Was afraid we were looking at a sizeable
Mike Shelor our LBA Technician is awesome. He has Great knowledge and very professional.
Really can't say enough good things about Austin, the plumbing tech. who helped us today: Knowledgeable, patient, thorough! He made short work of what was a miserable issue for us, and was so professional and kind. Thanks LBA for always sending quality people, we count on you for that.
Furnace was making noise on start up. Replaced blower. Could not hear the noise upon testing with the service tech. Noise returned 30 mins after tech left on furnace start up. I went and turned off the humidifier on the furnace which eliminated the noise. Blower was old but not the problem.
Apon arrival I performed a yâ€™all cooling tune up. I found that the voltage enhancement system was testing under factory specifications and I gave customer estimates but she stated she would go over options with her husband. Everything else tested as it should at this time.
Found leak on equalizer connection. Fixed leak and recharged system everything tested as it should
Cause of problem was leaking Schrader leaked all the refrigerant. Replaced failed stem and recharged a/c.
Installed txv due to failure. Everything tested as it should at this time
Replaced vessel sink and faucet. Customer supplied. Checked for leaks
Today I completed your annual cooling tune up. I tested all electrical and found that your voltage enhancement system was testing under factory specifications, I gave customer estimates and they decided to go with the silver repair. After repair was made everything tested as it should at this time. I checked filter, tested refridgerant and cleaned system, thanks for having me out today, Eli
Estimate to replace sink and faucet
Upon arrival the master bathroom sink was installed incorrectly by a handyman and was corroded between the granite top and the bowl. I talked to my manager and he recommended that the customer goes out and buy a new single handle faucet and bowl assembly. They would need to call us back and have some give a proper bid on replacement. Collecting trip charge.
Apron arrival I found that the system was low on refrigerant. After performing leak search I found that the leak was on the heat media transfer coil. I gave customer estimates and he decided to go with the gold option. I filled system with refrigerant and made electrical repairs today and scheduled for coil install to be done friday
Inspected leak coming from the the space inside the ceiling tiles. The leak is located external from all duct runs and condensation lines. All duct runs are insulated to prevent leaks. Inspected the unit and roof for any leaks. Could not find any visible leaks coming from then unit. Inspected all duct runs Leak and line sets, leak is entirely external from the unit. Would recommend to have a certified roofer inspect the roofing membrane for leaks.
Repaired refrigerant leak at 3/8 liquid line solder joint located at evaporator coil inlet. Unsolder joint, replace small section of 3/8 piping, replace liquid line drier, solder connections, pressure test , evacuation below 500microns, and recharge system. The unit is cooling properly now
Perform refrigerant leak search on condenser #2 . Located refrigerant leak with electronic leak detector. The leak is on the 3/8 solder joint at inlet on evaporator coil. The joint will need to be unsoldered, cleaned and redone. The 3/8 liquid drier will also need to be replaced.
Wasn't able to access space. Jumped trane unit and it operated normally. We need to return tomorrow to determine exact number of units. Returned 6-9-20 to finish diagnostics. Discovered Honeywell pro 8000 thermostat send signal for heat and cooling causing system to struggle to maintain cooling set point. Informed Erin of findings and she got approval from Katie to replace thermostat. Replace thermostat and confirm cooling operation the unit is cooling probably now the temperature split is 20Â°.
Bronze level rebuild in hallway bathroom replaced fill valve, flapper, supply, and emergency stop. Also cleaned out p trap free of charge. After tested P-trap and toilet by running water multiple times everything is testing OK at this time. Also notified customer basket strainer on left side of sink was loose if customer starts to have leak recommend replacing basket strainer itself. Thank you for choosing lba and have a wonderful day!
Removed both blower housing in twinned Lennox furnaces disassembled and cleaned. Reassemble blower housing and reinstalled. The blowers are operating normally. Also replaced run capacitor for furnace #1. Notice loose internal connections in control board on #2 furnace. The control board is working normally now but may need to be replaced in the future. A.c. #2 isn't cooling has much as it should be and was starting to freeze up this morning when I arrived. I check refrigerant pressures and found the unit low on refrigerant I shut this unit off to prevent any damage to system due to low refrigerant charge. Unit #2 may have a refrigerant leak and needs a leak search to pinpoint source of the leak.