On time. Clear explanation of problem. Solution done quickly.
Service reps were very helpful and hood at explaining the situation.
Kaden was professional, romper and very knowledgeable.
personable young man. Explained the work done well
Nick did a great job solving our lack of water pressure in a bathroom sink faucet. Happy with speed of response and price. Nick is very professional
Noah was very professional and efficient getting our plumbing situation up and running again!
Austin told me what he was doing and why during installation which was very helpful and gave me confidence in what he was doing.
HVAC Maintenance Service near Alhambra St. We visited a residential client's house to carry out essential seasonal maintenance on their HVAC system, ensuring optimal efficiency regardless of the changing seasons. Conducting a comprehensive diagnostic tune-up, we thoroughly examined the system for any potential performance issues and replaced the filters to maintain proper airflow and indoor air quality. After a thorough inspection, we found no indications of weakness or issues within the HVAC system. The client can now enjoy peace of mind, knowing that their HVAC system is in excellent condition and ready to provide reliable performance.
Arrived to call for moisture leaking from underneath the furnace. Upon inspection I found the condensation drain fully clogged with debris and the evaporator drain pan over filling. I went over the repair of clearing the condensation drain with the customer and replaced the air filter with truck stock. Once finished I checked for proper temp split and static pressure. I spoke about our membership and how we flush this drain and clean the outdoor coil during our maintenances. Customer will clean the outdoor coil himself. System running upon departure.
Arrived to HVAC out call. Upon arrival I spoke with the customer who showed me the location of the furnace, ac, and corresponding thermostat. At the indoor unit we found the blower operational but no cooling happening. At the outdoor unit the compressor and fan were on. After hooking up gauges I found the system empty of refrigerant. I performed a leak search finding a leak on the refrigerant suction line. After this I went over repair options with the customer which included repairing the leak, removing all non condensables from the refrigeration system, and re charging with refrigerant. Customer would like to speak with her husband before the work is performed. Disconnect off upon departure.
Checked all operations in the cooling mode and inspected the furnace filters. Filters were dirty and replaced. Checked the static pressure of both systems and found that the American standard system had high static pressure. Checked all electrical and refrigerant components at the outdoor units. All electrical and refrigerant components were good at this time. Systems are operating properly at this time.
Estimates for todays inspection
Arrived at customers home Wednesday, May 10, 2023. Hall home plumbing inspection. Water heater less than two years old. Flushed water heater and some sediment was removed from water heater. During inspection found multiple issues that were brought to customers attention. Mostly pertaining to old drain lines in home. Kitchen sink drain line is original cast iron for portion behind it cabinet upstairs down to ceiling in basement. Also made customer aware of hard water damage. Customer also has instant hot on kitchen sink that they rarely use and was interested in swapping it out for a reverse osmosis. Estimates for all repairs will be included in a separate invoice. Thank you for choosing LB a have a wonderful day
Upon arrival I found that the system was operating and getting a twenty degree split. I checked static pressure and found that the system has high static pressure. I checked everything at the outdoor unit and found that the unit was extensively dirty which was the cause of why it was not cooling as well. Upon customer approval we preformed a extensive cleaning and got them on the new maintenance program. System is operating properly at this time.
AC maintenance. Checked all task. Rudd system did have bad capacitor and all three systems needed extensive coil clean as well as the upstairs, Lennox unit and the Rudd system would benefit from having a kickstart installed like the downstairs Lennox unit. Customer approved of everything went ahead and got that all done.
5-2-23 Tue Per the quote Sam and I installed new blower pillow bearings on the engineered air cold deck unit. After install replace the existing belts and blower pulley. Ran the unit for approximately half hour, then checked the blower amps Rated @ 29.5amps and running @ 18 amps. Check the motor casing for any overheating. Also, check the bearings for any overheating system is working properly at this time. I will do a follow up check tomorrow morning. Install new door handle assembly for the evaporator coil access door. Found during the spring tune up Front and rear lower wheel pillow bearings grease seals are bad. One door handle broken. Quote to replace front and rear blower wheel pillow bearings and one door handle. Price includes the factory replacement parts and labor. Part prices include the customers 10% discount per their pm contract. The unit will be down during the repairs resulting no air flow or cooling. Price does not include work outside of normal business hou
Arrived to do a dual performance maintenance. Turned on the air conditioning systems at their respective thermostat. Measured the temperature split between return and supply air for each separate system. Performed a static pressure test to ensure each system has the proper air flow. Found that both systems are operating beyond their maximum rated static pressure. Each system is rated for .5 IWC and are performing much higher than that. Homeowner would like to meet with a supervisor to receive solutions on the static pressure issue. Set the appointment for Wednesday between 12 and 4. Used inspection camera to check the heat exchangers and evaporator coils. Measured power consumption of the blower motors and checked the system filters. Found that the blower wheel for the newer furnace is heavily coated in dust and debris. Checked the outside coil for cleanliness and excessive vibration. Measured power consumption of the compressors and condenser fan motors. Verified performance of all me
Checked all operations in the cooling mode and inspected both furnace filters. Both filters were dirty and replaced. Checked the static pressure of both units and found that they both have high static pressure. Checked all electrical and refrigerant components. Today I found that the older R-22 system was low on refrigerant. Due to the age and condition of the system customer will look into replacement of the system. The slightly newer ac is operating properly at this time. A supervisor will be out tomorrow to evaluate the ductwork and price out a new ac system.
Completed AC tune up. Refrigerant charge is in range. All electrical components tested in manufacturers specifications today. Temperature drop is good. Customer will replace air filter. Cleaned outdoor coil. Thank you for choosing LBA services. Your technician today, Jake.
Arrived to do a performance maintenance. Turned on the air conditioning system at the thermostat. Started inspection with the furnace. Measured the temperature split between return and supply air on the system. Performed a static pressure test to ensure the system has the proper air flow. Used inspection camera to check the heat exchanger and evaporator coil. Found bacterial growth present on the evaporator in the basement. Measured power consumption of the blower motors and checked the systems’ filter. Continued maintenance on the outside units and checked the coils for cleanliness and excessive vibration. Measured power consumption of the compressors and condenser fan motors. Verified performance of all mechanical and electronic components. Verified systems refrigerant charge. Found that the capacitor fan side was bad. Proposed capacitor, as well as relocating the disconnect due to it not being code. Also proposed a Uv bulb and filter to protect against mold build up. Replaced capaci
Company came out for annual plumbing inspection. Everything looks good besides hard water. Company gave a few options to solve hard water issues. Thank you for using LBA services, Jake
Company arrived Thursday, April 20, 2023 to perform plumbing inspection. Upon completion of inspection company found that there are six gate valves that need replaced with quarter turn ball valves. Company found water heater is five years old recommending anode rod replacement. Company found the trap nut is broken on the downstairs sink. Company found washer hook ups need replaced. After discussing with customer, no action is chose to be taken. Thank you for choosing LBA.