like he did a thorough job cleaning and checking my ac unit to make sure everything was working properly. Thank you!
Technician had this done in no time. Did a very nice job. Friendly guy.
The technician was friendly, introduced himself, respectful & knowledgeable. He answered all questions, showed my husband that he found that the humidifier was not snapped back into the housing all the way which was the reason for the leaking of water from the unit & it not working properly.
Have worked with Rick in the past and trust his judgement and work.
Aaron did a very thorough job and explained everything perfectly.
Would recommend them to anyone. They are friendly knowledgeable patient & efficient.
There was a tech at our door less than 2 hours after we contacted the company on Christmas Eve regarding our hot water heater going out with 12 people staying at our home. He was friendly, knowledgable and fast. However, the pricing was much higher than other companies.
Arrived to find the compressor over ramping and shutting off due to internal overload. The compressor will need to be replaced. Will be using a newer model compressor and will need to install a compressor conversion kit due to compressor for this model is discontinued by manufacturer. Estimate includes labor and materials for replacement. Model-2TTAOO60A4000AA Serial-32112GM3F Parts been order on 10/26/2020 want be available until Friday on10/30/2020
Arrived at home October 14. Gas line had to be inspected by Overland Park inspector. Attached gauge to gas line outside near gas meter. Pressurized gas line up to 15 psi. Tested for 15 minutes and pressure held. While at home Overland Park inspector arrived. Permission was given by homeowner to enter home and show inspector work that had been completed. Inspector approved home to have gas back on to home. Removed gauge from gas line. Gas is now OK to be turned on by county. No charge to customer.
Ran new gas lines from meter to range, water heater, and furnace. Lines ran in Flash shield. Lines were pressure tested at 15 psi for 15 minutes and checked for leaks.
Service charge for today returning tomorrow to install icemaker box Iâ€™ve created an estimate.
Arrived at home Monday, October 5. Customer already had hose bib set up and ready to be soldered. Soldered hose bib for customer. Tested for leaks and proper function. Hose bib is now working properly with no leaks. Company will not have any warranty on parts or labor today. Company will not have any warranty on parts or labor today.
Perform maintenance and safety inspection on Lennox furnace. Checked all electrical components and safeties for proper operation. Performed combustion analysis cleaned out furnace. Filter is clean at this time. Furnace is currently operating under manufacture specifications.
Customer complaint of no cooling from split system Checked and found thermostat in cooling mode , checked condenser found fan running but no compressor, checked refrigerant charge and low pressure switch both are ok , notice compressor is open on thermal protection, cool down compressor than try to run system ,compressor motors amps locked up about 78 amps, compressor is bad need to be replace, talk with customer and they request to send a quote to have compressor replace All work will be scheduled on condenser unit #3 Trane#3 Model-2TTA0060A4000AA Serial-32112GM3F
Performed full heating maintenance. Changed filters, checked all mechanical and electrical components. Checked heat exchanger and heating performance. All units working properly at this time.
Performed full heating preventative maintenance on four furnaces checked all electrical and mechanical components, changed all filters.
Arrived at home September 3, 2020. Customers main concern being shower valve in master bedroom not shutting completely on hot side and continuing to drip. Customer chose to go with Bronze level repair of shower faucet. Shower faucet was two handle Gerber shower valve. Picked up parts at Ferguson that came with trim and handles as well. Replaced both hot and cold cold stems as well as handles and trim. Tested shower for leaks as well as proper function to make sure seats in shower valve weâ€™re still operable. Master bathroom shower is now testing properly at this time no leaks in valve or dripping from shower head. Shower valve stems will have six month bronze level warranty on parts installed today. Thank you for choosing LBA have a wonderful day.
Performed maintenance inspection on a trane air conditioner. Checked all the electrical components and refrigerant for proper pressures and temperatures. Customer will replace air filter. Washed outdoor condenser coil. Air conditioner is currently operating under manufacture specifications.
Upon arrival Found that drainage system was partially clogged. Flushed all drainage systems for the HVAC system. Resealed all a coil penetrations. Spoke with customer about performing maintenance on the air conditioning and furnace systems customer was not interested in maintenance agreement at this time. System is cooling properly and draining properly upon departure.
OAT 85 RAT 74 SAT 59 Upon arrival the customer informed me that their Ruud AC system serving the main level of the residence was operating but it wasnâ€™t operating as well as it once did. After further investigations I discovered that the EEV isnâ€™t regulating the flow of refrigerant entering the indoor coil properly. I tried to test the EEV suction line thermistor but I recorded infinite ohms. I have created an estimate for the appropriate repairs for the customers records. I will return Monday between 12-4 pm to complete the EEV repairs that were proposed. Thank you
Performed maintenance inspection on a Ruud a/c. Checked all the electrical components and refrigerant for proper pressures and temperatures. Replaced filter with customer provided filter. Washed outdoor coil. Air conditioner is currently operating under manufacture specifications.
Performed maintenance inspection on outdoor air conditioner. Checked all the electrical components and refrigerant for proper pressures and temperatures. Check temperature split and washed outdoor coil. Air-conditioner is currently operating under manufacture specs.