Technician Andrew Graves arrived at our home and introduced himself. Very friendly. He provided an action plan then executed. Afterwards he explained the root cause and we are very satisfied.
Jerry was very thorough and knowledgeable. We would highly recommend LBA!
He was polite and thorough. He went far above what the job required! Can’t say enough good things about him. If he represents the quality of your personnel, LBA is the most professional plumbing company in the area. I will highly recommend your company.
The hot water heater went out at our business on a Sunday morning. Doug was on it and have it all replaced by 11:00 AM. I strongly recommend LBA!
Satisfied with the service
Very professional and technically proficient.
Upon arrival, the customer informed me that their thermostat was displaying a fault code of flame present with gas valve de-energized. After further investigations, I discovered that there was minimal flames present after the gas valve de-energizing as shown in the video included. I tested gas pressure and found that the incoming gas pressure measured at 6.49â€ WC, low fire measured at 2.02â€ WC and high fire measured at 3.67â€ WC. The supply gas pressure was within tolerances but the manifold pressures were both slightly high so I adjusted them down to be within tolerances. After adjusting the manifold pressures, I found the Ruud U802VA furnace system to be operating within the manufacturers tolerances. I have included pictures and videos of everything as well. I spoke with the customer about renewing their membership with us and they would like to do so but would also like to wait as their membership is good until May 2020. Furthermore, we scheduled the customerâ€™s furnace tuneup
Checked all operations in the heating mode. Upon arrival found that the thermostat was not controlling the furnace properly after speaking with the customer we decided to replace the thermostat to allow the furnace to operate properly. Furnace filter was OK at this time left furnace filter for customer to change in the future. Cleaned out housing of furnace and tested all safety systems. The system is now operating within factory specifications.
I rode to find The system shut off to pressure switch failure. I cleaned out the port and the barometric tubing to the pressure switch and the system fired up. It is currently running and operating within factory specifications at this time. I suggest replacing the pressure switch and cleaning out the inducer motor housing if the problem occurs again.
Checked unit for dinning room for no heating. Found loose connections at W1. Tighten connections at W1 terminal and verified heating operation. The unit is heating normally now.
Checked all operations in heating mode. Clean that house in the furnace and housing of humidifier. Performed a gas leak search on all exposed gas piping. Performed combustion analysis on the furnace. Replace furnace filter with customer supplied filter. Replaced humidifier pad. System is operating within factory specifications. Customer does not have any CO detectors in the house recommended CO detectors. Customer was not interested in purchasing Co detectors at this time. Recommended outdoor maintenance in the future for the outdoor unit customer is going to look into maintenance agreement.
Installing a new tankless water heater do to the old tankless that is leaking water in the inside of it. Talked to tech support and they said it would need to be replaced.
Checked the tube heater over the bake fab area for intermittent noise complaint. Found the inducer motor with the bearings failing causing the complaint. Quoted the repair to the customer as requested. Blew out the inducer assembly and verified the unit was operating normal with the exception of the motor noise.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Performed a safety inspection on furnace, Upon arrival found system to be going off on a safety limit, hot limit switch closing electrical circulation. Gave customer options to solving problems. I would recommend changing settings on the board on the heating side. allowing right amount of time to go thru testing and make sure furnace does not fail again. Every adjustment requires testing. Customer declined said he would like another company to look at it Customer wanted a furnace tune up. Performed safety inspection of furnace, System was going off a high limit change the blower motor speed settings to high. Furnace didnt shut off when adjusting. Completely cleaned all safety switches and recalibrated. Safety switches performing to specifications. Indoor blower motor test, indoor blower motor is working to specification. Performed combustion analysis, combustion motor working within guidelines and properly pushing carbon monoxide out of the house. Performed a heat exchanger e
Homeowner doesnâ€™t want to cut exploratory holes in walls. Condo unit has main water shut off in parking garage.
Performed inspection on air handler, heat strips are performing to specification. Heat strips are reading to be running at 20 A and performing 18 amps that checks out great. System is heating properly with each individual heat strip. Air scrubber Uv lights burned out and no longer operating. Tested electrical wiring 240 v going to air handler secure and safe at air handler. Low voltage wiring stable and secure between thermostat and board. Low voltage wiring communicating properly. Perform an indoor blower test, The blower motor is running to manufacture specification. Based on my readings the system is performing to manufacture specification. Pat will be out on Monday to talk to customer about tankless water heater and adding a water softener .
Installed (1) 3 ton Trane rooftop unit. This installation included the following: â— (1) 3 ton Trane rooftop unit â— Crane to set new unit (21 ton) â— Hauling and disposal of old equipment â— Electrical connections â— Gas line connections â— Condensate drain â— Start-up and commissioning â— Hail guards $862 (add-on)
I was called out to check on two furnaces, the main furnace was having issues maintaining temperatures. Jackie change the batteries in the thermostat before I arrived and that seem to have taken care of the problem. I cycled on the furnace multiple times and it came on every time. I also checked both furnaces for cracks in the heat of strangers and was Unable to find any cracks or breaches in the heat exchanger. They appear to be in fairly good shape. I did notice that the filters are dirty and should be changed to help with airflow.
Upon arrival the customers master bathroom toilet was clogged and couldnâ€™t get in and unclog it do to the customer wheelchair being to wide. I had to use the plunger to get the clog out and I also cleaned it up for her when I was done. Just charging the trip charge and a additional diagnostic fee with no warranty. Everything tested good. I also told them about our P3 and she said they already got an agreement with someone else already.
Several estimates for work in basement All estimates include labor and parts needed as needed