Furnace was making noise on start up. Replaced blower. Could not hear the noise upon testing with the service tech. Noise returned 30 mins after tech left on furnace start up. I went and turned off the humidifier on the furnace which eliminated the noise. Blower was old but not the problem.
Service guy never went over the details or results of the ac checkup. Just had me sign the service contract and he left.
Mike Shelor of LBA did our Summer HVAC Inspection and Tune Up and did an AWESOME job.
Mike, the service technician that came to our home and corrected our HVAC problem was knowledgable, competent and very personable. LBA personnale are the best.
From the customer service representative that answered the phone to the technician that handled our HVAC issue, they were the BEST!
Upon arrival I found the blower motor getting power to the motor but it would not turn. Blower motor has failed electrically. Jeff gave me a authorization to replace the blower motor. After installing new blower motor I test of the unit and it is operating as designed and has a temperature split that is in tolerance.
Checked the Reznor gas fired heater for the outlet side of the detail bay for no heat after the inducer motor and wheel was replaced. Found the time delay and pressure switch failed. Explained the extra repairs needed to Cameron the manager in charge. He will get back with us if they want to proceed with the repairs.
i Performed the repair of replacing the inducer motor. After the repair there was an additional issue with the unit. I did some diagnosing and was not able to complete diagnostics. I will tell the office we need to someone to finish diagnostics.
Performed PMA. Checked all electrical components, mechanical components, tested heating functions, replace air filters. Found no issues at this time. For further information please see the checkout sheet.
Performed a full heating inspection. Checked all wires and safety switches. Cleaned indoor unit. Also performed a full humidifier inspection. Replaced humidifier filter and checked all wires. Both the furnace and humidifier are operating within factory specifications at this time.
***air movement system faults. VEC testing outside of tolerance and blower motor bearings failing allowing the motor shaft to have side to side movement*** ***heat exchanger looking at the front of the furnace the fourth chamber from left has heavy scorch marks but no breeches at this time*** I performed a safety and maintenance inspection on the furnace system. During my inspection, I discovered two faults within the air movement system. The voltage enhancement component tested outside of the manufacturers tolerance and the blower motor bearings are failing allowing the motor shaft to have side to side movement. I spoke to the customer about my concerns and presented repair options. Due to the age of the equipment, the customer is planning to just replace the furnace instead of making repairs. The customer called Scott to get an idea of what new equipment costs would be while I was onsite. The customer is looking to replace the furnace this oncoming spring. Todayâ€™s service is at n
I performed a safety and maintenance inspection on the furnace system. I found the furnace system to be operating within the manufacturers tolerances at this time. Additionally, the customer purchased a humidifier tuneup today which I also found to be operating within the manufacturers tolerances. Furthermore, the customer renewed their P3 membership today choosing the annual non-recurring standard P3 membership plan. Todayâ€™s tuneup was owed from last years agreement so as of 1-7-20 the customer still has all three visits included in the membership available to them. Thank you
Upon arrival I found both muaâ€™s for the interior cleaning bay to not be operational. After diagnosing both units I found one of them to have dead batteries in the thermostat. The other unit had a inducer motor that the bearings failed in and are not allowing it spin freely. I am waiting for a call back from the part distributor for availability and price on the part. Once I get a call back I will create a quote for the inducer motor replacement.
Arrived to find steam humidifier extremely dirty. Performed maintenance on system. Replaced cartridge. Cleaned unit. System is operating properly at this time.
Installed owner furnished Kemco Boiler. This installation included the following: â— Boiler drain â— Removal of existing equipment â— Set new boiler in place â— Boiler assembly â— New boiler piping â— Isolation valves (up to 6) â— Gas line connection â— Flue installation â— PVC for intake air â— Controls connection â— Auto fill system â— Holding tank installation â— Start-up and commissioning
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, found that inducer motor was failing, everything else tested as it should at this time, thanks for choosing Lba, Eli
Arrived to perform bandaid humidifier install. Installed new humidifier and humidistat. Performed safety testing to ensure no leaks and the system is operating properly. Units are operating within factory specifications at this time.
The direct fire burner for the car wash tunnel was heating at 150 degrees when I arrived. I tested the functions of the unit found no issues. However the ignition process turn the burners takes about 20 seconds. So if we only send one car through the tunnel at a time that car was barely getting any of that heated air blowing on it, so I had Cameron speed up the timing for the blowers to kick on. This allowed the burners to fire right when the car come into the drying room.
Checked all operations in the heating mode. Cleaned out housing of furnace and cleaned all safety sensors at this time. Performed combustion analysis on furnace. Replaced furnace filter. Found the voltage enhancement p system for the furnace to be out of factory specifications at this time. Customer was not interested in making repairs this time emailed options to customer to have. Found the humidifier to be un operational at this time after speaking with the customer customer decided to replace instead of repair. Collected in full for that today will perform the install 12/17 of 2019.
Checked the tunnel exit direct fired heater for not warm enough complaint. Found the unit firing normal with a discharge temp of 140 to 150 deg. Watched the unit cycle from the wash bay controls with a variable flow of traffic thru the bay. Found the air flow switch with a intermittent delay of closure causing a delay in the burner firing resulting in discharge temp fluctuation. Ajusted the air flow switch. Verified proper operation after ajusting. Explained the repairs to the manager on site.