Great service! Called late on Friday and they had a new disposal by noon on Saturday. I will be calling again!
The technician was really nice and took the time to explain any findings and suggestions.
Completed cooling tune up, replaced voltage distribution system
Estimate for sewer sot repair
Upon arrival found unit for nursery running with a 23 degree split with an 83 degree return closed economizer damper and tightened belt/ adjusted pulley now running with a 19 degree split and a 80 degree return
Performed a full cooling inspection. Noticed that the system was extremely dirty proposed a extensive coil cleaning. Customer wanted to do an extensive coil cleaning. Performed extensive coil cleaning.Checked all wires and safety switches. washed and cleaned out outdoor unit. Also changed UV light bulb. Perform safety testing to ensure everything was working properly. Unit is operating within factory specifications at this time.
Completed annual cooling tune up, found that voltage enhancement system was testing below factory specifications, customer decided to have work performed, everything else tested as it should at this time. Thanks for having me out today, Eli
Kitchen drain slow
Installed new 50 gal water heater
Performed Furnace tuneup on train 80 percent furnace. Replaced blower motor capacitor and replaced filter.
Lennox preventative maintenance
Trance A/C not cooling. Remove a large mouse nest that was causing signaling issues for a home in Timber Park.
Maintenance tune up on a Lennox furnace. Found and replaced the failing capacitor.
Installing ISE COMPACT disposal
Perform heating maintenance and safety check out on two Trane furnaces. Also check out two April air humidifiers. All systems are operating properly at this time.