Quick & Thorough A/C service maintenance check from Eli at LBA!
Called on Saturday morning with a plumbing issue and LBA was able to set up an appointment the same afternoon. Doug took great care of the initial issue and was able to set up follow-up appointment for next Monday. Great experience so far.....
John Sutter was super awesome rebuilding my kitchen faucet and saving me $$$! This is why LBA is my “go-to” for my home repairs!!!
Have used LBA several times over the years. Always very professional, very skilled, courteous. Pricing is very fair. Would recommend higly.
Kent and his trainee Nathaniel did a very nice job. Kent was quick to diagnose the problems at hand and then they made the necessary repairs. Unfortunately my old pipes are not as good as the plumbers. There is more work to do later. Plumbing is not cheap so use the coupons on their website.
Angelena was a very knowledgable plumber that gave great advice to a new homeowner.
Performed heating maintenance on 12 heat boxes. Changed all filters and greased rooftop air handler.
Performed planed maintenance as contract states. All systems are running at factory specifications at time of departure except for the units that have been discussed with Michel. Kellen is making quote for those. Nothing further at this time.
Front door was still locked. Customer couldnâ€™t get home to unlock the door. Customer will need to reschedule.
Upon inspection found very dirty filter, due to the dirty filter the air flow was restricted causing the system to overheat. Replaced filter and cycled the system a few times to verify heating ops. System is now heating normally. Customer supplied filter.
Arrive to customers home Friday, October 23. All home plumbing inspection. Water heater one-year-old. Water pressure at hose spigot 80 psi. During inspection found the water heater is not venting properly and show signs of plastic warping on top of water heater. Provided knowledge and estimate for power vent water heater to customer. Customer also has leak on galvanized piping coming in for main water supply to home. Pat was able to come by job to give estimate to replace water piping from meter in yard into home with new copper piping. Other issues found while doing inspection were that hot and cold stops for kitchen faucet are seized and do not turn as well as stops in upstairs master bathroom for lavatory faucet and toilet are seized as well. Thank you for choosing LBA have a wonderful day
Estimate for water line
Arrive to customers home Thursday, October 22. Customers main concern was toilet in main floor bathroom. Toilet was leaking from bottom of toilet whenever flushed. Customer chose to replace wax ring of toilet. Shut off water supply to toilet then polled toilet off of flange. Removed old wax ring and replaced with new wax ring to be able to seal properly to flange. Reset toilet onto flange and connected water supply back to tank. Flushed toilet multiple times to ensure no leak. Toilet is now functioning properly with no leaks at this time. Thank you for choosing LBA have a wonderful day.
Upon arrival customer took me to the basement bathroom were toilet was leaking from supply. I replaced supply with new and checked for leaks.
Performed maintenance inspection on a Lennox furnace. Checked all the electrical components and safeties for proper operation. Checked combustion one the flue. Both furnaces are operating under manufacture specifications.
Arrive to customers house Thursday, October 1. Customer having issues with foul smell and garbage disposal as well as in dishwasher in first floor kitchen. Kitchen drain is tied in with corrugated drain line and back grades slightly. Suggested to customer to have kitchen drain repiped to have separate traps on basket strainer and garbage disposal and to properly grade piping. Customer went with Band-Aid repair where in trap and drain were disassembled and cleaned out. Also made high loop for dishwasher discharge drain line to prevent dirty water back feeding into dishwasher. Pulled dishwasher out and drilled new holes for drain pipe. Tied in and re-assembled drain line for kitchen sink and disposal. Tested kitchen drain and put ice in disposal to help clear any buildup of foul food. Tested dishwasher as well to ensure dishwasher pumped out properly and all fittings were leak free. Dishwasher is functioning properly at this time along with no leaks in kitchen sink drain lines. Tha
At time of arrival customer stated his unit heater for downstairs was not coming on on pilot mode. Before I began troubleshooting he tried it again and system came on and held on pilot mode. After he saw it kick on he decided to just pay for a trip charge since it is running at this time
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed humidifier tune up, performed combustion analysis, checked for proper heating transfer, changed humidifier panel, everything tested as it should at this time, thanks for choosing Lba, Eli
Checked air filter, took heat rise, performed combustion analysis for O2 levels in the fluegas, CO levels in the fluegas, and fluegas temperature, cleared clog in the secondary heat exchanger condensate drain, clean the flame sensor, pulled and cleaned the burners,Polled and clean the Blower motor, inspected heat exchangerâ€™s.Cleared the condensate drain, took temperature drop, clean the condenser coilâ€™s, checked all electrical components, tightened all electrical connections, checked the systems refrigerant levels. AC and furnace are working properly at this time.
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I check your air filter and cleaned flame safety system. Everything tested as it should at this time
Upon arrival the customer sump pump in the finish basement wouldnâ€™t come on and pump the water out. After presenting pricing the customer chose the silver options and I installed a new sump pump. I tested it by letting the water in the in the pit get pumped out. Everything tested good