Good job friendly coved safe professional
On time and very pleasant to have in our home .
Arrived on time and acted professionally.
As expected. Would use again.
Both Austin and Noah were very professional, friendly and courteous. They gave us options which we appreciated. Every thing is working great.
Andrew and John were AWESOME!! Appreciate their work and how they explained everything to me. Will be requesting them when I schedule another appointment. Will definitely recommend them to others!
Eli was very professional and knew what he was doing.
Both Austin and Ed were very professional and efficient. Great customer service.
Installed bypass humidifier
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I checked your air filter and cleaned flame safety system. Performed humidifier tune up. Everything tested as it should at this
Checked all operations in the heating mode. Customer explained that house is very dusty and indoor air quality is not up to standards. Also explained the house is very dry. Spoke with customer about a new humidifier and indoor air quality products. Customer wanted humidifier replaced and an I wave air purification system installed. Installed I wave and will return January 14 of 2021 to install new humidifier. Replaced furnace filter and upgraded customer from a Merv 13 to a Merv 16 And did not charge the customer the difference. Cleaned out housing of furnace. Furnace is now heating properly.
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I checked your air filter and cleaned flame safety system. Everything tested as it should at this time
Upon arrival found that the air movement system had failed at this time. Also noticed that the system was extremely dirty. Replaced air movement system tested all blower speeds and cleaned out the entire furnace. Set up the humidifier at this time. Equipment is now operating within factory specifications.
P3 Furnace Maintenance Tuneup- Inspected thermostat, Inspected/Replaced air filter, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested all safety sensors, all sensors are operating correctly at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Performed humidifier maintenance, replaced water pad, cleaned drain line and inside of humidifier, humidifier is set for the winter. All heating ops are normal at this time. Customer is interested in possibly having either Iwave or Air Scrubber installed. Presented customer quotes and booklets on the Iwave and Air Scrubber. Customer Renewed P3 contract on todays call.
upon arrival I installed new hot and cold shut offs in the his and hers master bathroom sink. I also installed 2 customer supplied bathroom faucets and new p-traps in the same bathroom. I tested the for leaks and everything tested good.
Preforming quoted work tomorrow. Collecting trip charge today.
Upon arrival the the customers had a leak in there bathroom ceiling from the kitchen above. I had to cut the ceiling out to locate the leak. The leak was a cracked kitchen drain line. I cut out the old pipe and replaced it with new pvc. I tested for leaks and everything tested good.
Arrived to customers home Thursday, December 31. Customers upstairs master bathroom Jacuzzi tub having multiple leak issues. Upon further inspection found that cartridges in both handles of Jacuzzi tub faucet were leaking down water under handles. Customer also mentioned That while Jets were in use water would leak from connection on tub. Had customer fill tub and ran jets and could see leak on adapters going into Jacuzzi tub jets. Made customer aware that company does not work on Jacuzzi tub jets only Jacuzzi faucet. Customer chose to have both handle cartridges replaced as well as disassemble tub spout to clear up buildup of grime and hard water. Made trip to plumbing supply and matched manufacture cartridges. Return to home and removed trim from Jacuzzi tub faucet. Shut off water supply to tub. Removed both cartridges and replaced seats, Springs and cartridges. Cleaned up hard water debris inside of valve itself. Disassembled tub spout and removed from tub itself. Let tub spout so
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they are secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Filter was changed with one customer had on hand. We also spoke about types of whole home humidifiers. I suggested Scott our sales rep come and present options. Also spoke about duct cleaning. I recommend on all new homes that the ducts be cleaned. System is
Performed heating tuneup on Electric air handler. Checked heat strips amperage. Inspected all electrical components and electrical wires. Checked temperature split. Replaced air filter with customer supplied filter. Found some mold buildup around air circulation system and showed customer and recommended to install the Iwave R air purifier and customer accepted. Installed new I wave R, no other work performed at this time
Installed two air scrubber bulbs for uv air cleaners. This was prepaid on Friday. See invoice from then for information.
Ground floor Performed furnace maintenance. Replaced merv 16 filter. Completed all checks and cleanings. Checked supply and return temperatures for proper heating operation. System is heating and operational at this time. Performed a humidifier tuneup. Recommended replacing uv blub due to the age of the bulb. Customer approved uv bulb replacement. Main floor: Performed furnace maintenance. Replaced merv 16 filter. Completed all checks and cleanings. Checked supply and return temperatures for proper heating operation. System is heating and operational at this time. Recommended replacing uv blub due to the age of the bulb. Customer approved uv bulb replacement. Recommended installing steam humidifier to increase the humidity inside the home to optimal humidity levels. See estimates for pricing. Upstairs: Performed furnace maintenance. Replaced merv 16 filter. Completed all checks and cleanings. Checked supply and return temperatures for proper heating operation. System is heating a
Camera and estimate for sewer repair