Eli was wonderful! After an early morning call with an upbeat receptionist, an equally upbeat scheduler had Eli here within an hour! He toured our newly purchased home solving several heating anomalies and set us up for a 24 hour installation of humidifiers and repairs. We couldn’t be more relieved and satisfied.
The technician’s service was good. He was very professional. The cost of the hot water heaters was high. But Noah was pleasant.
Performed heating tuneup on furnace. Performed tuneup on humidifier and replaced water panel. Performed combustion check on heat exchanger. Checked temperature rise. Verified proper operation of humidifier and heat furnace system. Inspected all electrical components and electrical wires. System is running within manufacturers specs at this time
1-13-21 wed 7 hrs South Tennis bubble was started to loss pressure and coming down, They need to have the yes back up generator tested and figure out why they lost pressure. When I arrived the magnehelic was reading .75 inches water column which is OK and the bubble was up. Kevin and I tested the loss of power, back up generator. Working properly One thing though we had to turn the generator off manually but that may be due to a minimal run time controller that we werenâ€™t gonna wait for. At this time I checked the belts on the two auxiliary blowers found one supposed to have a B-belt but has an A-belt on it. It is also loose and slipping this may be the cause of the bubble starting to come down. However, changing it today with high winds itâ€™s not a good idea we will return when the winds calm down. Other issue, that has come up is that the low pressure horn is going off before the back up motor is coming on. It should be the other way around. The controls do not have a schematic i
Upon arrival found unit running IT room not to be cooling. Spoke with Norman and found condenser not to have any power. After finding breaker box found compressor pulling high amps due to failed run capacitor. Replaced fan and compressor run capacitor per approval of Norman on site. Unit began to function and only pulling 9.9 amps out of 11.5. Found the delta T to be 18 degrees and unit back up and functioning. Customer now did not request a quote for leak search but is still asking for replacement quote. I gathered information and sent to estimator. Upon departure unit had satisfied and shut off at thermostat. Trane condenser model: TTB024C100AA Serial 54857S95F.
Changed out 40 gallon water tank added expansion tank and water leak alarm. Customer had a 3â€ chimney liner so reused liner.
Johnson County Waste Water 4â€ Zurn backwater valve installation, with sump pump and pit replacing exsisting soil pipe drain for walk out area drain. Broke up approximately 20â€™ of concrete in corner of basement installing backwater valve and 22â€ base in with Zoeller sump pump and new 120volt electrical outlet for operation. Replaced concrete to finished grade and hauled out all job related debris. Also splashblock installed at end of run on outside. Tested for operations. Job is to be billed to Johnson County Waste Water.
Thank you for allowing me to service your HVAC equipment today. Performed maintenance and safety inspection on the air handler. Inspected all electrical connections to ensure they are secure and not rubbing. Tested all heating elements and their safeties. Tested air movement system to ensure adequate air flow. Filter (20x20x1) did not need replaced at this time. Spoke to the customer about the age of the system and does not want a Comfort Specialist to come out and give an estimate. System is running safely and within manufacturers specifications at this time.
Camera sewer found cast iron rotted. Gave estimate for repair
Performed furnace maintenance. Filter does not need replaced. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Performed a humidifier tuneup. System is heating and operational at this time. In completing a thorough evaluation of mechanical systems in the home, I found the existing water heater was 38 years old and I found a gas leak on the gas valve of the water heater. I recommended replacement of the water heater. Spoke to the customer about the issues with the water heater and tagged the water heater. Gave customer an estimate for a new water heater, including all code upgrades required.
Arrive to customers home Friday, January 15. Customers floor drain in basement backing up sewage. Snaked drain line that was causing floor drain to back up roughly 40 feet to clear blockage. Cannot get cable farther than where a blockage was cleared. Cablehead kept getting snagged on something in pipe. Customer decided to have drain line camera technician come to home to be able to properly diagnose drain obstruction. Warranty on drain opening will be dependent on what camera technician diagnosis. Thank you for choosing LBA have a wonderful day.
Performed heat pump tune up. System is heating and operational at this time. Spoke to customer about adding a humidifier to the system to help with humidity levels in the home. Customer is not interested in a humidifier.
Install pump, pit, and backwater valve
88 dollar tune up special. Cleaned furnace, vacuumed intake screen, performed combustion analysis, checked components for reliability, measured temperature difference across furnace, performed heat exchanger inspection and checked for gas leaks. No concerns with furnace safety or reliability at this time. Could upgrade thermostat to Lennox iComfort control (this control is made for this furnace and would get the most efficiency out of the furnace). There are also universal WiFi thermostats now that can run on 4 wires.
Performed maintenance inspection on 2 American standard furnace. Checked all the electrical components and safeties for proper operation. I did discover that the main floor furnace had a failed control board not sending power to the combustion blower. Customer approved repair on getting control board and wiring harness replaced. I replaced control board and will need to return to replace harness. Both furnaces are currently operating under manufacture specifications.
Performed maintenance inspection on rheem furnace. Checked all the electrical components and safeties for proper operation. Replaced air filter. Checked combustion in the exhaust. Furnace is currently operating within manufacture specifications.
Upon arrival I found that the gas valve connector was not all the was secured. I secured it to the valve and found that the system was tripping on high temperature due to dirty filter. I replaced air filter and everything tested as it should at this time. Thanks for having me out. Eli