Jerry quickly assessed the problem and corrected it.
Our air conditioner went out last Saturday. Jerry, our LBA technician came out Monday and diagnosed our problem, which required ordering a part. He found the part out of town and he ordered it for Wednesday delivery. On Wednesday when it hadn’t come in he called the supplier several times and was told they would check it out. He called once again and found out it had not shipped as promised. He required they send it by overnight and it came in this morning and he immediately brought it out to install it. LBA had him on call yesterday to install it, but since it didn’t come in, he came in at 6 AM today to wait for it. LBA kept us informed throughout the week. Their customer service was outstanding and I will happily recommend them to friends. Al Cohen
Nate was prompt, polite and professional. He had done work for us previously and that is why we called again!
Arrived on time and did a good job.
All good now
On time, let you know exactly when they’ll be there. Polite, courteous and professional.
Checked the conference room in suite 300 for low air flow too warm complaint. Found the supply register dampered down to 50%. Opened the damper to 100% for maxium air flow.
I came back to replace the condenser motor, after discovering a fault during a tuneup on the tenth. The system is running within factory specifications at this time. Kay previously paid me for this job.
Upon arrival customer took me to the master bathroom where the toilet was running. After showing options customer chose the bandaid toilet repair.30 day warranty.I replaced fill valve and flapper. And checked operation.
I found a setting on the thermostat set to run the fan always. I rest the thermostat and the fan now turns off when the thermostat reaches temperature.
Replaced the 2 pole contactor and the AX35 blower belt. Tested functions of both and the unit is cooling as designed.
Estimate for joco sump pump and backwater valve
Completed PMA. Cleaned the condenser coil, condensate drain, replaced air filters. Checked all electrical and mechanical components. Tested the functions of the unit. Created a estimate for repairs. For further information please see checkout sheets and the estimate.
Conducted preventative maintenance on 3 Carrier split systems. Inspected all electrical and mechanical cooling components. Inspected condition of all blower wheels, motors, and capacitors. Cleaned all coils. Replaced all air filters. All deficiencies have been quoted for repairÈ™.
Upon arrival customer took me to the basement where he wants to remove about 30â€™ of gas line and cap. Waiste under laundry sink cut out and capped. And to cut and cap water lines to laundry sink. I did as requested. Two year warranty. Platinum.
I preformed a p3 maintenance and safety inspection on the smaller air conditioner, it was working within factory specifications. I attempted to do a maintenance inspection on the larger unit but the condenser fans miter has gone bad. I was unable to check the pressures but did the rest.
Sump pump that was installed on Saturday was sounding a alarm battery leads need cleaned or battery not functioning. Replaced maintenance free battery. Warranty no charge.
Upon arrival I was Informed unit #3 was not cooling. I inspected the unit and found the low voltage transformer was blown. I replaced the transfer turned on the unit, and the low voltage fuse going out. I found in the condenser That a mouse had chewed through the wire insulation causing a short. I fixed the wiring and the unit is operating properly at this time.
Installed new pro series combo pumps with maintenance free battery, hauled off old unit.
Upon arrival found that the thermostat had failed at this time. I replaced thermostat and proceeded to check temperatures and found that the temperatures were not running within factory specifications.i the. proceeded to then check the refrigerant charge and found the refrigerant charge to be low. Performed electronic leak search and found a leak in the heat media transfer coil. After speaking with the customer customer decide to go with gold repair allowing me to replace the heat media transfer coil, replaced the thermostat As well as a water heater temperature and pressure failure.
Rebuild spare bathroom toilet and replace stop bronze package 60day warranty