John Sutter was super awesome rebuilding my kitchen faucet and saving me $$$! This is why LBA is my “go-to” for my home repairs!!!
Have used LBA several times over the years. Always very professional, very skilled, courteous. Pricing is very fair. Would recommend higly.
Kent and his trainee Nathaniel did a very nice job. Kent was quick to diagnose the problems at hand and then they made the necessary repairs. Unfortunately my old pipes are not as good as the plumbers. There is more work to do later. Plumbing is not cheap so use the coupons on their website.
Angelena was a very knowledgable plumber that gave great advice to a new homeowner.
The technician did a great job and gave us some tips on when to change filters, etc
Nick Larkins is AWESOME - knowledgeable & professional
I replaced the old sump pump with a pro series sump pump in the basement. I tested with water and everything tested good.
Upon arrival the customer informed me that the mini split system we installed a few weeks ago wasnâ€™t heating as it should. After further investigations I discovered that there was a leak on the liquid line at a flare connection where the line set meets the head unit whip on the exterior of the home. Jesse brought out a torque wrench to properly tighten the connection and the leak was resolved. We pulled out the remaining refrigerant and put in new refrigerant which was measured in at 2 pounds 5 ounces. After completing the repair the mini split system was operating as it should within the manufacturerâ€™s tolerances. There is no charge for todayâ€™s service as it is covered under our workmanship warranty. Thank you
I arrived to find that the furnace was locked out on limit switch open. I reset the furnace and tested heating operations. I found that the air circulation component was bad and causing no airflow through the system which in turn was causing the furnace to overheat and shut down. During my inspection, I also found that the evaporator coil has a lot of dirt and debris build-up causing an Air Flow Restriction. Given the age and condition of the system, the customer would like a design specialist to come out and quote new equipment pricing.
9-16x25x2--1-20x20x1--1-18x20x1--1-16x20x1 all pleated from our warehouse--18-20x25x2 pleated per PO #34706543-101--Performed the Pm on the cold deck and the electric reheat boxes. Details in the checkout sheets.
Arrived to find both systems operating properly. Attic unit is just an ac and air handler. System is working properly. Systems are operating properly at this time.
***gas leak at gas valve on hot water tank*** I performed a safety and maintenance inspection on the furnace. At this time I found everything to be operating within the manufacturers tolerances. During my inspection, I did however discover a gas leak at the gas valve body providing the hot water heater. I brought my concerns to the customer and they informed me that they were given a quote from LBA by Pat back in May this year for a hot water heater replacement. I encouraged the customer to call in to verify that the given quote was still a correct price for the job and to schedule the replacement of the hot water heater.
Helped john on pan notes on john ticket
Performed a full heating inspection. Checked all wires and safety switches. Cleaned unit and all safety switches. Performed a heat exchanger inspection. Heat exchanger passed inspection. Unit is operating within factory specifications at this time.
Checked all operations in the heating mode for both systems. Performed a humidifier tuneup cleaning out housing of humidifier and replacing humidifier filter. Checked all safety systems in the furnaces. Replaced both furnace filters with LBA supplied filterâ€˜s. Cleaned out housing of furnaces. Performed a whole house gas leak search and found a gas leak at the old valve shut off replaced valve with coupling because each appliance has its own shut off. Relit water heater. Systems are now operating within factory specifications.
Quoted the customer on a expansion tank on the water heater and a new prv on the main water line. The water psi is 110 and I canâ€™t warranty the inspection do to the high water pressure in the house.
Found vav box in vacant space stuck on as pressure control was slightly out of calibration adjusted to proper pressure and unit is now off.
Checked all operations in the heating mode. Performed a combustion analysis as well as checking the carbon and oxygen levels. Cleaned off blower wheel as well as the furnace itself. Spoke with customer about humidifier tune up which customer wanted to do at this time. Also asked customer if they would like to join P3 agreement which they did not to do so. Furnace filter was changed with customer supplied furnace filter. Furnace and humidifier are operating within factory specifications at this time. Nice meeting and talking to you
Upon arrival found motor starter for RTU blower motor had tripped due to power surge earlier in the day reset and unit is now operating well.
Upon arrival found RTU's receiving improper voltage to the units shut them off and traced electrical back to panel to find power company remedied the problem and the power came back on checked to make sure rotation was correct on all compressors and fans found operating well at this time.
Found refrigeration system failed on the outdoor unit. Went through system. Customer was given prices to repair system. Will go over prices with husband.