Nick did a great job explaining what he found and advising available options.
Quick and on time.
Pat provided excellent consultation and a very quick reasonable estimate for the work.
On time, quick work, and helpful service and advice.
Upon arrival customer stated the humidifiers werenâ€™t working. After further investigation discovered that the reverse osmosis filtration system was bypassed due to it leaking outside of the casing. recommend replacing the reverse osmosis filtration system. Customer said he would do that himself. Also the second floor humidifier has a failed water solenoid recommended replacing but warned the customer that those solenoids are known to fail quite often. I will leave an estimate to replace water solenoid. Thank you
I was called out because the south east corner of the building was not heating. There was some concern that the issue was with the new Lennox unit that we installed this year. This was not the case. The faulty unit is a 8 year old carrier (model 48TCFD12A2M5A0B0A0, serial number 5012G10150). The gas valve is not activating when power is supplied and must be replaced. I hav left a quote to replace the gas valve via email, this quote includes all parts, labor and taxes.
Welcome to the LBA Family. Do not hesitate to call for more information about your next plumbing visit and Spring tune up. Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they were secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Replaced the filter and tested the air movement system. Cleaned furnace cabinet inside and out. Furnace is running safely and within manufacturers specifications.
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they were secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Filter (16x25x1) was new so I left one for future use. Serviced the humidifier and tested. Water flow is adequate, water pad is changed, and drains properly. Cleaned cabinet inside and out. It was time to renew Service Agreement.
Upon arrival I performed a whole house plumbing inspection. Water heater is 18 years old. I recommend replacement due to age. I checked the water pressure. It was 70 psi. Within range. I checked natural gas system with a leak detector . No leaks detected.I checked all of the plumbing fixtures and everything was operating normally.
Upon arrival Sloan handle was in menâ€™s lobby restroom was leaking. Replaced seals and springs and diaphragm. Tested for leaks and proper function.
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I changed your air filter and cleaned flame safety system. Everything tested as it should at this time
Found the fuse blown on the circuit board of the furnace. This means there is some type of short in the electrical wiring. Removed all thermostat wires to test furnace. Furnace runs without issues with the thermostat disconnected. Found a short in the thermostat. The thermostat (ADC-3000) was wired wrong. The blue wire was wired to the â€œBâ€ terminal on the t-stat. Also found the Red wire wired to â€œRCâ€ when the manual calls for it to be wired to just the â€œRHâ€ terminal. Went to test system after wired properly and found the AC and Heat were coming on at the same time. I have now found that the t-stat has a short. Customer is going to have his security company come out and fix it. As of now the furnace is only wired for heat and the fan runs constantly due to a short in the thermostat. Replace thermostat for equipment to run properly.
Checked all operations in the heating mode. Customer takes care of furnace filter. Cleaned and checked all safety systems. Performed combustion analysis. Furnace is heating within factory specifications at this time.
Arrived to do start up with Johnson Controls. On two air handlers and two 3 ton heat pumps. The rep for Johnson controls had to leave early. He was not able to complete full commissioning of units. I will reach out to him and find out when he will be able to return to finish commissioning of the Units. I will pass the information on to the commercial construction dept. so we can move forward with this project.
Upon arrival the customer had a leaking from the shower in the downstairs basement. The customer just finished fixing his shower valve and thought it was leaking. I looked at the work and noticed the customer did a good job on it. The overflow had a small opening in it. I told the customer to go downstairs and see if water would come down. I poured some water on the tub overflow and the customer said water was coming out really good. I showed the customer what I did and presented options on repairs. Customer declined and said he will use his own caulking to take care of the issue.
Arrived at home Saturday, October 24. Previous technician at home attempted to repair newly installed water heater with new pilot assembly. According to customer shortly after a technician left town pilot light on water heater went out. Upon arriving to home Towne the pilot light was in fact not lit. Replaced control valve and entire burner assembly on water heater. Customer multiple times to ensure a pilot light was staying on and water heater is functioning properly. Water heater is now functioning properly. Labor and parts under warranty no charge to customer today. Thank you for choosing LBA have a nice day. Ruud 50 gallon natural gas SERIAL #Q122007358 MFH. DATE 12MAR2020
P3 Furnace Maintenance Tuneup- Inspected thermostat, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Performed humidifier maintenance, replaced water pad, cleaned drain line and inside of humidifier, humidifier is set for the winter. All heating ops are normal at this time.
Warranty call on water heater. Pilot would not light and stay lit. I replaced pilot assembly. And relit water heater.
Performed maintenance and safety inspection on the furnace. Inspected all electrical to ensure connections where secure. Performed combustion analysis on the heat exchanger and found zero issues. Cleaned furnace housing inside and out. Humidifier is on and set to 35%. Furnace is running safely and within manufacturers specifications.