Absolutely outstanding service from Justin. Knowledgeable and courteous. First rate.
Upon arrival house was getting low pressure. Checked in coming and outgoing pressures. Verified that pressure regulating valve was not properly regulating pressure. Replaced prv and installed a cut off.
Install a OEM compressor sound blanket to reduce the harmonic sound that the Scroll compressor naturally makes.
I arrived to find that the motorized damper for zone 2 is really noisy. I replaced the motorized damper and tested zoning operations. Zoning system is now operating properly at this time. The customer also stated that the outdoor unit has a loud rhythmic sound to it. The customer would like a compressor sound blanket installed to quite the system. I explained to the customer that once the compressor sound blanket arrives we will call him to schedule time for me to come out and install it.
Not a recall, cabled laundry line from pulled trap under vanity. Line is open and flowing at this time.
Main line special : cabled approximately 25â€™ of main line backwards from outside c/o, line is open at this time.
Ice maker leak
Mainline clogged with roots had to auger drain line
Expansion tank was leaking at the connection also copper supply line was leaking at the Tee. Had to replace both sections and the expansion tank.
Augured toilet stack had to pull and reset toilet due to paper towels in drain line
Install customer supply water softener
Replace both showers stems on the hot and cold side also replace shower head.
Full furnace and humidifier tune up.