Nathaniel was super kind and got my backed up sewer drain opened. He provided “knock your socks off” service in a very challenging environment! A+++++
Quick & Thorough A/C service maintenance check from Eli at LBA!
Called on Saturday morning with a plumbing issue and LBA was able to set up an appointment the same afternoon. Doug took great care of the initial issue and was able to set up follow-up appointment for next Monday. Great experience so far.....
John Sutter was super awesome rebuilding my kitchen faucet and saving me $$$! This is why LBA is my “go-to” for my home repairs!!!
Have used LBA several times over the years. Always very professional, very skilled, courteous. Pricing is very fair. Would recommend higly.
Ran camera in sewer Estimates for spot repair and burst replacement No guarantee on sewer there is a known defect
Upon arrival the customers main line was backing up. I had to cable the line through the cleanout in the garage. I went all the way out and brought back roots on my cable.
Customers main garbage disposal locked up and stopped working (Not the same disposal company worked on before). Customer wanted a replacement that was same horsepower or equivalent as original one, so company installed new Pro 1100 xl insinkerator 1 horse power. Customer also requested company to leave original strainer hook up for garbage disposal it being a special color (white). Company also cleaned out p traps with installation of garbage disposal. After installation was complete company tested for operation and everything is testing properly at this time. Customer will have one year warranty on garbage disposal installation itself. Thank you for choosing lba and have a wonderful day!
Performed heating tuneup on both furnaces. Inspected both air filters. Checked temperature rise on both systems. Serviced both humidifiers and replaced water panels. Inspected both heat exchangers and both furnaces are still in good condition. Performed combustion check on heat exchangers and very thing tested within manufacturers specs. Both furnaces are running within manufacturers specs at this time. No other work performed, customer renewed p3 membership
Checked all operations in the heating mode. Performed a combustion analysis. Cleaned entire safety system. Customer takes care of furnace filter which was OK at this time. Spoke with customer about a humidification system and adding a pumping system to get rid of a long drain that stretches across the basement floor. Emailed customer options upon repairs. furnace is operating properly at this time.
Estimate for hot water recirculating pump There is also a water leak outside. Homeowner is going to check with irrigation company first before going to water line replacement
Upon arrival found thermostat had failed. Inspected all low voltage wiring. No issues found with any connections or wires. Replaced thermostat with new Aprilaire wifi with a backplate to cover hole and paint on the wall. Walked through setup of WiFi with Ellen. Tested operation. 1 year warranty.
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections and ensured they were secure and not rubbing. Humidifier is on and draining properly. Set humidistat to 40%, customer was complaining about dry air. Humidifier will need serviced next heating season. Performed a combustion analysis on the heat exchanger and found zero issues. Replaced filter (20x25x1). Furnace is running safely and within manufacturers specifications at this time.
Customers floor drain was backing up while washer was in use. After running a series of test. Company Determined line was partially clogged after floor drain. Company renewed customers P3 agreement and gave $88 drain line special. After cabling line multiple times company finally was able to open line itself. Both kitchen and laundry are tied into old 3 inch line that is too big in size for amount of water running through kitchen and laundry causing sludge throughout the whole line. Company was able to open line but due to the amount of sludge company cannot warrantee line itself. Recommended to customer to jet line or replace the line itself going to main. Customer requested for drain specialist to come out and get bid on replacing line itself below floor going to main sewer.
Found that humidifier water was turned too high causing water to leak down return duct work. Adjusted water pressure and everything tested as it should at this time
Upon arrival the customer master bathroom sink wouldnâ€™t drain fast when water was being ran. I had to cable the line and clean the stopper off for the sink not to back up. Customer had $50 online coupon and everything tested good.
P3 Furnace Maintenance Tuneup- (Main Unit) Inspected thermostat, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested the voltage enhancement system, tested/cleaned all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- heat exchanger shows some rust, no cracks or holes are visible, heat exchanger appears to be safe at this time. Vacuum/Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Performed humidifier maintenance, replaced water pad, cleaned drain line and inside of humidifier, humidifier is set for the winter. All heating ops are normal at this time. Additional Furnace Maintenance Tuneup- (Master Bed Unit) Inspected thermostat, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested the vo
P3 Furnace Maintenance Tuneup- Checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested the voltage enhancement system, tested/cleaned all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- heat exchanger shows some rust, no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Pressure switch is beginning to fail, this could be a potential failure this winter. All other heating ops are normal.
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they were secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Filter was good and replaced just a week ago. Customer had inquired about some issues with the furnace not working every time it came on. Tested it multiple times and sounded like a venting issue. Inspected the inlet and exit point of the flue on the side of the garage. Found a leaf stuck on top restricting some of the inlet air. Also found stagnant water in the exhaust flue in the garage. I cut into the exhaust and drained the excess water. After repaired flue I adjusted the pitch of the pipe to fall back to the furnace. Furnace is running safely and within manufacturers specifications at this time.
-Send Rick Lower level heat box #3 needs diagnoses. Fan is not running. Found the blower motor failed. Upstairs in Great Plains office, the heat box unit in the file room needs to be looked at to see if fan speed can be adjusted. Some areas are getting to hot and closing dampers would result in increased air flow elsewhere. Ajusted the dampers and removed a 8" cap from a supply to dump air above the ceiling. Michelle requested that we look into the cause of a fan noise in her office. You can hear the fan start up and slow down intermittent. Replaced the failed pneumatic thermostat. Repairs were approved by Michelle M.