The technicians arrived at my home at the designated time, put booties over their shoes to keep my home clean, were very professional, considerate and kind. I cannot say enough good things about this company....and I'm spreading the word!!
He arrived on time and stayed with the job until it was completed.
great experience, Great techs
Phil and I had a good time. Waited a week to be sure the job was effective.
Always get great service from LBA
I just had Eli here again to finish the work that was being done on my furnace. He is such a nice and professional young man. I appreciate having him as a service provider.
Phil was very professional and did a great job explaining the problem and solution and even helped check another spigot to make sure we didn’t have a problem with it.
Submitted repair proposal for install of service disconnect, and verified two compromised heat exchanges.
I performed a full heating CPMA on 6 RTUâ€™s. I checked all electrical and mechanical functions of the heating cycle on all units. All filters were changed as well. Upon inspection of the units a few deficiencies were found. RTU 03 S# N1B9598689 is wired incorrectly and has no power disconnect. Without said disconnect the unit is unsafe to properly do any repairs or maintenance on. RTU 02 S# N0H7167172 and RTU 01 S#N0H70436 have multiple cracks in the heat exchangers, which may be causing Carbon Monoxide to leak into the airstream of the building whis can cause serious medical issues if unresolved. RTU 01 has a bad draft inducer motor as well. I have provided quotes for repairs on all unit that require attention. Please see the checkout sheets provided for any further questions or concerns.
Performed the preventive maintenance for the heating season. I checked the amp draw of the blower motor and inducer motor, I made sure that the blower wheel and belt were in good working condition, I took readings of the capacitor to make sure that it was within the manufacturer's recommended tolerance, I looked over the heat exchanger to make sure there were no cracks or holes, I took a temperature split reading and I changed the filters. I found that RTU 3 was missing the service disconnect switch and that RTU 2 had a crack in the heat exchanger so the W terminal has been disconnected due to this being a health hazard.
Upon arrival the main line was backing up into the floor drain. I cabled the line through the main line stack in the basement. The clog was about 20 to 30 feet out. When bring the cable back there was kids underwear warped around my cable. I tested the main line by running lots of water and everything tested good
Arrived to find uv airflow sensor has failed due to previous water damaged. Recommended replacement of the system. Customer wanted to replace uv system for the sanuvox srmax. Replaced uv system performed safety testing to ensure system is operating properly. Turned on airflow sensor in new uv system. Unit is operating properly at this time.
Estimate for tankless water heater Please disregard the tax this is an error
Performed two full heating inspections. Checked all wires and safety sensors. Cleaned both indoor units. Both humidifiers are operating at this time. Performed bandaid repair on basement unit on the combustion exhaust system. Furnace filters were ok at this time. Units are now operating within factory specifications at this time and Also Changed bulbs in the uv light systems.
Preformed hole house plumbing inspection. Water pressure 70 psi. In range. Natural gas no leaks detected. Age of water heater 15 years old suggest replacement do to age. Bar sink disposal not working. Reset breaker and ran. Customer had kitchen faucet repair she wanted. I showed customer options and she chose the band aid with 30 day warranty. Installed new spout and checked operation and for leaks.
Flue pipe for 90%system is leaking at 3 different joints. Replaced parts, system is working to specification.
Upon arrival customer took me to the basement where the water heater was leaking water from the base. And second water heater is a 2003. After showing options customer chose the bronze 50gal water heater to replace the two 40 gal water heaters. 6 month warranty on the bronze package. Removed old water heaters. And installed one 50 gallon water heater and expansion system with new ball valve.
Performed a furnace safety inspection and a humidifier tune up. All safety switches are corresponding to specification. Completely cleaned and re-calibrate all safety switches. Performed combustion analysis, combustion motor is running to specification and pushing carbon monoxide out of the house properly. Performed an electrical test, 120 V going to furnace table and secure at furnace. Low-voltage wiring communicating properly between thermostat and board. Low-voltage wire secure at board and thermostat. Performed an indoor blower test, indoor blower motor is performing to manufacture specification. Based on my reading is the furnace is running to manufacturing specifications. Gas valve had a flex gas coming out of the furnace, By code hard pipe should be coming out of furnace. Recommended replacement for a customer, customer chose bandaid repair. Performed gas test, no gas leaks found system checked out great
Upon arrival I spoke with Justin and he explain the unit In the IT ceiling was leaking again. After inspection the condensate pump I found the check valve in the pump was corroded and was sticking not allowing it to pump water out and eventually over flowing. I completely dissembled the check valve and cleaned it out throughly. I reinstalled the check valve and poured 4 pitchers of water into and the pump moved the water fine with no issues.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
I filled out replacement forms for both Trane rooftop units over the space and emailed them to our estimator.
Customer decided she wanted to go ahead and replace the system did not charge anything at this time informed customer that we will call back to collect a service fee if the customer does not decide to replace her HVAC system.