Izzy was very knowledgeable. Friendly and professional. Would recommend to a friend.
Aaron was professional and friendly. One you can trust to make a genuine recommendation for your home and HVAC system. Thank you LBA.
Felt very comfortable with visit. Welcome rusty back to work on our unit again. Knowledgeable and professional.
Excellent service via knowledgable professional
I thought the service we had was wonderful. The LBA employee was very professional and did a wonderful job. It was one of my best visits from a heating and air visit.
Installed Ruud 80% Furnace
Performed heating tuneup on furnace. Inspected all electrical components and electrical wires. Inspected air filter. Performed combustion check on heat exchanger. Inspected heat exchanger and is in good shape. System is running within manufacturers specs at this time
At time of arrival found furnace metal four pipe broken off, and also found hole in the heat exchanger and showed customer my concerns. After showing customer my options for repair, he decided itâ€™s best to schedule a comfort advisor to give an estimate to replace the furnace and flue pipe to get a better warranty together. I did shut down the furnace and tagged out for hazardous condition. Comfort advisor will come out today after noon. No other work performed at this time
Performed maintenance and safety inspection on the furnace. Inspected all electrical connections to ensure they are secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. Customer service the humidifier there selves. I showed him where to turn the water on which is above the water heater on the hot water line. I made sure humidifier was draining properly. There was a little bit of drywall dust in the blower compartment. I cleaned out as much as possible and recommended having their ducts clean since this house is a new build. Furnace is running safely and within manufacturers specifications at this time. Customer did bring up a small issue they are having with their mechanical room drain. Says there is a smell that comes and goes every so often. This drain accommodates the AC, furnace, and humidifier condensation. Asked the customer to keep an eye on it and note when it happens along with what the circumstances were when it happ
Checked all operations in the heating mode. Performed combustion analysis on the furnace. Performed a humidifier tuneup. Furnace filter was OK at this time. Cleaned out housing of furnace and humidifier. Furnace is heating properly and humidifier is humidifying properly.
Checked all operations and found that the system had major restriction issues due to the failures and problems customers going to look into replacement.
Customer stated that the a/c outside would kick on than kick off for certain time. After further diagnostic discovered that the a/c was tripping on the plenum discharge sensor when zone 2 was the only zone calling for cool. The only to correct and keep the discharge sensor from tripping is to open up the barometric damper to lower air pressure and cool properly. A/C is currently operating under manufacture specifications.
Upon arrival customer stated the neither the furnace or a/c would kick on. After further diagnostic discovered that the fuse was blown. Replaced fuse and I still wasnâ€™t receiving any control voltage. Than discovered that the voltage conversion transformer had failed. Replaced transformer to test where the low voltage short was coming from. Discovered that the inline fuse that was protecting the transformer is bypassed internally in the circuit board and not protecting the transformer. After further investigation discover that the outdoor voltage distributor is whatâ€™s causing the short. Informed the customer that to get system properly fixed we would have to replace the outdoor voltage distributor, the voltage conversion transformer, and the electronic control board. The customer approved to only get the voltage conversion transformer to at least have heat running. I did inform him in order to prevent shorting out another transformer I would have to disconnect the control wires that
09/03/2020 2:40:22 PM - Option 3 <a clicktracking="off" href="https://partsgatorstorage.blob.core.windows.net/proposals/932020 82520 PM - 1 - 13-28-Patrick Bunch -Proposalcopy.pdf?sv=2014-02-14&sr=b&sig=Mf6%2BMhqeR3X%2FKPhIty8GoCzxSm7zYYAw4Uw7csKnPZo%3D&st=2020-09-04T14%3A26%3A17Z&se=2520-09-04T14%3A31%3A17Z&sp=rw" target="_blank">View PDF</a>
Estimate for gas line to stove. Proper sizing requires a 3/4â€ line
Installed new fan blade to complete the work previously formed system is clean and operation within factory specifications.
Upon arrival found that the outdoor exhaust removal system and the Voltage enhancement system has failed. After speaking with the customer customer chose gold option allowing me to rebuild the outdoor electrical control panel, replace the exhaust removal system, and return at a later date after ordering parts to perform extensive cleaning as well as to replace the outdoor exhaust removal fan blades. System was slightly low on refrigerant due to customer being a good customer and choosing a top option I went ahead and recharged the outdoor unit back to factory specifications. (Adding the refrigerant is not included in the 18 month warranty) everything else done it covered. System is cooling properly at this time.
Checked all operators in the cooling mode. Replaced furnace filter that was very dirty. Checked all electrical and refrigerant components outdoors and found the system. To be low on refrigerant. Upon customers request I added refrigerant and internal leak sealer to the system. System is now cooling within factory specifications.
Installed two heads mitsubishi mini split
Apon arrival I found that the refridgerant in your system was overcharged, I gave estimate to have refridgerant removed and customer excepted, after removing refridgerant system cooled as it should, before removing refridgerant the superheat was 1 degree and after I removed refridgerant it was 24 degrees as factory specifications recommend. Thanks for having me out today, Eli