Great service! Called late on Friday and they had a new disposal by noon on Saturday. I will be calling again!
The technician was really nice and took the time to explain any findings and suggestions.
Upon arrival found low voltage on twin Goodman furnaces for kids toys section. Isolated wiring and found low voltage short. Replaced burned & pitted voltage connection system on roof. Checked operations on system. System is operating within factory specifications at this time. Note** part is not covered within the 1 year warranty that the system had.
Performed five full cooling inspections. Washed and cleaned outdoor unit units. Checked all wires and safety switches. Greased all blower wheels that needed it. All unit are operating within factory specifications at this time.
Agreement that yard is good to go.
Upon arrival found thrown A50 belt replaced and added spare to the unit suggest customer clean filters for unit but found otherwise operational.
Removed low spot in main sewer line, installed cleanout in flower bed
Relocated sewer and marked
Installed Ruud furnace and AC and coil with zoning
Previous tech left unit off after left. Arrived turned unit on. Performed safety testing to ensure unit is operating properly. Unit is operating within factory specifications at this time.
Found that condensate was leaking, repaired insulation with foam tape, chemical cleaned unit and recommended zoning and system replacement
Completed cooling tune up, replaced voltage distribution system
Estimate for sewer sot repair
Upon arrival found unit for nursery running with a 23 degree split with an 83 degree return closed economizer damper and tightened belt/ adjusted pulley now running with a 19 degree split and a 80 degree return
Performed a full cooling inspection. Noticed that the system was extremely dirty proposed a extensive coil cleaning. Customer wanted to do an extensive coil cleaning. Performed extensive coil cleaning.Checked all wires and safety switches. washed and cleaned out outdoor unit. Also changed UV light bulb. Perform safety testing to ensure everything was working properly. Unit is operating within factory specifications at this time.
Completed annual cooling tune up, found that voltage enhancement system was testing below factory specifications, customer decided to have work performed, everything else tested as it should at this time. Thanks for having me out today, Eli