Joshua did an excellent job assessing the HVAC uniys
Very professional and courteous
Jesse R. and the other LBA associates have always been very professional in their work and their customer interaction. I trust them implicitly.
Drew, the service technician from LBA arrived as scheduled, was very knowledgable and professional!
Our service professional was polite and very thorough
Arrived to installed new non-programable thermostat. Performed test to ensure thermostat was working properly. Unit is now operating a factory specifications at this time.
Arrive to find sand the fan running all the time. Switched up thermostat to see if the thermostat was bad. Perform safety testing to ensure that the system was operating properly. System is operating properly at this time.
Performed inspection of vacant suite 892 per Fred's request. I found that this suite has 3 units that serves this space. Discrepancies found notated below. Rtu-28 is a 5 ton carrier that is 25 years old. This unit was found disabled on heating and with a cracked heat exchanger. This unit was also found with a very low temperature split and appears to be low on charge. I will quote to diagnose and repair these issues and to also replace the unit due to its age and condition. Rtu-29 is a 5 ton Lennox that's 14 years old. It was found operating on heating and cooling was found non Operational due to a bad 10mfd capacitor for the condenser fan motor. If you spin the fan to help it get jump started the unit does run on cooling. Rtu-30 is a 3 ton carrier that is 16 years old. This unit was found shut down on heating with cracks in the heat exchanger so heating is non operational. Cooling was found operating properly with a good temperature split at this time. Due to supply houses closed t
I performed a maintenance and safety inspection I found the air conditioner over charged by 25%. I removed and recalibrated the the refrigerant and got the system operating within factory specifications.
No one home
Performed a full cooling inspection. Washed and cleaned outdoor unit. Tested all safety switches and wiring. Unit is operating within factory specifications. It is time to renew the membership. You can call the office to set up a payment for the membership. Also the outdoor unit has the old-style refrigerant which is R-22. January 1 of 2020 the EPA is completely phasing out.
Inspected twin Lennox units for no cooling. Customer reported the control was flashing a fan error code. The thermostat was found to be in the auto position not allowing for a cooling call. The unit is operating properly at this time. Customer has been instructed on the proper thermostat programs and functions.
This estimate will be to install a new water pressure regulator on the hot water side , with pressure gauges installed on both sides of regulator . Job is estimated to take about 2-3 hours to complete . This estimate was requested to be performed after normal business hours , this new cost will reflect our overtime charges to perform. Also if any unforeseen issues arise , and unsuspected parts are required , invoice will reflect those unsuspected charges .
Menâ€™s restroom toilet was leaking from the vacuum breaker when flushed , i removed old breaker and installed new vac breaker and spud coupling , tested flush all ok .
Leak search repaired frozen busted waterline
Lennox furnace not heating
Installed new shut off valve toilet
Fall furnace tuneup completed on a Lennox SL280 heating system.