Izzy was very knowledgeable. Friendly and professional. Would recommend to a friend.
Aaron was professional and friendly. One you can trust to make a genuine recommendation for your home and HVAC system. Thank you LBA.
Felt very comfortable with visit. Welcome rusty back to work on our unit again. Knowledgeable and professional.
Excellent service via knowledgable professional
I thought the service we had was wonderful. The LBA employee was very professional and did a wonderful job. It was one of my best visits from a heating and air visit.
Customer had a faulty safety switch. Customer chose the Band-Aid option. Completed the Band-Aid option and the furnace is now operating correctly, cycled about four times. System started out properly and working correctly
Upon arrival area code was high limit switch, after inspecting all high limit switches found a high limit at the blower motor to be cutting the furnace electrical circulation causing the furnace to not turn on. Took out blower motor examined the heat exchanger no cracks found Reset and system is working again waited 20 min System is still running High limit switch faulty. Customer declined to open store and wants to do everything tomorrow.
Completed furnace tuneup. Performed an electrical test, High voltage wiring running to furnace is stable and secure normal 120 volts. Low-voltage wiring secure and stable. Making the right call from thermostat to board. Performed a combustion check, combustion motor is running and amping normally. Blower motor is running, amperage is on blower motor are up-and-down potentially losing power increasing power losing power would recommend replacing blower motor but system is running. Completed a safety inspection on the furnace, all safety switches are working to manufacture specification. Cleaned all safety switches and recalibrated. This system is heating properly. Lennox store is closed today. Will get back to you Monday.
Left customer a quote upon removing and reinstalling air conditioner will Credit the $59 trip charge if customer makes decisions to go with work.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed humidifier tune up, performed combustion analysis, checked for proper heating transfer, changed humidifier panel, everything tested as it should at this time, thanks for choosing Lba, Eli
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Arrived to find a fault in the voltage enhancement system. Showed customer options. Customer chose bandaid option. Performed all work under the bandaid options also performed safety testing to ensure system is working properly. Unit is cooling at this time. Customer also wanted to look into replacement. Office will call in the morning 7/29/19 to set up an opponent with our design specialist.
The customer stated that the system would not keep up with the cooling demand over the weekend when it reached near 100Â° outside. After testing the system in cooling mode, the only issue I found was that the outdoor coil was clogged with cotton and dirt. I conducted a performance and safety inspection for the air-conditioner. After washing the outdoor coil, the system is now operating properly and within factory specifications. I emailed the customer a quote to install zoning so they could better control the temperatures on the second level and the main level.
Completed cooling tune up
Completed annual cooling tune up, everything tested as it should at this time
Customer having problems when urinal is flushed loud pressure noises are present , took apart urinal valve found lead,solder partials inside cleaned out put valve together still having noises. Had the city come out and check water pressure to building, will need to install pressure regulator to help with pressure as 1st step to solving noise issues.
Completed cooling tune up, recommended having Coil chemical cleaned customer declined at this time, everything else tested as should. Thanks for having me out today, Eli
York furnace repairs