Austin did an outstanding job!!! He went above and beyond!
Was afraid we were looking at a sizeable
Mike Shelor our LBA Technician is awesome. He has Great knowledge and very professional.
Really can't say enough good things about Austin, the plumbing tech. who helped us today: Knowledgeable, patient, thorough! He made short work of what was a miserable issue for us, and was so professional and kind. Thanks LBA for always sending quality people, we count on you for that.
Furnace was making noise on start up. Replaced blower. Could not hear the noise upon testing with the service tech. Noise returned 30 mins after tech left on furnace start up. I went and turned off the humidifier on the furnace which eliminated the noise. Blower was old but not the problem.
Performed maintenance and safety inspection on furnace. Performed heat exchanger test and it passed. Replaced humidifier water panel and set humidistat to 45% per customers previous setting. Filter was replaced by customer prior to visit. Cleaned inside furnace housing and inspected all electrical connections. Furnace is running within manufacturers specifications. During zone board test I noticed upstairs motor grinding when returning to rest position. Informed the customer and emailed an estimate. Also recommended having ducts cleaned due to the amount of drywall dust in furnace cabinet. An estimate was sent for this as well.
Whole house plumbing inspection Incoming pressure is 75 psi Customer has no pressure regulator valve or thermal expansion tank Notified customer to keep an eye on single lever boiler drain for both hot and cold of washer unit for cross connections. Recommended repairs Water heater replacement based off of age House trap removal Switch rubber supply lines for braided lines Outside hydrant low pressure Went over options with customer And customer does not wish to have the estimate at the time.
Furnace tune up- checked CO/Gas leaks, found none. Vacuumed inside of furnace cabinet. Cleaned flame sensor. Checked filter, filter is good at this time. All heating ops are normal at this time.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, found that humidifier drain hose was leaking at this time and customer declined humidifier tune up. I also found that gas line running to fire place was made of copper and not up to code. Recommended having replaced but customer declined at this time. everything else tested as it should at this time, thanks for choosing Lba, Eli
Picked up parts from winnelson for installation of 6 gallon electric point of use hot water heater. Company returned on September 23rd of 2020 to conduct quoted work from pat. Company installed 6 gallon 120 volt water heater underneath menâ€™s restroom lavatory with hot side feeding menâ€™s lavatory and shooting through wall to tie into female lavatory. Company replaced three stops and ran all lines in copper. After turning water back on and tested everything for operation and everything is testing OK at this time. Tried calling owner and owner was unavailable Company still needs to collect for Job itself.
Estimate for water heater in hallway bathrooms. Found and turned on water heater in basement bathrooms
Performed planed maintenance as contract states. All systems are running at factory specifications at time of departure.
Upon arrival lobby area was at 81 degrees,checked unit out on roof,clean the condenser and add 2.5 pound of 410 to both units,unit will need time to recover, also people was coming in and out the doors making it hard for the unit to recover
Today I completed your annual cooling tune up. I tested all indoor operations. Tested temperature split and checked filter. I tested all outdoor operations. Checked refrigerant and cleaned outdoor system. Everything tested as it should at this time. Thanks for having me out today, Eli
Upon arrival the customer informed me that their Mitsubishi mini split system was dirty and also looked like it was dripping water down around the blower wheel. After speaking with the customer about cleaning options the customer wanted to just have a standard maintenance performed today. While I was disassembling the indoor unit I discovered microbial growth was present on and around the blower wheel. I spoke with the customer again and they then decided to have the blower wheel cleaning performed. I removed the drain pan and blower wheel and cleaned both, I cleaned both washable filters as well. After completing the cleaning I found the mini split system to be operating within the manufacturers tolerances at this time. I also spoke with the customer about the addition of an iWave M air purifier and I have included an estimate for that as well. Thank you
Whole house plumbing inspection Customer has six year old electric water heater with PRV and expansion tank that are both operational and testing at 60 PSI. Recommend repair is small drain repair and stop replacement on lavatory sink in hallway bathroom. Went over options with customer for drain repair and customer wants to go ahead and wanted to proceed with bronze level drain repair on vanity bathroom sink in hallway. Company replaced both emergency stops, pop up assembly, and p trap after turning water back on everything is staying dry and working properly at this time. Informed customer that company couldnâ€™t hook pop up assembly completely due to the fact customers original cable pop up assembly would not come off original faucet. Recommended to customer to replace original faucet In near future. Customer will have bronze six month warranty on companyâ€™s installation itself thank you for choosing lba and have a wonderful day!
Performed planed maintenance as contract states. All systems are running at factory specifications at time of departure. Condenser coils where very dirty I recommend the customer have LBA come out to this location 4 times a year instead of 2 for planed maintenance. Someone from the office will need to contact the customer to discuss this in further detail. Nothing further at this time.
Perform maintenance inspection on a Lennox air conditioner. Checked all the electrical components and refrigerant for proper pressures and temperatures. Upon checking the AC discover that the unit was really dirty and also the air filter was dirty. Recommended replacing the air filter and to perform a extensive coil cleaning on the outdoor unit. Customer declined both recommendations at this time. Everything else seems to be cooling under manufacture specification.
Upon arrival found supply blower wheel on unit 2 on passenger side of tunnel to be broken off of shaft. Penn ventilation is no longer a company as they are now Penn Barry out of Texas. Penn Barry distributor is Mechanical sales out of Lenexa. Spoke to managers C.J and Cameron and they have asked for quotes on replacement of unit and repair. I will be sending quote over when I receive parts quote from Mechanical sales. Sent quote to customer. Highly recommended replacement.
We replaced a broken thermostat located on the east wall, where construction had been done. We tested the unit in cooling mode, the system is cooling at this time. The breakers were off in the breaker panel when we got here.