Received AM call asking to move appointment for tune-up from afternoon, agreed. Did tune up but had to relay disappointing news that 2-1/2 year old Aprilaire humidifier had failed. Not Eli’s fault of course just bearer of bad news. He explained cost to replace, pro-rated credit to be applied to that cost. Overall he did excellent job, and was extremely courteous & clean.
The technicians arrived at my home at the designated time, put booties over their shoes to keep my home clean, were very professional, considerate and kind. I cannot say enough good things about this company....and I'm spreading the word!!
He arrived on time and stayed with the job until it was completed.
great experience, Great techs
Phil and I had a good time. Waited a week to be sure the job was effective.
Always get great service from LBA
Found unit M#ZE048H12A2AA1BAA1 S#N1B9598689 operating in free cooling mode. With 68* outdoor temp. Set free cooling mode to 55* and 50%th. Confirmed cooling operation. The unit cooling normally now. Warranty call.
Checked all operations in the cooling mode for both systems. Replaced both furnace filters at this time. Checked all electrical and refrigeration components outdoors. Found the units to be extremely unlevel causing the voltage enhancement systems to fail from overworking the exhaust removal system outdoors. After speaking with the customer customer decided to re-level the air conditioners and extensively clean the outdoor units as well as replace both voltage enhancement systems at this time. Equipment is now operating within factory specifications at this time.
Estimate for kitchen line reroute
Upon arrival the kitchen drain was backing up into the floor drain in 5he basement. There is a clean out between the washer and dryer in the basement that I tried to cable the line through. My cable could only get out about 7 to 10 feet. When bringing the cable back there was a lot of slug and mud on the line. After see that I decided to un the cable through the floor drain and got the water to drain. Have pat out to give a bid on a new kitchen drain line.
Performed pma inspection. Replaced air filters, checked capacitors, checked wiring connection, flush condensation drain and test cooling operation.
Performed double wall flue pipe replacement on older furnace. Internal rust. When removed it broke apart. Flue running normal .
Performed the PMA. Replace air filters, cleaned condensate drains, and condenser coils. Tested cooling functions, checked all electrical, and mechanical components. For further information please see check out sheets.
I performed a safety and maintenance inspection on both AC systems. I found the Lennox XC17-036 system that serves the main level to be operating within the manufacturers tolerances at this time. I found the XC17-024 system that serves the room addition to also be operating within the manufacturers tolerances at this time. The only concerns I had was the XC17-024 systems air filter was rather dirty and the line set insulation to that same system was deteriorating. I spoke with the customer regarding my concerns and the customer chose to make repairs to the line set insulation and replace the Merv 16 air filter. Additionally the customer renewed their P3 membership choosing the annual recurring standard P3 membership option. Thank you
Cabled approximately 30â€™ from drain next to stationary tub in basement, line is open and flowing at this time. Flushed with multiple gallons of water to test out.
Hole house plumbing inspection and water heater flush. Water pressure is 65 psi. In range. Checked natural gas with a detector and no leaks detected. Water heater is 14 years old and recommend replacement do to age. And recommend a water treatment system to help with calcium build up. Flushed water heater.
Installed new Koehler round front comfort height toilet in upstairs spare bath off of bedroom, tested for operations. Cleaned up and hauled off old fixture. Customer requested using her Syncrony account.
Performed a safety inspection and a furnace tuneup. All safety switches are corresponding to their specification. Completely cleaned safety switches and recalibrated. Performed combustion analysis, combustion motor is operating within guidelines and properly pushing carbon monoxide out of the house. Performed an indoor blower test, Indoor blower motor is working to manufacture specification. Checked all drains, drains are draining properly. Performed an electrical test, high-voltage wiring communicating properly the furnace. High-voltage and low voltage stable and secure. Furnace is performing to manufacture specification. Picture I took on file is of the underneath tub in the upstairs customer thinks it leaking. Believe he is right.
Upon arrival water heater pilot light was out. Water heater is 13 years old. Flame switch was not tripped. Burner chamber had some debris in it and needs cleaning. Water heater shows signs of general deterioration (rust and scaling) Temperature and pressure valve has tripped at some point. Work done: Relit Pilot. Recommendations: Recommend replacing water heater due to itsâ€™ age and condition.
Upon arrival the sewer smell the customer had reported in 1st floor guest bath had gone away. She had ran water through the shower drain to refill the p-trap. Checked all other accessible problem areas and did not find another issue.
Checked unit for pre-k room for no cooling. Found unit locked out on fault code 9 limit switch or rollout fault. Checked heating operation. The heating temperature rise was in range and there was no sense of flame rollout at this time. There are pleated filters in return air grills that could cause air flow restriction. The furnace and A.c. are working normally at this time with no issue.