Have used LBA for years.
Nathaniel was very professional and did a great job.
Sump pump installation was accomplished in a timely and professional manner with courteous technicians.
Pat was very professional and informative during the inspection. It’s always a relief when a knowledgeable expert will tell me the truth in detail w/o trying to sell something I don’t need. Our waste pipe was very old, cast iron, and never been opened so the cap broke off w/o much effort. It wasn’t his fault, but he stuck around to have the part delivered, cleaned off the remaining residue, and put on a new plug cap. I’m very happy with the service and will definitely call LBA again for any plumbing needs in the future.
Jerry was polite and knowledgeable!
I replaced the rotted out flue pipes and connections for the water heater and pool heater. I turned on the water heater and checked the flue draft- 0.03â€ w.c.
Carrier RTU system not cooling properly. Found the 50mfd run capacitor to have failed. Capacitor has been replaced. Unit is cooling properly at this time. Unit found leaking condensation from the supply duct. Found condensation blowing over the drain pan directly into the supply duct. Modified the evaporator drain pan with a sheet metal lip to catch condensation and drain properly into the pan.
Estimate for Halo 5 whole home water conditioner
Estimate for backwater valve
Arrived to find that the furnace switch was in the off position. I restored power to the furnace and the system turned on. While I was here, I took care of the spring AC tuneup and inspection. During inspection, I installed suction line insulation to help the systems efficiency and chemical washed the outdoor coil to maintain the systems performance and efficiency during peak demand times. To prevent the furnace power from being accidentally turned off, I also relocated the furnace switch from the side of the furnace to the floor joists above the furnace.
Checked the two Rtus for the space for operation after a single phasing condition from the building power supply. Found the East Carrier unit running normal on first stage. Jumped the second stage and verified operation. Restored power to the West Lennox unit. Found the blower overload tripped holding off the unit. Reset the overload and verified operation of all stages and compressors.
Checked the South paint booth for no heat. Found no call to the flame safeguard due to the combustion blower presure switch being open with the combustion blower on. Cleaned the pressure switch and sensing tube. Pulled the pilot assembly and cleaned the flame rod and pilot while on site. Verified operation after repairs.
Ran camera in sewer from clean out in basement. Line is in very good condition
I conducted a performance and safety inspection for the air conditioner. I found the system to be operating properly and safely at this time. I chemical washed the outdoor coil to maintain the systems performance and efficiency during peak demand times.
Removed leaking heater in pump room behind spa , installed new 50 gallon heater with expansion tank and piping , all flue exhaust piping is rotted out from pool heater and water heater , hvac tech will return tommorow to replace all the flue piping . Heater was left filled , but unlit .
Installed new 10â€ frostproof hydrant in rear of home and tested for leaks. Also found second defect in 2â€ abs line next to hose bib, and repaired at no charge to customer( we were out on July 2 for that repair).
I conducted a performance and safety inspection for the air conditioner. I found that the system is operating within factory specifications. I chemical washed the outdoor coil to maintain the systems performance and efficiency during peak demand times.
Follow up visit to pressurize 1â€ pvc line for sprinkler and bury.
Upon arrival customer stated he needed a water source for filtration unit for kitchen sink. Found unit canâ€™t be hooked up to plumbing system without going threw kitchen faucet.
Upon inspection found the it room cooling properly with over a 20 degree temperature split. The room was 66 degrees when I arrived. There were no error codes on either of the cooling units. I sent David Guzman pictures of the room temperature. No problem found at this time.