Our entire experience with LBA was perfect, from the person who set the appointment, to the sales technician, to the installers. The price was under what we were quoted by another company and they were far more attentive and helpful. Would definitely recommend!
good service. No complaints.
Our Technician arrived on time and was very professional and knowledgeable!
Needed to have a gas line valve modified and Doug did a great job modifying the original install. Completed the job very quickly and neatly.
Doug and Ed did a great job installing a new gas line for our new gas range. They did a thorough job and left everything neat and clean. The price was very fair compared to other plumbing companies we checked with.
On time and done quickly and completely.
Jose did an incredible job evaluating our system and recommendations.
Found problems, recommended new water heater. Installed same day , explained everything , fast and efficient.
Andrew did a treat job. Would recommend LBA and Andrew to anyone
I performed a safety and maintenance inspection on the Carrier AC system. During my inspection I discovered a few faults. First fault I discovered was the system is operating with refrigerant pressures outside of the manufacturers tolerance and it is nearing pressures that will cause the indoor coil to start freezing. The second fault I discovered was that the VEC tested outside of the manufacturers tolerance. Last fault I discovered was the OFM bearings have worn to the point that the motor shaft is allowed side to side movement. I spoke with the customer about my discoveries and concerns and due to the age and condition of the existing equipment and the cost of the appropriate repairs, I highly recommend replacing the equipment versus making the appropriate repairs. The customer didnâ€™t want to speak with Scott today as they wanted to speak with their family and look at finances before meeting with Scott. Todayâ€™s services were at no charge to the customer as it was part of the P3
Performed whole house plumbing inspection. Water pressure to home is 60psi Concerns and recommendations: Water heater is 14 yrs old. The average lifespan of a water heater is 8-12 years old. Older water heaters are more prone to failure. Recommend replacing heater before failure can occur. 1/2 bath lav sink is slow draining and the toilet flapper is failing. Recommend augering sink drain. Recommend replacing flapper.
Replaced condenser compressor motor. After performing swap out of compressor motor, the compressor refrigerant levels were up to manufacture specification temperature indoors is about 80Â° temperature coming out of supply 60Â°. Thatâ€™s 20Â° split before leaving the system slowly made it to 59Â° after an hour. The system will slowly go down in temperature temperature will drop a lot more during the night time. After waiting for temperature to drop started inspecting furnace. Notice that the board was calling for heating stage two but we are running an air conditioner. Seems like the main motherboard has a shortage or some type of water damage. Due to the fact that it is cooling I am not further inspecting the system. It is really uncommon for heating stage 2 to run during cooling mood
Performed maintenance inspection on both air conditioners. Checked all the electrical components. Voltage enhancer for the lower level air conditioner is weak on manufacture specifications. Recommended replacement. Customer stated that they have a home warranty to take care of any repairs.Check refrigerant for proper pressures and temperatures. Replaced air filters. Both air conditioners are cooling at this time.
Checked the split system for not keeping up in the afternoon. Customer informed that the space temp will go up too 75 degrees with a 70 degree setpoint. Found the air return temp high due to the return box not being sealed to the furnace allowing hot air from the warehouse to be sucked in around the box. Sealed the box to the furnace. Found the return temp 72.3 degrees after sealing from a 85 degree temp before sealing. Will have our sheetmetal department make a new return box to replace the existing one.
Upon arrival the customers water heater would light up and was 14 years old. The customer want to replace it with a 50 gallon gas water heater in its place. Also the customer asked if I could change out the humidifier saddle valve with at quarter turn valve which I charged the customer an extra $100. The customer asked about the veterans discount so I applied that to the pricing. I checked for leaks and everything tested good. Leaving a quote for the P3 agreement with the customer as well
Checked all the operations and found a fault in the safety system for the furnace. After making repairs upon customers request found that the system is almost completely out of refrigerant. Customer wanted to stop with repairs and look into replacement at this time.
Found that system was low on refrigerant and gave customer quote. He wanted to have system filled and get estimates on a new system
Performed cooling maintenance on system. Checked operations and safetyâ€™s. Changed filters in system. Checked system temperature split. System is operating within factory specifications at this time.
Placement of coil, adding refrigerant,deep vacuum and A performance analysis.
Estimate for two bottle filler stations.
Upon arrival found that there was no power to the outside unit and there was power coming out of the breaker box at this time. Recommended calling an electrician for repairs. Customer was aware that this should have been a chargeable But we will go ahead and waive charges tonight due to the customer just replacing both air conditioners.
Found that coil was completely frozen. Customer is letting it thaw out and having me back out tomorrow
Upon arrival found the compressor to not be engaging, condenser coil was completely clogged up and condenser motor was locked up due to overheating. After completely washing outdoor condenser coil and cooling compressor down found that the indoor coil was clogged causing the coil to knock out properly. Informed customer about issue customer chose a Band-Aid repair for Tomorrow.
Estimate for water heater. The home was designed to have a 50 gallon water heater. Both estimates include hauling off old heater