Nate’s been to our home twice. He’s exceptional. Knows what he’s doing, is fair and honest, and gets the job done...even when it’s ridiculously difficult, like today’s job.
Austin did an outstanding job!!! He went above and beyond!
Was afraid we were looking at a sizeable
Mike Shelor our LBA Technician is awesome. He has Great knowledge and very professional.
Really can't say enough good things about Austin, the plumbing tech. who helped us today: Knowledgeable, patient, thorough! He made short work of what was a miserable issue for us, and was so professional and kind. Thanks LBA for always sending quality people, we count on you for that.
Performed furnace maintenance. Replaced merv 13 filter. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Performed a humidifier tuneup. System is heating and operational at this time.
Called for estimate on water heater. Water heater is original and should be replaced but is working. Problem with hot water is master tub and shower valve. Needs rebuilt. Talked to landlord and gave estimate
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I checked your air filter and cleaned flame safety system. Customer informed me he had been having intermitent issues with system but was unable to see any issues at this time. Everything tested as it should at this time
Upon arrival customer spoke with to me about the unit would sometimes not start up normally. Seemed like it would run for a short amount of time then shut off. Upon inspection system was operating correctly, no errors occurred during the inspection. Cycled the system a few times and system operated correctly. Customer still has a prepaid tune up (heating) owed. Customer will wait for his tune up for further diagnosis. Customer did renew his P3 contract on todays visit however customer has not yet had his furnace tune up or plumbing inspection, these are still owed to the customer.
Ran camera in sewer in sewer from basement. Sewer line goes out high on wall to back. Clean out has been removed to add main level drain line without adding a clean out outside. There is no way to inspect or properly clean line with out an access. The clean out in basement is only access. This drain line in basement is clear to where basement line and main level line tie together. There is roots coming out of main level line at this tie in. A proper clean out outside on main level line must be installed. There is no guarantee on sewer, proper clean outs are not available.
Upon arrival main line would backup into floor drain in basement/garage. There is no accessible cleanout. Attempted to unstop through floor drain, but was only partially successful. Disconnected washer drain dropping into 3â€ toilet flange so that large auger could be ran. Pulled out an excessive amount of roots and finally opened the line. Hit obstruction at 45â€™ and a major obstruction between 65&75â€™. Line is open but repair of line is necessary to insure home can drain properly. Camera service will be scheduled.
Estimate for tankless and tank type water heater
Performed furnace maintenance. Replaced customer supplied merv 16 filter. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Spoke to customer options about replacing older water heater. Is interested in replacing with tankless water heater. Will schedule for a plumbing specialist to come out here and take a look at the system.
Performed heating tuneup on furnace. Inspected heat exchanger did not see any cracks present but did find lots of construction dust on the heat exchanger. I told customer about this issue and that in order to clean it we will have to proceed with a deep clean of the furnace, he did not want to proceed with that at this time. Voltage enhancement system is running below manufactures specifications I did recommend replacement of this component and also ignition system for the furnace reading max resistance allowed by manufacturer. Customer did not want to address these issues today. Performed combustion check on heat exchanger. Checked temperature rise no other work performed. Customer signed up for P3 membership
Customer never got called back on pricing and does not want service.
Performed PM tasking on makeup air units and units heaters, change the filters , inspection belts checked operation of heating mode mode
Performed inspections on systems. Found Reznor unit with issues and quote submitted in January of 2020. Found another Reznor with bad belt but approved on site and repaired. Performed checks on other units and changed filters and updated filter list.
Removed old belt and install new belt. Approved on site by Cameron completed and verified operation. Unit is functioning correctly.
Upon arrival the customer tried to pull the toilet in the downstairs basement out and in doing so he took the old rusted flange out and couldnâ€™t install the new flange. I had to drill into the concrete to get the ne flange to sit properly. Customer only wanted the flange to be fix and wanted to install the toilet himself.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli