Quick response time solving my urgent a/c problems with skill and cleanliness .
LBA quickly responded on a Saturday and got me back up and running in no time. Thanks
Nathaniel performed a very professional job and discussed any problems or concerns in an easy to understand manner. He did a truly great job.
We had a water heater go out first thing in the morning and expecting out of town guest to arrive later that day so we called LBA and of course the service was outstanding! I apologize for not knowing the lady's name that helped schedule the appointment but she was amazing! By 8:00 AM we received a text from Phillip Norris letting us know he would arrive by 9:00 and precisely at 9:00 he was at our door. Phillip was friendly, polite, very informative and extremely patient in answering and explaining all of the questions that we had for him. Phillip understood the fact that this is a big financial decision and did not pressure or rush us in the least to make a decision on how we wanted him to repair and or replace the unit. LBA should be happy and proud to have an employee like Phillip!! Thank you!
I’d have them back again!
Same day service and what a personable professional guy! Work was done quickly and well; couldn’t have asked for a better experience!
He received my message that I had to leave by a certain time, and so he arrived with plenty of time to fully evaluate our options with me. When he arrived, he introduced himself and got to work. He was able to answer all of my questions about a replacement tank, tankless, and instant hot. He made sure to confirm my email where he'd send the estimate. Still have to review the options with my husband, but as far as using Pat or LBA in general, we're fully confident and comfortable moving forward.
Upon arrival found production area unit frozen with all three units having very worn belts replaced all belts and had customer turn production unit to fan on for over the weekend to thaw unit out other two units operating well now with a 21 degree split informed customer we could set up a meeting with a maintenance specialist to set up a scheduled maintenence plan. L
Preforming a p3 safety and maintenance inspection I found the indoor coil to be frozen solid. After thawing the coil I discovered that there is a restriction in the recreation system. At the minimum we need to replace the Thermal Expansion Valve.
Looked at septic tank Work will be done Tuesday 9/24
Tested backflow , yielded passing results , will send ppwork to water one
I found the water supply to the humidifier stuck open causing the humidifier to build up calcium and other growth. Because of the growth I recommend a whole home air cleaner. I replaced the water control, water panel and the drain line.
Installed Ruud U802VA100521MSA Gas furnace. Also installed customer supplied Nest thermostat. Customer has financed.
Check unit #1 for no cooling and condensate leak. Found clogged drain causing water to leak out of cabinet. Flush drain to restore flow. The unit is drain properly now. Replace customer supplied air filter. Check cooling operations. Found refrigerant within acceptable parameters and the unit is cooling with a normal temperature split of 19*. Check capacitor and fan motors amp. The unit is operating normal at this time.
Price to make refrigerant repair on overtime basis there is no guarantee of the operation of the system as the compressor may have some unknown damage as the system was completely void of refrigerant does not include repair to any other unit which may be needed When I arrived on site to make quoted repairs I was told by Eric who was working the front desk that the A.c. was fix already. All three thermostat were reading 66*. Don't charge for repairs only charge for trip charge.
I came out to look at an issue that has been occurring for a while, and found a fault in the control circuit system. Do to age of equipment Carla wants to replace the furnace.
In the kitchen the kitchen sink drain where the drain goes into the wall was leaking. I had to cut some wall out and cut the pipe in between the hubs to put in a new fernco. I tested by running water in both sinks. Everything tested good
Gave quote off of this dispatch - no charge
Install new 1/2 rpa backflow to dishwasher under 3 bay sink , certify backflow and send ppwork to water dept .
Upon arrival, the customer informed me that the outdoor unit was not operating and they thought that the capacitor had failed. After further investigations, I discovered that the problem wasnâ€™t the capacitor but within the wiring. I discovered that there were several loose connections. I presented options for repair to the customer and they did not want to make any repairs at this time. Thank you
Upon arrival, the customer informed me that the AC system was not working and that the outside unit was running but the air coming through the vents was warm. After further investigations, I discovered that the compressor was not operating. I tested the compressor and the ohm readings were 1.2, 2.0 and 2.9 and no windings were shorted to ground. I tried bumping the compressor with a hard start kit and the compressor ran. I removed the hard start kit and the compressor would kick on its own once again. I presented options for repairs to the customer and at this time they do not want to put money into a system that they believe the compressor could go out again at any time. The customer requested that I email quotes for compressor replacement and also would like to speak with a design comfort specialist. Thank you
Upon arrival found two thermostats not keeping up found one unit with large refrigerant leak repair bid available upon request or unit replacement bid as unit is 15 years old.