Izzy was very knowledgeable. Friendly and professional. Would recommend to a friend.
Aaron was professional and friendly. One you can trust to make a genuine recommendation for your home and HVAC system. Thank you LBA.
Felt very comfortable with visit. Welcome rusty back to work on our unit again. Knowledgeable and professional.
Excellent service via knowledgable professional
I thought the service we had was wonderful. The LBA employee was very professional and did a wonderful job. It was one of my best visits from a heating and air visit.
Apon arrival I found that the refridgerant in your system was overcharged, I gave estimate to have refridgerant removed and customer excepted, after removing refridgerant system cooled as it should, before removing refridgerant the superheat was 1 degree and after I removed refridgerant it was 24 degrees as factory specifications recommend. Thanks for having me out today, Eli
Preformed a whole home plumbing inspection and gave them a quoted them on a new 50 gallon gas water heater. The old 40 gallon gas water heater is 8 years old and doesnâ€™t have a expansion tank. There water pressure is at 80 psi but informed the customer that a pressure regulator would only help if the city decided to turn the water pressure up. Last I quoted the customer on a new outside faucet on the front of the house. Also quoted them a yearly p3
I performed a safety and maintenance inspection on the cooling system. The work I performed included, changing air filter, cleaning the condensate drain, checking temperature split, checking amp readings, and cleaning the outdoor coil. After my inspection I found that the system is operating within factory specifications at this time. Thank you
Found that thermostat had failed. Gave customer options to replace. He decided to sign up on maintenance agreement and have us come back out to install thermostat after he bought his own. Thanks for having me out today, Eli
, I tested all safety operation, checked refrigerant, checked all electrical operation and everything tested as it should. Performed chemical coil wash Turned off humidifier. Thanks for having me out today
Customer had a faulty safety switch. Customer chose the Band-Aid option. Completed the Band-Aid option and the furnace is now operating correctly, cycled about four times. System started out properly and working correctly
Upon arrival area code was high limit switch, after inspecting all high limit switches found a high limit at the blower motor to be cutting the furnace electrical circulation causing the furnace to not turn on. Took out blower motor examined the heat exchanger no cracks found Reset and system is working again waited 20 min System is still running High limit switch faulty. Customer declined to open store and wants to do everything tomorrow.
Completed furnace tuneup. Performed an electrical test, High voltage wiring running to furnace is stable and secure normal 120 volts. Low-voltage wiring secure and stable. Making the right call from thermostat to board. Performed a combustion check, combustion motor is running and amping normally. Blower motor is running, amperage is on blower motor are up-and-down potentially losing power increasing power losing power would recommend replacing blower motor but system is running. Completed a safety inspection on the furnace, all safety switches are working to manufacture specification. Cleaned all safety switches and recalibrated. This system is heating properly. Lennox store is closed today. Will get back to you Monday.
Left customer a quote upon removing and reinstalling air conditioner will Credit the $59 trip charge if customer makes decisions to go with work.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed humidifier tune up, performed combustion analysis, checked for proper heating transfer, changed humidifier panel, everything tested as it should at this time, thanks for choosing Lba, Eli
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Arrived to find a fault in the voltage enhancement system. Showed customer options. Customer chose bandaid option. Performed all work under the bandaid options also performed safety testing to ensure system is working properly. Unit is cooling at this time. Customer also wanted to look into replacement. Office will call in the morning 7/29/19 to set up an opponent with our design specialist.
The customer stated that the system would not keep up with the cooling demand over the weekend when it reached near 100Â° outside. After testing the system in cooling mode, the only issue I found was that the outdoor coil was clogged with cotton and dirt. I conducted a performance and safety inspection for the air-conditioner. After washing the outdoor coil, the system is now operating properly and within factory specifications. I emailed the customer a quote to install zoning so they could better control the temperatures on the second level and the main level.
Completed cooling tune up